- 1 Purpose
- 2 The process
- 3 Activated sludge control
- 4 History
- 5 Types of plants
- 6 Aeration methods
- 7 See also
- 8 References
- 9 External links
In a sewage (or industrial wastewater) treatment plant, the activated sludge process is a biological process that can be used for one or several of the following purposes:
- oxidizing carbonaceous biological matter.
- oxidizing nitrogenous matter: mainly ammonium and nitrogen in biological matter.
- removing phosphates.
- driving off entrained gases such as carbon dioxide, ammonia, nitrogen, etc.
- generating a biological floc that is easy to settle.
- generating a liquor that is low in dissolved or suspended material.
The process involves air or oxygen being introduced into a mixture of screened, and primary treated sewage or industrial wastewater (wastewater) combined with organisms to develop a biological floc which reduces the organic content of the sewage. This material, which in healthy sludge is a brown floc, is largely composed of saprotrophic bacteria but also has an important protozoan flora mainly composed of amoebae, Spirotrichs, Peritrichs including Vorticellids and a range of other filter feeding species. Other important constituents include motile and sedentary Rotifers. In poorly managed activated sludge, a range of mucilaginous filamentous bacteria can develop including Sphaerotilus natans which produces a sludge that is difficult to settle and can result in the sludge blanket decanting over the weirs in the settlement tank to severely contaminate the final effluent quality. This material is often described as sewage fungus but true fungal communities are relatively uncommon.
The combination of wastewater and biological mass is commonly known as mixed liquor. In all activated sludge plants, once the wastewater has received sufficient treatment, excess mixed liquor is discharged into settling tanks and the treated supernatant is run off to undergo further treatment before discharge. Part of the settled material, the sludge, is returned to the head of the aeration system to re-seed the new wastewater entering the tank. This fraction of the floc is called return activated sludge (R.A.S.). Excess sludge is called surplus activated sludge (S.A.S.) or waste activated sludge (W.A.S). W.A.S is removed from the treatment process to keep the ratio of biomass to food supplied in the wastewater in balance, and is further treated by digestion, either under anaerobic or aerobic conditions prior to disposal.
The space required for a sewage treatment plant can be reduced by using a membrane bioreactor to remove some wastewater from the mixed liquor prior to treatment. This results in a more concentrated waste product that can then be treated using the activated sludge process.
Many sewage treatment plants use axial flow pumps to transfer nitrified mixed liquor from the aeration zone to the anoxic zone for denitrification. These pumps are often referred to as internal mixed liquor recycle pumps (IMLR pumps). The raw sewage, the RAS, and the nitrified mixed liquor are mixed by submersible mixers in the anoxic zones in order to achieve denitrification.
Activated sludge is also the name given to the active biological material produced by activated sludge plants.
Activated sludge control
The general method to do this is to monitor sludge blanket level, SVI (Sludge Volume Index), MCRT (Mean Cell Residence Time), F/M (Food to Microorganism), as well as the biota of the activated sludge and the major nutrients DO (Dissolved oxygen), nitrogen, phosphate, BOD (Biochemical oxygen demand), and COD (Chemical oxygen demand).
In the reactor/aerator + clarifier system:
- The sludge blanket is measured from the bottom of the clarifier to the level of settled solids in the clarifier's water column; this, in large plants, can be done up to three times a day.
- The SVI is the volume of settled sludge in milliliters occupied by 1 gram of dry sludge solids after 30 minutes of settling in a 1000 milliliter graduated cylinder.
- The MCRT is the total mass (lbs) of mixed liquor suspended solids in the aerator and clarifier divided by the mass flow rate (lbs/day) of mixed liquor suspended solids leaving as WAS and final effluent.
- The F/M is the ratio of food fed to the microorganisms each day to the mass of microorganisms held under aeration. Specifically, it is the amount of BOD fed to the aerator (lbs/day) divided by the amount (lbs) of Mixed Liquor Volatile Suspended Solids (MLVSS) under aeration. Note: Some references use MLSS (Mixed Liquor Suspended Solids) for expedience, but MLVSS is considered more accurate for the measure of microorganisms. Again, due to expedience, COD is generally used, in lieu of BOD, as BOD takes five days for results.
Based on these control methods, the amount of settled solids in the mixed liquor can be varied by wasting activated sludge (WAS) or returning activated sludge (RAS).
The activated sludge process was discovered in 1913 in the United Kingdom by two engineers, Edward Ardern and W.T. Lockett, who were conducting research for the Manchester Corporation Rivers Department at Davyhulme Sewage Works. This development led to arguably the single most significant improvement in public health and the environment during the course of the century.
In 1912, Dr. Gilbert Fowler, a scientist at the University of Manchester, observed experiments being conducted at the Lawrence Experiment Station at Massachusetts involving the aeration of sewage in a bottle that had been coated with algae. Fowler's engineering colleagues, Ardern and Lockett, experimented on treating sewage in a draw-and-fill reactor, which produced a highly treated effluent. They aerated the waste-water continuously for about a month and were able to achieve a complete nitrification of the sample material. Believing that the sludge had been activated (in a similar manner to activated carbon) the process was named activated sludge. Not until much later was it realized that what had actually occurred was a means to concentrate biological organisms, decoupling the liquid retention time (ideally, low, for a compact treatment system) from the solids retention time (ideally, fairly high, for an effluent low in BOD5 and ammonia.)
Their results were published in their seminal 1914 paper, and the first full-scale continuous-flow system was installed at Worcester two years later. In the aftermath of the First World War the new treatment method spread rapidly, especially to the USA, Denmark, Germany and Canada. By the late 1930s, the activated sludge treatment was the predominant process used around the world.
The general arrangement of an activated sludge process for removing carbonaceous pollution includes the following items:
- Aeration tank where air (or oxygen) is injected in the mixed liquor.
- Settling tank (usually referred to as "final clarifier" or "secondary settling tank") to allow the biological flocs (the sludge blanket) to settle, thus separating the biological sludge from the clear treated water.
Treatment of nitrogenous matter or phosphate involves additional steps where the mixed liquor is left in anoxic condition (meaning that there is no residual dissolved oxygen).
Types of plants
There are a variety of types of activated sludge plants. These include:
There are a wide range of types of package plants, often serving small communities or industrial plants that may use hybrid treatment processes often involving the use of aerobic sludge to treat the incoming sewage. In such plants the primary settlement stage of treatment may be omitted. In these plants, a biotic floc is created which provides the required substrate. Package plants are designed and fabricated by specialty engineering firms in dimensions that allow for their transportation to the job site in public highways, typically width and height of 12 by 12 feet. Length varies with capacity with larger plants being fabricated in pieces and welded on site. Steel is preferred over synthetic materials (e.g., plastic) for its durability.
Package plants are commonly variants of extended aeration, to promote the 'fit & forget' approach required for small communities without dedicated operational staff. There are various standards to assist with their design.
In some areas, where more land is available, sewage is treated in large round or oval ditches with one or more horizontal aerators typically called brush or disc aerators which drive the mixed liquor around the ditch and provide aeration. These are oxidation ditches, often referred to by manufacturer's trade names such as Pasveer, Orbal, or Carrousel. They have the advantage that they are relatively easy to maintain and are resilient to shock loads that often occur in smaller communities (i.e. at breakfast time and in the evening).
Oxidation ditches are installed commonly as 'fit & forget' technology, with typical design parameters of a hydraulic retention time of 24 – 48 hours, and a sludge age of 12 – 20 days. This compares with nitrifying activated sludge plants having a retention time of 8 hours, and a sludge age of 8 – 12 days.
Where land is in short supply sewage may be treated by injection of oxygen into a pressured return sludge stream which is injected into the base of a deep columnar tank buried in the ground. Such shafts may be up to 100 metres deep and are filled with sewage liquor. As the sewage rises the oxygen forced into solution by the pressure at the base of the shaft breaks out as molecular oxygen providing a highly efficient source of oxygen for the activated sludge biota. The rising oxygen and injected return sludge provide the physical mechanism for mixing of the sewage and sludge. Mixed sludge and sewage is decanted at the surface and separated into supernatant and sludge components. The efficiency of deep shaft treatment can be high.
Surface aerators are commonly quoted as having an aeration efficiency of 0.5 - 1.5 kg O2/kWh, diffused aeration as 1.5 - 2.5 kg O2/KWh. Deep Shaft claims 5 – 8 kg O2/kWh.
However, the costs of construction are high. Deep Shaft has seen the greatest uptake in Japan, because of the land area issues. Deep Shaft was developed by ICI, as a spin-off from their Pruteen process. In the UK it is found at three sites: Tilbury, Anglian water, treating a wastewater with a high industrial contribution; Southport, United Utilities, because of land space issues; and Billingham, ICI, again treating industrial effluent, and built (after the Tilbury shafts) by ICI to help the agent sell more.
DeepShaft is a patented, licensed, process. The licensee has changed several times and, currently (2007), it is Aker Kvaerner Engineering Services.
Most biological oxidation processes for treating industrial wastewaters have in common the use of oxygen (or air) and microbial action. Surface-aerated basins achieve 80 to 90% removal of BOD with retention times of 1 to 10 days. The basins may range in depth from 1.5 to 5.0 metres and utilize motor-driven aerators floating on the surface of the wastewater.
In an aerated basin system, the aerators provide two functions: they transfer air into the basins required by the biological oxidation reactions, and they provide the mixing required for dispersing the air and for contacting the reactants (that is, oxygen, wastewater and microbes). Typically, the floating surface aerators are rated to deliver the amount of air equivalent to 1.8 to 2.7 kg O2/kWh. However, they do not provide as good mixing as is normally achieved in activated sludge systems and therefore aerated basins do not achieve the same performance level as activated sludge units.
Biological oxidation processes are sensitive to temperature and, between 0 °C and 40 °C, the rate of biological reactions increase with temperature. Most surface aerated vessels operate at between 4 °C and 32 °C.
Sewage liquor is run into deep tanks with diffuser grid aeration systems that are attached to the floor. These are like the diffused airstone used in tropical fish tanks but on a much larger scale. Air is pumped through the blocks and the curtain of bubbles formed both oxygenates the liquor and also provides the necessary mixing action. Where capacity is limited or the sewage is unusually strong or difficult to treat, oxygen may be used instead of air. Typically, the air is generated by some type of blower or compressor.
Surface aerators (cones)
Vertically mounted tubes of up to 1 metre diameter extending from just above the base of a deep concrete tank to just below the surface of the sewage liquor. A typical shaft might be 10 metres high. At the surface end the tube is formed into a cone with helical vanes attached to the inner surface. When the tube is rotated, the vanes spin liquor up and out of the cones drawing new sewage liquor from the base of the tank. In many works each cone is located in a separate cell that can be isolated from the remaining cells if required for maintenance. Some works may have two cones to a cell and some large works may have 4 cones per cell.
Pure oxygen aeration
Pure oxygen activated sludge aeration systems are sealed-tank reactor vessels with surface aerator type impellers mounted within the tanks at the oxygen atmosphere-mixed liquor surface interface. The amount of oxygen entrainment, or DO (Dissolved Oxygen), can be controlled by a weir adjusted level control, and a vent gas oxygen controlled oxygen feed valve. Oxygen is generated on site by cryogenic distillation of air, pressure swing adsorption, or other methods. These systems are used where wastewater plant space is at a premium and high sewage throughput is required as high energy costs are involved in purifying oxygen.
- Activated sludge model
- Aerated lagoon
- Aerobic granular reactor
- Industrial wastewater treatment
- List of waste water treatment technologies
- Rotating biological contactor
- Sewage treatment
- Sludge bulking
- Trickling filter
- Aerobic granulation
- Daniel Ishag HYBACS®
- Operation and Control From the Water/ Wastewater Distance Learning Website of the Mountain Empire Community College in Virginia.
- Mathematics For Wastewater Operators
- Eckenfelder, Jr., W. Wesley; Cleary, Joseph G. (2014). Activated Sludge Technologies for Treating Industrial Wastewaters (1st ed.). DEStech Publications. p. 234. ISBN 978-1-60595-019-8. Retrieved 29 December 2014.
- Beychok, Milton R. (1967). Aqueous Wastes from Petroleum and Petrochemical Plants (1st ed.). John Wiley & Sons Ltd. LCCN 67019834.
- Benidickson, Jamie (2011). The Culture of Flushing: A Social and Legal History of Sewage. UBC Press. Retrieved 2013-02-07.
- Code of Practice, Flows and Loads-2, British Water
- Review of UK and international standards
- British Standard BS 6297:1983
- Tilbury construction
- Deep Shaft Process Technology
- Beychok, M.R. (1971). "Performance of surface-aerated basins". Chemical Engineering Progress Symposium Series 67 (107): 322–339. Available at CSA Illumina website
-  Modelling activated sludge wastewater treatment plants using artificial intelligence techniques
- Modelling using ASM1
- Steady-state activated sludge model
- Various PhD theses on modelling activated sludge systems
- Detailed algorithms for ASM1 and Takacs settling tank model
- Metabolic activated sludge model
- Aerated, Partial Mix Lagoons (Wastewater Technology Fact Sheet by the U.S. Environmental Protection Agency)
- Aerated Lagoon Technology (Linvil G. Rich, Professor Emeritus, Department of Environmental Engineering and Science, Clemson University)
- Modeling activated sludge (Y. Heymann, 2010)
- Why surface aeration? Comparison between surface aerators or low-speed turbines and fine bubble bottom aeration.