International standard IEC 60446 defines basic safety principles for identifying electrical conductors by colours or numerals, for example in electricity distribution wiring.
The standard permits the following colours for identifying conductors:
(The colours green and yellow on their own are only permitted where confusion with the colouring of the green/yellow protective conductor is unlikely. Combinations of the above colours are permitted, but green and yellow should not be used in any of these combinations other than as green/yellow for the protective conductor.)
Use of colours
Neutral or mid-point conductor
AC phase conductors
The colour combination green/yellow is always and exclusively used to identify the protective conductor. On any 15 mm length of the conductor, one of these two colours should cover between 30% and 70% of the area and the other the remaining area.
Insulated PEN conductors should be marked either green/yellow along their entire length with light blue markings at their ends, or light blue along their entire length with green/yellow markings at the ends.
United States, Canada and Japan
The three countries United States, Canada and Japan are mentioned in a note in the standard for using different colours:
- white or natural grey for mid-wire or neutral conductor (instead of light blue)
- green for the protective conductor (instead of green-and-yellow)
British Standard BS 7671:2001 Amendment No 2:2004 adopted the IEC 60446 colours for fixed wiring in the United Kingdom , with the extension that grey can also be used for line conductors, such that three colours are available for three-phase installations. This extension is expected to be adopted across Europe and may even find its way into a future revision of IEC 60446.
Where conductors are in addition identified by numbers, then these numbers must be written in Arabic numerals, digits 6 and 9 must be underlined, and green-and-yellow conductors must not be numbered.