Hypoxic air technology for fire prevention
Hypoxic air technology for fire prevention, also known as oxygen reduction system, is an active fire protection technique based on a permanent reduction of the oxygen concentration in the protected rooms. Unlike traditional fire suppression systems that usually extinguish fire after it is detected, hypoxic air is able to prevent fire.
In a volume protected by hypoxic air, a normobaric hypoxic atmosphere is continuously retained: hypoxic means that the partial pressure of the oxygen is lower than at the sea level, normobaric means that the barometric pressure is equal to the barometric pressure at the sea level. Usually 5%/10% of oxygen contained in the air is replaced by the same amount of nitrogen: as a consequence a hypoxic atmosphere containing around 15 Vol% of oxygen and 85 Vol% of nitrogen is created. In a normobaric hypoxic environment, common materials cannot ignite or burn. Thus, considering the fire triangle, a fire cannot occur because of the lack of sufficient oxygen.
The phenomenon of fire prevention at higher oxygen concentration than the oxygen concentration required for extinguishing an established fire has been observed and exploited for decades. The technology was originally developed for athletic training in 1993 by Igor (Gary) Kotliar but its value for fire prevention was only patented in 1998. In 2001 Kotliar started FirePASS to market breathable hypoxic fire prevention systems.
Design and operation
Air with a reduced oxygen content is injected to the protected volumes to lower the oxygen concentration until the desired oxygen concentration is reached. Then, because of air infiltration, the oxygen concentration inside the protected volumes rises: when it exceeds a certain threshold, low-oxygen air is again injected to the protected volumes until the desired oxygen concentration is reached. Oxygen sensors are installed in the protected volumes to monitor continuously the oxygen concentration.
The exact oxygen level to retain in the protected volumes is determined after a careful and accurate assessment of materials, configurations and hazards. Tables listing ignition-limiting oxygen thresholds for some materials are available in the fire safety literature. Alternatively the ignition-limiting threshold is determined by performing a proper ignition test described in BSI PAS 95:2011 - Hypoxic air fire prevention systems specification.
Air with low oxygen concentration is produced by hypoxic air generators, also known as air splitting units. There are three different types of hypoxic air generators: membrane-based, PSA-based and VSA-based ones. VSA-based hypoxic air generators have usually a lower energy consumption compared to PSA-based and membrane-based ones. Hypoxic air generators can be located inside or outside the protected rooms. Hypoxic air systems can be integrated with the building management system and can include systems to recover the heat generated by the hypoxic air generator that, otherwise, would be wasted.
Air with low oxygen concentration is transported to the protected volumes through dedicated pipes or, more simply, via an existing ventilation system. In the latter case, dedicated pipes or ducts are not required.
Combined use of hypoxic air for fire prevention
Hypoxic air fire prevention systems can also be used for purposes other than fire prevention, for example:
- High altitude training
- Health[examples needed]
- Preserving artifacts and objects from degradation or oxidation
- Preserving food from deterioration, commonly known as modified atmosphere packaging.
Combining fire prevention, indoor climate and reduction of artefacts/food degradation is a completely new approach for a fire safety system.
The benefits of preventing a fire instead of suppressing it makes hypoxic air especially suitable for applications where a fire would cause unacceptable damage and traditional fire suppression is unacceptable or unusable. Unlike traditional fire-suppression systems, dedicated pipes or nozzles are not required. In situations where the installation of a traditional firefighting system would pose severe problems, fire protection can be provided with hypoxic air.
Hypoxic air for fire prevention suits best for:
- Data centers / ICT facilities
- Storage of high value items
- Freezer and cold storage
- Large warehouses
- Heritage applications
- Document Storage
The reduction of artifact degradation and food deterioration is a plus for applications like food warehouses, storage and archives.
The inherent simplicity of hypoxic air systems facilitates integration of sustainable building design and fire protection engineering.
Effects on health
Fire-prevention systems which result in the oxygen content being less than 19.5% are not permitted for occupied spaces by federal regulation (OSHA) in the United States .
However, hypoxic air is considered by some to be safe to breathe for most people. Medical studies have been undertaken on this topic. Angerer and Novak's conclusion is that "working environments with low oxygen concentrations to a minimum of 13% and normal barometric pressure do not impose a health hazard, provided that precautions are observed, comprising medical examinations and limitation of exposure time". Küpper et al. say that oxygen concentration between 17.0-14.8% does not cause any risk for healthy people by hypoxia. It also does not cause risks for people with chronic diseases of moderate severity.
Pressurized aircraft cabins are typically maintained at 75kPa, the pressure found at 2500 m altitude, resulting in an oxygen partial pressure of about 16 kPa, which is the same as a 15% oxygen concentration in a hypoxic-air application at sea-level pressure. However, passengers are sedentary and crew members have immediate access to supplemental oxygen.
Hypoxic air is to be considered clean air and not contaminated air when assessing oxygen depletion hazards.
Applicable standards and guidelines, system verification
- BSI PAS 95:2011 - Hypoxic air fire prevention systems. Specification
- VdS 3527en:2007 - Inerting and Oxygen Reduction Systems, Planning and Installation 
Inspection body accreditation criteria are established according to ISO/IEC 17010 for third party verification of hypoxic air fire prevention system conformance to BSI PAS 95:2011 and VdS 3527en:2007 
Hypoxic air technology for fire prevention and SAIPHS
SAIPHS  stands for “The Summit Air Institute for Preservation, Health and Safety”. SAIPHS is an institution dedicated for the advancement of and fostering education of hypoxic air technology.
Among the scopes of SAIPHS there are:
- Exchanging knowledge related to Hypoxic Air Technology and applications
- Educating about Hypoxic Air Technology and its applications
- Supporting promotion and development of best practices and standard as well as Development of safety guidelines
- Being an independent source of information related to Hypoxic Air Technology
- Hypoxic Air Venting for Protection of Heritage
- Test Methods for Hypoxic Air Fire Prevention Systems and Overall Environmental Impact of Applications
- Fire Protection Requirements for ICT rooms - Best Practice Document
-  Brooks, J. Aircraft Cargo Fire Suppression Using Low Pressure Dual Fluid Water Mist and Hypoxic Air. NIST SP 984-2; NIST Special Publication 984-2;
- FirePASS Corporation. "FirePASS > Company". Archived from the original on 2011-04-11. Retrieved 2013-08-12.
- Chiti, Stefano (November 9, 2011). "A Pilot Study on Hypoxic Air Performance at the Interface of Fire Prevention and Fire Suppression". FIRESEAT 2011: The Science of Suppression.
- "PAS 95:2011 Hypoxic air fire prevention systems. Specification". BSI.
- Chiti, Stefano; Jensen Geir; Fjerdingen Ola Thomas (March 2011). "Hypoxic Air Technology: Fire Protection Turns Preventive.". Proceedings of the International Workshop on Fire Safety and Management.
- , Short-term exposure to hypoxia for work and leisure activities in health and disease: which level of hypoxia is safe? Burtscher M, Mairer K, Wille M, Gatterer H, Ruedl G, Faulhaber M, Sumann G.
- Angerer, Peter; Nowak (March 2003). "Working in permanent hypoxia for fire protection-impact on health". International archives of occupational and environmental health 76 (2): 87–102. doi:10.1007/s00420-002-0394-5. PMID 12733081.
- Küpper, Thomas. "Work in Hypoxic Conditions". THE INTERNATIONAL MOUNTAINEERING AND CLIMBING FEDERATION.
- "VdS 3527en - Inerting and Oxygen Reduction Systems, Planning and Installation". VdS.
- "Certification of Hypoxic Air Fire Prevention Systems".