Insulated glazing (IG), more commonly known as double glazing (or double-pane, and increasingly triple glazing/pane) are double or triple glass window panes separated by an air or other gas filled space to reduce heat transfer across a part of the building envelope.
Insulated Glass Units are manufactured with glass in range of thickness from 3 mm to 10 mm or more in special applications. Laminated or tempered glass may also be used as part of the construction. Most units are manufactured with the same thickness of glass used on both panes but special applications such as acoustic attenuation or security may require wide ranges of thicknesses to be incorporated in the same unit.
To reduce shear effects on the sealed unit (a major cause of premature failure), manufacturers use a rule of thumb that permits a difference of 1 mm between the thickness of the panes of glass used in the unit and still maintain the warranty for the unit. For example, a unit may be ordered with a 4 mm pane on the exterior and a 3 mm pane on the interior. These variations are allowed for architectural and cost reasons. Other combinations can be specified and produced but the manufacturer may reserve the right to limit the term of the warranty or refuse to warranty the unit altogether.
For ease of description the surfaces of a double paned unit are named according to the following convention: Surface #1 (facing outside), Surface #2 (inside of outside pane), Surface #3 (outside of inside pane) and Surface #4 (inside surface of inside pane). Applying the corresponding nomenclature for triple paned units results in surfaces #1 through #6.
The performance of insulating glazing can be modified through the use of the following:
The glass panes are separated by a "spacer". A spacer is the piece that separates the two panes of glass in an insulating glass system, and seals the gas space between them. Historically, spacers were made primarily of metal and fiber, which manufacturers thought provided more durability.
However, metal spacers conduct heat (unless the metal is thermally improved), undermining the ability of the IGU to reduce heat flow. It may also result in water or ice forming at the bottom of the sealed unit because of the sharp temperature difference between the window and surrounding air. To reduce heat transfer through the spacer and increase overall thermal performance, manufacturers may make the spacer out of a less-conductive material such as structural foam. A spacer made of aluminum that also contains a highly structural thermal barrier reduces condensation on the glass surface and improves insulation, as measured by the overall U-factor (see Thermal conductivity).
- A spacer that reduces heat flow in glazing configurations may also have characteristics for sound dampening in urban areas subjected to irritating noise levels, such as near subways, trucks and airports.
- Typically, spacers are filled with or contain desiccant to remove moisture trapped in the gas space during manufacturing, thereby lowering the dew point of the gas in that space, and preventing condensation from forming on surface #2 when the outside glass pane temperature falls.
- New technology has emerged to combat the heat loss from traditional spacer bars, including improvements to the structural performance and long-term-durability of improved metal (aluminum with a thermal barrier) and foam spacers.
IGUs are often manufactured on a made to order basis on factory production lines, standard units are also available. The width and height dimensions, the thickness of the glass panes and the type of glass for each pane as well as the overall thickness of the unit must be supplied to the manufacturer. On the assembly line, spacers of specific thicknesses are cut and assembled into the required overall width and height dimensions and filled with desiccant. On a parallel line, glass panes are cut to size and washed to be optically clear.
An adhesive sealant (polyisobutylene - PIB) is applied to the face of the spacer on each side and the panes pressed against the spacer. If the unit is gas filled, two holes are drilled into the spacer of the assembled unit, lines are attached to draw out the air out of the space and replacing it with the desired gas. The lines are then removed and holes sealed to contain the gas. The more modern technique is to use an online gas filler, which eliminates the need to drill holes in the spacer. The units are then sealed on the edge side using either polysulphide or silicone sealant or similar material to prevent humid outside air from entering the unit. The desiccant will remove traces of humidity from the air space so that no water appears on the inside faces (no condensation) of the glass panes facing the air space during cold weather. Some manufacturers have developed specific processes that combine the spacer and desiccant into a single step application system.
The double glazed window was invented in 1930s, and was commonly available in US in the 1950s under the ThermopaneTM brand name, registered in 1941 by Libbey-Owens-Ford Glass Company. After so many decades, the manufacturing process is well established, though innovation has continued to improved the R factor and other characteristics of windows. The brand name Thermopane has entered the vocabulary of the glazing industry as the genericized trademark for any IGU.
Materials which can be used for double glazing include aluminum, PVC, and wood (timber).
Thermal performance 
The maximum insulating efficiency of a standard IGU is determined by the thickness of the space containing the gas. Too little space between the panes of glass results in heat loss by diffusion between the panes (heat from one pane travelling through the fill gas the other pane) while if too large a gap is used, convection currents are not damped out by the gas viscosity and transfer heat between the panes. For further information, see the article heat flow. Typically, most sealed units achieve maximum insulating values using a gas space of 16–19 mm (0.63–0.75 in) when measured at the centre of the IGU. When combined with the thickness of the glass panes being used, this can result in an overall thickness of the IGU of 22–25 mm (0.87–0.98 in) for 3 mm (0.12 in) glass to 28–31 mm (1.1–1.2 in) for 6.35 mm (0.250 in) plate glass.
IGU thickness is a compromise between maximizing insulating value and the ability of the framing system used to carry the unit. Some residential and most commercial glazing systems can accommodate the ideal thickness of a double paned unit. Issues arise with the use of triple glazing to further reduce heat loss in an IGU. The combination of thickness and weight results in units that are too unwieldy for most residential or commercial glazing systems, particularly if these panes are contained in moving frames or sashes.
This trade-off does not apply to Vacuum Insulated Glass (VIG), or evacuated glazing, as heat loss due to convection is eliminated, leaving radiation losses and conduction through the edge seal. These VIG units have most of the air removed from the space between the panes, leaving a nearly-complete vacuum. VIG units which are currently on the market are hermetically sealed along their perimeter with solder glass, that is, a glass frit having a reduced melting point. Such a glass seal is rigid, and will experience increasing stress with increasing temperature differential across the unit. This stress may prevent Vacuuum glazing from being used when the temperature differential is too great. One manufacturer provides a recommendation of 35 °C (63 °F).
An older-established way to improve insulation performance is to replace air in the space with a lower thermal conductivity gas. Gas convective heat transfer is a function of viscosity and specific heat. Monatomic gases such as argon, krypton and xenon are often used since (at normal temperatures) they do not carry heat in rotational modes, resulting in a lower heat capacity than poly-atomic gases. Argon has a thermal conductivity 67% that of air, krypton has about half the conductivity of argon. Krypton and Xenon are very expensive. These gases are used because they are non-toxic, clear, odorless, chemically inert, and commercially available because of their widespread application in industry. Some manufacturers also offer sulfur hexafluoride as an insulating gas, especially to insulate sound. It has only 2/3 the conductivity of argon, but it is stable, inexpensive and dense. However, sulfur hexafluoride is an extremely potent greenhouse gas that contributes to global warming. In Europe, SF6 falls under the F-Gas directive which ban or control its usage for several applications. Since 1 January 2006, SF6 is banned as a tracer gas and in all applications except high-voltage switchgear.
In general, the more effective a fill gas is at its optimum thickness, the thinner the optimum thickness is. For example, the optimum thickness for krypton is lower than for argon, and lower for argon than for air. However, since it is difficult to determine whether the gas in an IGU has become mixed with air at time of manufacture (or becomes mixed with air once installed), many designers prefer to use thicker gaps than would be optimum for the fill gas if it were pure. Argon is commonly used in insulated glazing as it is the most affordable. Krypton, which is considerably more expensive, is not generally used except to produce very thin double glazing units or relatively thin, or extremely high performance triple glazed units. Xenon has found very little application in IGUs because of cost.
Heat insulating properties 
The effectiveness of insulated glass can be expressed as an R-value. The higher the R-value, the greater is its resistance to heat transfer. A standard IGU consisting of clear uncoated panes of glass (or lites) with air in the cavity between the lites typically has an R-value of 0.35 K·m2/W (2 h·ft2·°F/BTU).
Using US customary units, a rule of thumb in standard IGU construction is that each change in the component of the IGU results in an increase of 1 R-value to the efficiency of the unit. Adding Argon gas increases the efficiency to about R-3. Using low emissivity glass on surface #2 will add another R-value. Properly designed triple glazed IGUs with low emissivity coatings on surfaces #2 and #4 and filled with argon gas in the cavities result in IG units with R-values as high as R-5. Certain vacuum insulated glass units (VIG) or multi-chambered IG units using coated plastic films result in R-values as high as R-12.5
Additional layers of glazing provide the opportunity for improved insulation. While the standard double glazing is most widely used, triple glazing is not uncommon, and quadruple glazing is produced for very cold environments such as Alaska. Even quintuple glazing (four cavities, five panes) is available - with mid-pane insulation factors equivalent to walls.
Acoustic insulating properties 
In some situations the insulation is in reference to noise mitigation. In these circumstances a large air space improves the noise insulation quality or Sound transmission class. Asymmetric double glazing, using different thicknesses of glass rather than the conventional symmetrical systems (equal glass thicknesses used for both lites) will improve the acoustic attenuation properties of the IGU. If standard air spaces are used, sulfur hexafluoride is used to replace or augment an inert gas and improve acoustical attenuation performance.
Other glazing material variations affect acoustics. The most widely used glazing configurations for sound dampening include laminated glass with varied thickness of the interlayer and thickness of the glass. Including a structural, thermally improved aluminum thermal barrier air spacer in the insulating glass can improve acoustical performance by reducing the transmission of exterior noise sources in the fenestration system.
Reviewing the glazing system components, including the air space material used in the insulating glass, can ensure overall sound transmission improvement.
The life of an IGU varies depending on the quality of materials used, size of gap between inner and outer pane, temperature differences, workmanship and location of installation both in terms of facing direction and geographic location, as well as the treatment the unit receives. IG units typically last from 10 to 25 years, with windows facing south (Northern Hemisphere) or the north (Southern Hemisphere) often lasting less than 12 years. IGUs typically carry a warranty for 10 to 20 years depending upon the manufacturer. If IGUs are altered (such as installation of a solar control film) the warranty may be voided by the manufacturer.
The Insulating Glass Manufacturers Alliance (IGMA) undertook an extensive study to characterize the failures of commercial insulating glass units over a 25-year period.
For a standard construction IG unit, condensation collects between the layers of glass when the perimeter seal has failed and when the desiccant has become saturated, and can generally only be eliminated by replacing the IGU. Seal failure and subsequent replacement results in a significant factor in the overall cost of owning IGUs.
Large temperature differences between the inner and outer panes stresses the spacer adhesives, which can eventually fail. Units with a small gap between the panes are more prone to failure because of the increased stress.
Atmospheric pressure changes combined with wet weather can, in rare cases, eventually lead to the gap filling with water.
In Canada, since the beginning of 1990, there are some companies offering servicing of failed IG units. They provide open ventilation to the atmosphere by drilling hole(s) in the glass and/or spacer. This solution often reverses the visible condensation, but cannot clean the interior surface of the glass and staining that may have occurred after long term exposure to moisture. They may offer a warranty from 5 to 20 years. This solution lowers the insulating value of the window, but it can be a "green" solution when the window is still in good condition. If the IG unit had a gas fill (e.g. argon or krypton or a mixture) the gas is naturally dissipated and the R-value suffers.
Since 2004, there are also some companies offering the same restoration process for failed double glazed units in the UK, and there is one company offering restoration of failed IG units in Ireland since 2010.
Estimating heat loss from double glazed windows 
Given the thermal properties of the sash, frame, and sill, and the dimensions of the glazing and thermal properties of the glass, the heat transfer rate for a given window and set of conditions can be calculated. This can be calculated in kW ( kilowatts ), but more usefully for cost benefit calculations can be stated as kWH pa ( kilowatt hours per annum ), based on the typical conditions over a year for a given location.
The glass panels in double glazed windows transmit heat in both directions by radiation, across the panes by convection, and by conduction around the perimeter seals. The actual rates will vary with the conditions throughout the year, and while solar gain is much welcomed in the winter, it may result in increased air conditioning costs in the summer. The unwanted heat transfer can be mitigated by for example using curtains in the winter and using sun shades in the summer. In an attempt to provide a useful comparison between alternative window constructions the British Fenestration Rating Council have defined a "Window Energy Rating" WER, ranging from A for the best down through B and C etc. This takes into account a combination of the heat loss through the window ( U value ), the solar gain ( g value ), and loss through air leakage around the frame ( L value ). For example, an A Rated window will in a typical year gain as much heat from solar gain as it loses in other ways. This provides better thermal performance than a typical wall.
For a detailed analysis of the possibilities opened up by such glazing see the link to Passive Solar Design below.
See also 
- "Development and quality control of vacuum glazing by N. Ng and L. So; University of Sydney". Glassfiles.com. Retrieved 2011-04-05.
- "Kaye and Laby. Thermal conductivities of gases". Retrieved 2012-10-07.
- F-gas and SF6 restrictions
- ASHRAE Handbook, Volume 1, Fundamentals, 1993
- Sound insulation - Google Books. Books.google.com. Retrieved 2011-04-05.
- "IGMA". Igmaonline.org. Retrieved 2011-04-05.
- Handbook of Chemistry & Physics, 62ed, CRC Press, ISBN-0-8493-0462-8
|Wikimedia Commons has media related to: Insulated glazing|