Littlebrook Power Station
|Littlebrook Power Station|
Littlebrook D power station
Viewed from the south in March 2008
|Location||Kent, South East England|
|grid reference TQ556764|
Littlebrook Power Station refers to a series of four oil and coal-fired power stations situated on the south bank of the River Thames, next to the Queen Elizabeth 2 Bridge and the Dartford Tunnel in Dartford, Kent.
The first power station on the site was the coal-fired Littlebrook A Power Station, built by the Kent Electric Power Company in the early 1930s. It was opened in 1939. Coal was initially brought to the station by rail, until a riverside pier was completed. The station was later converted to burn supplementary oil over coal, and remained in use until it closed in 1973. The 'Station has six coal fired boilers, 3 chain grate and 3 pulverised fuel. The steam raised in the boilers was fed to three steam receivers which in turn supplied three steam turbine generators. Two of the turbines were supplied by CA Parsons at 30MW each driving a directly coupled air cooled alternator running at 3000rpm. The third turbine was supplied by BTH running at 1500 rpm driving a 4-pole air cooled alternator. In its last years the 1500 4 pole alternator was decoupled from its turbine and used as a synchronus compensator thereby providing voltage regulation to its local grid.
The construction of Littlebrook B Power Station was delayed by the Second World War, and came into use between 1949 and 1950. Like the A Station, it originally burned coal, but was later converted to burn oil instead. It had a capacity of 120MW and remained in use until 1975. This 'Station featured several new concepts in power generation design; it incorporated the "unit concept" whereby boilers directly supply steam to its designated turbine-generator. (Previously boilers "pooled" steam via a range or receivers to any of the installed turbines). The steam cycle featured "reheat" where steam exhausting from the initial high pressure turbine cylinder is routed back through the boiler to be reheated thereby increasing its available energy before being returned to the turbine's intermediate cylinder. Finally the 60MW Alternator was cooled by pure hydrogen gas which has a far greater cooling effect than air. These features became common in later power station designs utilising turbine generators rated at 120MW and over.
Littlebrook C Power Station was opened between 1952 and 1956 by the Central Electricity Board, and had a total generating capacity output of 240MW. Like the two earlier plants, it was originally coal-fired, but was converted burn fuel oil by 1958. The station continued operating until it was replaced by the D Station in 1981. This 'Station was built in response to a rapid demand for electricity as the Country emerged from austerity of the post war years. As such it utilised (a standard build) four 60 MW three cylinder non-reheat C A Parsons steam turbine generators supplied from a steam range fed by seven boilers. (The original design specified eight but the last was never built). The alternators (generators) were hydrogen cooled.
Littlebrook A, B & C
As each 'Station was built its outer buildings (Boiler House & Turbine Hall) was erected as a virtual extension to its predecessor although segregated internally. This led to the numeric succession of boilers and turbines, thus the last boiler in "C" 'Station was No. 11; the turbine, No. 9. The 'Station's electrical output was transformed into both 66kV and 132kV and fed designated sub-stations located on site that in turn exported power through 66kV and 132kV grid connections.
Littlebrook D is an oil-fired power station and was built by the nationalised Central Electricity Generating Board. The station was built by the Cleveland Bridge Company with construction starting in 1976. The first unit commissioning underway by 1981. The 1980s still saw a potential threat from the Cold War, and as such the CEGB designed Littlebrook D as a robust station with high plant redundancy, meaning that the station would form a pivotal role should disaster have struck the city of London. At this time, London was still dependant on several smaller generating stations within the city itself. Due to the flexibility of the oil-fired boilers, a cold unit can be synchronised onto the grid within 4 hours and the increased ability to rapidly increase or decrease load forms a significant part of what makes the station attractive on a commercial basis. Five 110,000-tonne fuel oil storage tanks are used to store the heavy fuel oil for the main units, and this fuel is delivered to the site by tankers mooring at one of the site's two jetties on the River Thames.
Originally built with three operational units having a design rating of 660 MW MCR (Maximum Continuous Rating), this was increased to 685 MW during commissioning with practically no additional engineering works required which is testament to the robust design standards rigorously upheld by the CEGB. This total generating capacity of 1,370 MW (1,475 MW including open-cycle gas turbines - see below) is enough power to meet the needs of over 2 million people. Unit 3 has been held in "long term reserve" for a number of years now, mainly due to the wear and tear the boiler experienced during the UK miners strike 1984 to 1985 where oil-fired stations were run aggressively while the base load coal stations were struggling to obtain fuel. During this strike all three units operated simultaneously and continuously throughout with the exception of a short repair period to Unit 3's boiler, thereby exceeding its design intent by continuously generating 2055 MWSO. This resulted in an annual generation of circa 18 000 GW which may be the unofficial record for the CEGB's 2000MW class of power station. The remaining two units are still fully operational, having undergone massive refurbishment investment in recent years to increase their efficiency and further improve the quality of emissions from the 215 m (705 ft) tall chimney, which is the fourth tallest chimney in the UK. Recent investment includes the addition of an electrostatic precipitator to remove any particulates present in the flue gas before it leaves the chimney and the unit control is currently being upgraded to a modern PLC (Programmable Logic Controller) based system.
Although the running regime of the Littlebrook D site has changed significantly since it was built, it still forms a critical strategic component to the UK grid system. The site is one of a number of stations throughout the UK with black-start capabilities, meaning that it is able to start generating without an external power supply - the station would be one of the first to start generating should the UK ever experience a partial or complete blackout. Littlebrook D played a vital role in restoring power supplies to the South East of England in the days following the storm force winds of October 1987. The black-start capability is facilitated by the presence of three open-cycle gas turbines (OCGTs), each capable of generating 35 MW, which is sufficient to operate the station auxiliary equipment and allow a main unit to be started. Each OCGT set incorporates two Rolls-Royce Olympus jet engines which are industrial derivatives of those that were used on the Concorde aircraft. As well as providing black-start supplies to the station, the fact that they can synchronise and ramp up to full load in under five minutes means they are used to generate at the request of National Grid Company (who operate the UK electricity grid system) to deal with short-term peaks in demand. Such peaks typically arise during the winter months, where evening demand is higher due to lighting and heating requirements. A further facility provided to the National Grid Company by the OCGTs is one of system protection. They will start automatically should the system frequency (50.0Hz in the UK) fall to 49.6 Hz, which would indicate that the supply from generation is not sufficient to meet the demand. The National Grid Company are obliged to ensure that there is enough operating reserve available at all times and as such, low frequency events are rare and will only arise where a substantial loss of generation has occurred.
A modification has been made to one of the units which allows for alternative fuel trials. Several have been trialled at the Littlebrook D site as part of ongoing research into generating energy from more sustainable fuel sources. At present, the current owners of the station have decided that Littlebrook is to "opt-out" under the Large Combustion Plant Directive , an EU directive aiming to deal with air pollutants created by the combustion of fossil fuels. This essentially means that Littlebrook D will cease to generate after 2015 in its current configuration.
After privatisation in 1991, the station was owned by National Power, and later by its subsidivision Innogy. The station is currently owned by RWE nPower which is owned by the German utility company, RWE.
- "A - Z list of Bridges Built by Cleveland Bridge Company". Newcastle University. Retrieved 18 April 2011.
- Chimney illustration
|Wikimedia Commons has media related to Littlebrook Power Station.|