|This article needs additional citations for verification. (April 2009)|
In electrical engineering, a load profile is a graph of the variation in the electrical load versus time. A load profile will vary according to customer type (typical examples include residential, commercial and industrial), temperature and holiday seasons. Power producers use this information to plan how much electricity they will need to make available at any given time. Teletraffic engineering uses a similar load curve.
In a power system, a load curve or load profile is a chart illustrating the variation in demand/electrical load over a specific time. Generation companies use this information to plan how much power they will need to generate at any given time. A load duration curve is similar to a load curve. The information is the same but is presented in a different form. These curves are useful in the selection of generator units for supplying electricity.
In an electricity distribution network, the load profile of electricity usage is important to the efficiency and reliability of power transmission. The power transformer or battery-to-grid  are critical aspects of power distribution and sizing and modelling of batteries or transformers depends on the load profile. The factory specification of transformers for the optimization of load losses versus no-load losses is dependent directly on the characteristics of the load profile that the transformer is expected to be subjected to. This includes such characteristics as average load factor, diversity factor, utilization factor, and demand factor, which can all be calculated based on a given load profile.
A transformer typically has a cyclic rating allowing for the variation in the load profile. This cyclic rating allows the transformer to be overloaded at peak times so long as there is a sufficient cooling down period at the lower point in the load profile.
Retail energy markets
In retail energy markets, supplier obligations are settled on an hourly or subhourly basis. For most customers, consumption is measured on a monthly basis, based on meter reading schedules. Load profiles are used to convert the monthly consumption data into estimates of hourly or subhourly consumption in order to determine the supplier obligation. For each hour, these estimates are aggregated for all customers of an energy supplier, and the aggregate amount is used in market settlement calculations as the total demand that must be covered by the supplier.
Calculating and recording load profiles
Load profiles can be determined by direct metering but on smaller devices such as distribution network transformers this is not routinely done. Instead a load profile can be inferred from customer billing or other data. An example of a practical calculation used by utilities is using a transformer's maximum demand reading and taking into account the known number of each customer type supplied by these transformers. This process is called load research.
Actual demand can be collected at strategic locations to perform more detailed load analysis; this is beneficial to both distribution and end-user customers looking for peak consumption. Smart grid meters, utility meter load profilers, data logging sub-meters and portable data loggers are designed to accomplish this task by recording readings at a set interval.
- Electricity generation
- Electric power transmission
- Electricity distribution
- Load duration curve
- Peak demand
- Relative cost of electricity generated by different sources
- California Independent System Operator (Cal ISO) Predicted system capacity and demand with approximate current demand chart for today.
- ACR Systems Inc. Energy demand portable data logger application.
- Planet Ark : E.ON UK Plans Giant Battery to Store Wind Power
- Eromon, David I. (2005), The Dynamics of Transformer Purchasing in a Transformed Electric Market, The International Journal of Modern Engineering 6 (1)