A flame detector is a sensor designed to detect and respond to the presence of a flame or fire. Responses to a detected flame depend on the installation, but can include sounding an alarm, deactivating a fuel line (such as a propane or a natural gas line), and activating a fire suppression system. When used in applications such as industrial furnaces, their role is to provide confirmation that the furnace is properly lit; in these cases they take no direct action beyond notifying the operator or control system. A flame detector can often respond faster and more accurately than a smoke or heat detector due to the mechanisms it uses to detect the flame.
- 1 Optical flame detectors
- 2 Other types
- 3 Applications
- 4 See also
- 5 Noted Manufacturers
- 6 References
Optical flame detectors
Ultraviolet (UV) detectors work by detecting the UV radiation emitted at the instant of ignition. While capable of detecting fires and explosions within 3–4 milliseconds, a time delay of 2–3 seconds is often included to minimize false alarms which can be triggered by other UV sources such as lightning, arc welding, radiation, and sunlight. UV detectors typically operate with wavelengths shorter than 300 nm.
Near IR array
Infrared (IR) flame detectors monitor the infrared spectral band for specific patterns given off by hot gases. These are sensed using a specialized fire-fighting thermal imaging camera (TIC), a type of thermographic camera. False alarms can be caused by other hot surfaces and background thermal radiation in the area. Water on the detector's lens will greatly reduce the accuracy of the detector, as will exposure to direct sunlight. A single-frequency IR flame detector is typically sensitive to wavelengths around 4.4 micrometers, which is a spectral characteristic peak of hot carbon dioxide as is produced in a fire. The usual response time of an IR detector is 3–5 seconds.
These detectors are sensitive to both UV and IR wavelengths, and detect flame by comparing the threshold signal of both ranges. This helps minimize false alarms.
IR/IR flame detection
Dual IR (IR/IR) flame detectors compare the threshold signal in two infrared ranges. In this case one sensor looks at the 4.4 micrometer range, while the other sensor looks at a reference frequency.
IR3 flame detection
Triple-IR flame detectors compare three specific wavelength bands within the IR spectral region and their ratio to each other. In this case one sensor looks at the 4.4 micrometer range while the other sensors look at reference wavelengths both above and below 4.4. This allows the detector to distinguish between non-flame IR sources and actual flames which emit hot CO2 in the combustion process. As a result, both detection range and immunity to false alarms can be significantly increased. IR3 detectors can detect a 0.1m2 (1 ft2) gasoline pan fire at up to 65 m (215 ft) in less than 5 seconds. Triple IRs, like other IR detector types, are susceptible to blinding by a layer of water on the detector's window.
Most IR detectors are designed to ignore constant background IR radiation, which is present in all environments. Instead they are designed to detect suddenly changing or increasing sources of the radiation. When exposed to changing patterns of non-flame IR radiation, IR and UV/IR detectors become more prone to false alarms, while IR3 detectors become somewhat less sensitive but are more immune to false alarms.
In some detectors, a sensor for visible radiation (light) is added to the design in order to better discriminate against false alarms or to improve the detection range.
Closed-circuit television or a web camera can be used for visual detection of (wavelengths between 0.4 and 0.7 µm). Smoke or fog can limit the effective range of these, since they operate solely in the visible spectrum.
Ionization current flame detection
The intense ionization within the body of a flame can be measured by means of a current that flows when a voltage is applied. This current can be used to verify flame presence and quality. Such detectors are normally used in large industrial process gas heaters and are connected to the flame control system. They usually act as both flame quality monitors and for flame failure detection.
Thermocouple flame detection
Thermocouples are used extensively for monitoring flame presence in combustion heating systems and gas cookers. A common use in these installations is to cut off the supply of fuel if the flame fails, in order to prevent unburned fuel from accumulating.
UV/IR flame detectors are used in:
- Hydrogen stations.
- Gas-fueled cookers
- Industrial heating and drying systems
- Domestic heating systems
- Industrial gas turbines
- Flame detection
- Active fire protection
- Flame ionization detector
- Gas detector
- Fire alarm system
- Talentum Developments.
- ESP Safety Inc.
- Sierra Monitor Corp.
- ITS Industrial Turbine Services GmbH
- Spectrex, Inc.
- REZONTECH Co., Ltd.
- GE Reuter Stokes
- Barrie Jenkins, Peter Mullinger. 2011. Industrial and Process Furnaces: Principles, Design and Operation, Butterworth-Heinemann/IChemE series, p.329. Butterworth-Heinemann. ISBN 0080558062
- S. P. Bag. 1995. Fire Services in India: History, Detection, Protection, Management, Environment, Training and Loss Prevention, p. 49. Mittal Publications. ISBN 8170995981
- Töreyin, B. Ugur; Dedeoglu, Yigithan; Cetin, A. Enis (2005). "IEEE International Conference on Image Processing 2005". IEEE International Conference on Image Processing, 2005 (Piscataway, N.J.: Institute of Electrical and Electronics Engineers) 2: 1230–3. doi:10.1109/ICIP.2005.1530284. ISBN 0-7803-9134-9.
- Karner, Don; Francfort, James (December 2003). "Arizona Public Service—Alternative Fuel (Hydrogen) Pilot Plant Design Report". U.S. Department of Energy FreedomCAR & Vehicle Technologies Program. pp. Appendix F (pdf).