# Photovoltaic system

A photovoltaic system mounted in front of a bank of windows.

A photovoltaic system, also photovoltaic power system, solar PV system, PV system or casually solar array, is a power system designed to supply usable solar power by means of photovoltaics. It consists of an arrangement of several components, including solar panels to absorb and directly convert sunlight into electricity, a solar inverter to change the electrical current from DC to AC, as well as mounting, cabling and other electrical accessories to set-up a working system. It may also use a solar tracking system to improve the system's overall performance or include an integrated battery solution, as prices for storage devices are expected to decline.

Strictly speaking, a solar array only encompasses the ensemble of solar panels, the visible part of the PV system, and does not include all the other hardware, often summarized as balance of system (BOS).

PV systems range from small, roof-top mounted or building-integrated systems with capacities from a few to several tens of kilowatts, to large utility-scale power stations of hundreds of megawatts. Nowadays, most PV systems are connected to the electrical grid, while stand-alone or off-grid systems only account for a small portion of the market.

Operating silently and without any moving parts or environmental emissions, PV systems have developed into a mature technology that has been used for fifty years in specialized applications, and grid-connected systems have been operating for over twenty years. A roof-top system recoups the invested energy for its manufacturing and installation within 0.7 to 2 years and produces about 95 percent of net clean renewable energy over a 30-year service lifetime.[1]:30[2][3]

As new installations are growing exponentially, prices for PV systems have rapidly declined in recent years. However, they vary by markets and the system's size. In the United States, prices for utility-scale systems were around $2.50–$4.00 per watt in 2012,[4] while prices for smaller roof-top systems in the highly penetrated German market fell below €1.40 per watt in 2014.[5] In that market, solar panels make up for 40 to 50 percent of the overall cost, leaving the rest to installation labor and to the PV system's remaining components.[6]

Solar power based on thermal energy, such as concentrated solar power or panels for water heating, are not components of a photovoltaic system.

## Modern system

### Overview

A photovoltaic system converts the sun's radiation into usable electricity. It comprises the solar array and the balance of system components. PV systems may be built in various configurations:

• Grid-connected optionally using a battery storage
• Off-grid without battery (array-direct)
• Off-grid with battery storage, optionally converting to AC

Besides these basic configurations, PV systems can be categorized by various aspects, such as, building-integrated vs. rack-mounted systems, residential vs. utility systems, distributed vs. centralized systems, roof-top vs. ground-mounted systems, tracking vs. fixed-tilt systems, new construction vs. retrofitted systems. Other distinctions may include, systems with microinverters vs. central inverter, systems using crystalline silicon vs. thin-film technology, and systems with modules from Chinese vs. European and US-manufacturers.

About 99 percent of all European and 90 percent of all US-PV systems are connected to the electrical grid, while in Australia and South Korea off-grid systems are somewhat more common.[7]:14 PV systems rarely use battery storage. This may change soon, as government incentives for distributed energy storage are being implemented and investments in storage solutions are gradually becoming economically viable for small systems.[8][9] A solar array of a typical residential PV system is rack-mounted on the roof, rather than integrated into the roof or facade of the building, as this is significantly more expensive. Utility-scale solar power stations are ground-mounted, with fixed tilted solar panels rather than using expensive tracking devices. Crystalline silicon is the predominant material used in 90 percent of worldwide produced solar modules, while rival thin-film has lost market-share in recent years.[1]:17–20 About 70 percent of all solar cells and modules are produced in China and Taiwan, leaving only 5 percent to European and US-manufacturers.[1]:11–12 The installed capacity for both, small rooftop systems and large solar power station is growing rapidly and in equal parts.[7]:43 Photovoltaic systems currently contribute about 1 percent to worldwide electricity generation.[10]

Driven by advances in technology and increases in manufacturing scale and sophistication, the cost of photovoltaics is declining continuously and the installed capacity of PV systems is growing exponentially.[3] There are several million PV systems distributed all over the world, mostly in Europe, with 1.4 million systems in Germany alone[1]:5– as well as North America with 440,000 systems in the United States,[11] China and Japan, the world's fastest growing regions. The energy conversion efficiency of a conventional solar module increased from 15 to 20 percent over the last 10 years[1]:17 and a PV system recoups the energy needed for its manufacture in about 2 years. In exceptionally irradiated locations, or when thin-film technology is used, the so-called energy payback time decreases to one year or less.[1]:30–33 Net metering and financial incentives, such as preferential feed-in tariffs for solar-generated electricity, have also greatly supported installations of PV systems in many countries.[12] The levelised cost of electricity (LCOE) from PV systems has become competitive with conventional electricity sources in an expanding list of geographic regions, as grid parity has been achieved in many different markets.[13][14]

### Grid-connection

Schematics of a typical residential PV system

A grid connected system is connected to a larger independent grid (typically the public electricity grid) and feeds energy directly into the grid. This energy may be shared by a residential or commercial building before or after the revenue measurement point. The difference being whether the credited energy production is calculated independently of the customer's energy consumption (feed-in tariff) or only on the difference of energy (net metering). Grid connected systems vary in size from residential (2-10kWp) to solar power stations (up to 10s of MWp). This is a form of decentralized electricity generation. The feeding of electricity into the grid requires the transformation of DC into AC by a special, synchronising grid-tie inverter.[15] In kW sized installations the DC side system voltage is as high as permitted (typically 1000V except US residential 600V) to limit ohmic losses. Most modules (72 crystalline silicon cells) generate 160W to 300W at 36 volts. It is sometimes necessary or desirable to connect the modules partially in parallel rather than all in series. One set of modules connected in series is known as a 'string'.[16]

### Scale of system

Photovoltaic systems are generally categorized into three distinct market segments: residential roof-top, commercial roof-top, and ground-mount utility-scale systems. Their capacities range from a few kilowatts to hundreds of megawats. A typical residential system is around 10 kilowatts and mounted on a sloped roof, while commercial systems may reach a megawatt-scale and are generally installed on low-slope or even flat roofs. Allthough roof-top mounted systems are small and display a higher cost per watt than large utility-scale installations, they account for the largest share in the market. There is, however, a growing trend towards bigger utility-scale power plants, especially in the "sunbelt" region of the planet.[7]:43[17]

Roof-top system
A 5.3 kW residential rooftop system near Boston, United States.

A small PV system is capable of providing enough AC electricity to power a single home, or even an isolated device in the form of AC or DC electric. For example, military and civilian Earth observation satellites, street lights, construction and traffic signs, electric cars, solar-powered tents,[18] and electric aircraft may contain integrated photovoltaic systems to provide a primary or auxiliary power source in the form of AC or DC power, depending on the design and power demands. In 2013, roof-top systems accounted for 60percent of worldwide installations.

Building-integrated system
Building integrated solar panels in Helsinki, Finland

In urban and suburban areas, photovoltaic arrays are commonly used on rooftops to supplement power use; often the building will have a connection to the power grid, in which case the energy produced by the PV array can be sold back to the utility in some sort of net metering agreement. Some utilities, such as Solvay Electric in Solvay, NY, use the rooftops of commercial customers and telephone poles to support their use of PV panels.[19] Solar trees are arrays that, as the name implies, mimic the look of trees, provide shade, and at night can function as street lights.

Utility-scale
The community-owned Westmill Solar Park in South East England

Large utility-scale solar parks or farmss are power stations and capable of providing an energy supply to large numbers of consumers. Generated electricity is fed into the transmission grid powered by central generation plants (grid-connected or grid-tied plant), or combined with one, or many, domestic electricity generators to feed into a small electrical grid (hybrid plant). In rare cases generated electricity is stored or used directly by island/standalone plant.[20][21] PV systems are generally designed in order to ensure the highest energy yield for a given investment. Some large photovoltaic power stations like Waldpolenz Solar Park and Topaz Solar Farm cover tens or hundreds of hectares and have power outputs up to hundreds of megawatts.

### Performance

Uncertainties in revenue over time relate mostly to the evaluation of the solar resource and to the performance of the system itself. In the best of cases, uncertainties are typically 4% for year-to-year climate variability, 5% for solar resource estimation (in a horizontal plane), 3% for estimation of irradiation in the plane of the array, 3% for power rating of modules, 2% for losses due to dirt and soiling, 1.5% for losses due to snow, and 5% for other sources of error. Identifying and reacting to manageable losses is critical for revenue and O&M efficiency. Monitoring of array performance may be part of contractual agreements between the array owner, the builder, and the utility purchasing the energy produced.[citation needed] Recently, a method to create "synthetic days" using readily available weather data and verification using the Open Solar Outdoors Test Field make it possible to predict photovoltaic systems performance with high degrees of accuracy.[22] This method can be used to then determine loss mechanisms on a local scale - such as those from snow [23][24] or the effects of surface coatings (e.g. hydrophobic or hydrophilic) on soiling or snow losses.[25] Access to the Internet has allowed a further improvement in energy monitoring and communication. Dedicated systems are available from a number of vendors. For solar PV system that use microinverters (panel-level DC to AC conversion), module power data is automatically provided. Some systems allow setting performance alerts that trigger phone/email/text warnings when limits are reached. These solutions provide data for the system owner and the installer. Installers are able to remotely monitor multiple installations, and see at-a-glance the status of their entire installed base.[citation needed]

## Components

The Balance of system components of a PV system (BOS) balance the power-generating subsystem of the solar array (left side) with the power-using side of the AC-household devices and the utility grid (right side).

A photovoltaic system for residential, commercial, or industrial energy supply consists of the solar array and a number of components often sumarized as the balance of system (BOS). The term originates from the fact that some BOS-components are balancing the power-generating subsystem of the solar array with the power-using side, the load. BOS-components include power-conditioning equipment and structures for mounting, typically one or more DC to AC power converters, also known as inverters, an energy storage device, a racking system that supports the solar array, electrical wiring and interconnections, and mounting for other components.

Diagram of the possible components of a photovoltaic system.

Optionally, a balance of system may include any or all of the following: renewable energy credit revenue-grade meter, maximum power point tracker (MPPT), battery system and charger, GPS solar tracker, energy management software, solar irradiance sensors, anemometer, or task-specific accessories designed to meet specialized requirements for a system owner. In addition, a CPV system requires optical lenses or mirrors and sometimes a cooling system.

The terms "solar array" and "PV system" are often used interchangeably, despite the fact that the solar array does not encompass the entire system. Moreover, "solar panel" is often used as a synonym for "solar module", although a panel consists of a string of several modules. The term "solar system" is also an often used misnomer for a PV system.

### Solar array

Fixed tilt solar array in Canterbury, New Hampshire, United States
Further information: photovoltaics, solar module and solar cell

Conventional solar cells, normally wired in series, are encapsulated in a solar module to protect them from the weather.The module consists of a tempered glass as cover, a soft and flexible encapsulant, a rear backsheet made of a weathering and fire-resistant material and an alumnium frame around the outer edge. Electrically connected and mounted on a supporting structure, solar modules build a string of modules, often called solar panel. A solar array consists of one or many such panels.[26]

A photovoltaic array (or solar array) is a linked collection of solar panels.[27] The power that one module can produce is seldom enough to meet requirements of a home or a business, so the modules are linked together to form an array.

Solar array of a power plant on Mt. Komekura, Japan

Most PV arrays use an inverter to convert the DC power produced by the modules into alternating current that can power lights, motors, and other loads. The modules in a PV array are usually first connected in series to obtain the desired voltage; the individual strings are then connected in parallel to allow the system to produce more current. Solar panels are typically measured under STC (standard test conditions) or PTC (PVUSA test conditions), in watts.[28] Typical panel ratings range from less than 100 watts to over 400 watts.[29] The array rating consists of a summation of the panel ratings, in watts, kilowatts, or megawatts.

Insolation and energy

Solar insolation is made up of direct, diffuse, and reflected radiation. The absorption factor of a PV cell is deﬁned as the fraction of incident solar irradiance that is absorbed by the cell.[30] At high noon on a cloudless day at the equator, the power of the sun is about 1 kW/m²,[31] on the Earth's surface, to a plane that is perpendicular to the sun's rays. As such, PV arrays can track the sun through each day to greatly enhance energy collection. However, tracking devices add cost, and require maintenance, so it is more common for PV arrays to have fixed mounts that tilt the array and face solar noon (approximately due south in the Northern Hemisphere or due north in the Southern Hemisphere). The tilt angle, from horizontal, can be varied for season,[32] but if fixed, should be set to give optimal array output during the peak electrical demand portion of a typical year for a stand alone system. This optimal module tilt angle is not necessarily identical to the tilt angle for maximum annual array energy output.[33]

Global solar potential

The optimization of the a photovoltaic system for a specific environment can be complicated as issues of solar flux, soiling, and snow losses should be taken into effect. In addition, recent work has shown that spectral effects can play a role in optimal photovoltaic material selection. For example, the spectral albedo can play a significant role in output depending on the surface around the photovoltaic system [34] and the type of solar cell material.[35]

For the weather and latitudes of the United States and Europe, typical insolation ranges from 4 kWh/m²/day in northern climes to 6.5 kWh/m²/day in the sunniest regions. Typical solar panels have an average efficiency of 15%, with the best commercially available panels at 21%. Thus, a photovoltaic installation in the southern latitudes of Europe or the United States may expect to produce 1 kWh/m²/day. A typical "150 watt" solar panel is about a square meter in size. Such a panel may be expected to produce 0.75 kWh every day, on average, after taking into account the weather and the latitude, for an insolation of 5 sun hours/day. A typical 1 kW photovoltaic installation in Australia or the southern latitudes of Europe or United States, may produce 3.5-5 kWh per day, dependent on location, orientation, tilt, insolation and other factors.[36] In the Sahara desert, with less cloud cover and a better solar angle, one could ideally obtain closer to 8.3 kWh/m²/day provided the nearly ever present wind would not blow sand onto the units. The area of the Sahara desert is over 9 million km². 90,600 km², or about 1%, could generate as much electricity as all of the world's power plants combined.[37]

Module

Module output and life are also degraded by increased temperature. Allowing ambient air to flow over, and if possible behind, PV modules reduces this problem. Effective module lives are typically 25 years or more.[38] The payback period for an investment in a PV solar installation varies greatly and is typically less useful than a calculation of return on investment.[39] While it is typically calculated to be between 10 and 20 years, the financial payback period can be far shorter with incentives.[40]

Efficiency
Solar array at National Solar Energy Center in the Negev Desert, Israel

Due to the low voltage of an individual solar cell (typically ca. 0.5V), several cells are wired (see: Copper in photovoltaic power systems) in series in the manufacture of a "laminate". The laminate is assembled into a protective weatherproof enclosure, thus making a photovoltaic module or solar panel. Modules may then be strung together into a photovoltaic array.

In 2012, solar panels available for consumers can have an efficiency of up to about 17%,[41] while commercially available panels can go as far as 27%. It has been recorded that a group from the The Fraunhofer Institute for Solar Energy Systems have created a cell that can reach 44.7% efficiency, which makes scientists' hopes of reaching the 50% efficiency threshold a lot more feasible.[42][43][44][45]

Several methods have been developed to determine shading losses from trees to PV systems over both large regions using LiDAR,[50] but also at an individual system level using sketchup.[51] Most modules have bypass diodes between each cell or string of cells that minimize the effects of shading and only lose the power of the shaded portion of the array. The main job of the bypass diode is to eliminate hot spots that form on cells that can cause further damage to the array, and cause fires. Sunlight can be absorbed by dust, snow, or other impurities at the surface of the module. This can reduce the light that strikes the cells. In general these losses aggregated over the year are small even for locations in Canada.[23] Maintaining a clean module surface will increase output performance over the life of the module. Google found that cleaning the flat mounted solar panels after 15 months increased their output by almost 100%, but that the 5% tilted arrays were adequately cleaned by rainwater.[52][24]

### Cabling

Main articles: Solar cable and Electrical wiring

Due to their outdoor usage, solar cables are specifically designed to be resistant against UV radiation and extremely high temperature fluctuations and are generally unaffected by the weather. A number of standards specify the usage of electrical wiring in PV systems, such as the IEC 60364 by the International Electrotechnical Commission, in section 712 "Solar photovoltaic (PV) power supply systems", the British Standard BS 7671, incorporating regulations relating to microgeneration and photovoltaic systems, and the US UL4703 standard, in subject 4703 "Photovoltaic Wire".

### Mounting systems

A 23-year old, ground mounted PV system on a North Frisian Island, Germany

Modules are assembled into arrays on some kind of mounting system, which may be classified as ground mount, roof mount or pole mount. For solar parks a large rack is mounted on the ground, and the modules mounted on the rack. For buildings, many different racks have been devised for pitched roofs. For flat roofs, racks, bins and building integrated solutions are used.[citation needed] Solar panel racks mounted on top of poles can be stationary or moving, see Trackers below. Side-of-pole mounts are suitable for situations where a pole has something else mounted at its top, such as a light fixture or an antenna. Pole mounting raises what would otherwise be a ground mounted array above weed shadows and livestock, and may satisfy electrical code requirements regarding inaccessibility of exposed wiring. Pole mounted panels are open to more cooling air on their underside, which increases performance. A multiplicity of pole top racks can be formed into a parking carport or other shade structure. A rack which does not follow the sun from left to right may allow seasonal adjustment up or down.

### Solar trackers

A 1998 model of a passive solar tracker, viewed from underneath.
Main article: Solar tracker

A solar tracking system tilts a solar panel throughout the day. Depending on the type of tracking system, the panel is either aimed directly at the sun or the brightest area of a partly clouded sky. Trackers greatly enhance early morning and late afternoon performance, increasing the total amount of power produced by a system by about 20–25% for a single axis tracker and about 30% or more for a dual axis tracker, depending on latitude.[53][54] Trackers are effective in regions that receive a large portion of sunlight directly. In diffuse light (i.e. under cloud or fog), tracking has little or no value. Because most concentrated photovoltaics systems are very sensitive to the sunlight's angle, tracking systems allow them to produce useful power for more than a brief period each day.[55] Tracking systems improve performance for two main reasons. First, when a solar panel is perpendicular to the sunlight, it receives more light on its surface than if it were angled. Second, direct light is used more efficiently than angled light[citation needed]. Special Anti-reflective coatings can improve solar panel efficiency for direct and angled light, somewhat reducing the benefit of tracking.[56]

Trackers and sensors to optimise the performance are often seen as optional, but tracking systems can increase viable output by up to 45%.[27][57] PV arrays that approach or exceed one megawatt often use solar trackers. Accounting for clouds, and the fact that most of the world is not on the equator, and that the sun sets in the evening, the correct measure of solar power is insolation – the average number of kilowatt-hours per square meter per day. For the weather and latitudes of the United States and Europe, typical insolation ranges from 2.26 kWh/m²/day in northern climes to 5.61 kWh/m²/day in the sunniest regions.[58][59]

For large systems, the energy gained by using tracking systems can outweigh the added complexity (trackers can increase efficiency by 30% or more). For very large systems, the added maintenance of tracking is a substantial detriment.[60] Tracking is not required for flat panel and low-concentration photovoltaic systems. For high-concentration photovoltaic systems, dual axis tracking is a necessity.[61]

Pricing trends affect the balance between adding more stationary solar panels versus having fewer panels that track. When solar panel prices drop, trackers become a less attractive option.

### Solar inverters

Inverter for grid connected PV

Systems designed to deliver alternating current (AC), such as grid-connected applications need an inverter to convert the direct current (DC) from the solar modules to AC. Grid connected inverters must supply AC electricity in sinusoidal form, synchronized to the grid frequency, limit feed in voltage to no higher than the grid voltage and disconnect from the grid if the grid voltage is turned off.[62] Islanding inverters need only produce regulated voltages and frequencies in a sinusoidal waveshape as no synchronisation or co-ordination with grid supplies is required.

Inverter (left), generation meter, and AC disconnect (right). A modern 2013 installation in Vermont, United States.

A solar inverter may connect to a string of solar panels. In some installations a solar micro-inverter is connected at each solar panel.[63] For safety reasons a circuit breaker is provided both on the AC and DC side to enable maintenance. AC output may be connected through an electricity meter into the public grid.[64] The number of modules in the system determines the total DC watts capable of being generated by the solar array; however, the inverter ultimately governs the amount of AC watts that can be distributed for consumption. For example: A PV system comprising 11 kilowatts DC (kWDC) worth of PV modules, paired with one 10-kilowatt AC (kWAC) inverter, will be limited by the maximum output of the inverter: 10 kW AC.

Maximum power point tracking

Maximum power point tracking (MPPT) is a technique that grid connected inverters use to get the maximum possible power from the photovoltaic array. In order to do so, the Inverter's MPPT system digitally samples the solar array's ever changing power output and applies the proper resistance to find the optimal maximum power point.[65]

Anti-islanding

Anti-islanding is a protection mechanism, that immediately shuts down the inverter preventing it from generating AC-power, when the connection to the load no longer exists. This happens, for example, in the case of a blackout. Without this protection, the supply line would become an "island" with power surrounded by a "sea" of unpowered lines, as the solar array continues to deliver DC power during the power outage. Islanding is a hazard to utility workers, who may not realize that a AC-circuit is still powered, and it may prevent automatic re-connection of devices.[66]

### Charge controller

Main article: Charge controller

PV systems with integrated battery solutions also need a charge controller, as the varying voltage and current from the solar array requires constant adjustment to prevent damage from overcharging.[67] Basic charge controllers may simply turn the PV panels on and off, or may meter out pulses of energy as needed, a strategy called PWM or pulse-width modulation. More advanced charge controllers will incorporate MPPT logic into their battery charging algorithms. Charge controllers may also divert energy to some purpose other than battery charging. Rather than simply shut off the free PV energy when not needed, a user may choose to heat air or water once the battery is full.

### Battery

Although still expensive, PV systems increasingly use rechargeable batteries to store a surplus to be later used at night. Batteries used for grid-storage also stabilize the electrical grid by leveling out peak loads, and play an important role in a smart grid, as they can charge during periods of low demand and feed their stored energy into the grid when demand is high.

Common battery technologies used in today's PV systems include, the valve regulated lead-acid battery– a modified version of the conventional lead–acid battery, nickel–cadmium and lithium-ion batteries. Compared to the other types, lead-acid batteries have a shorter lifetime and lower energy density. However, due to their high reliability, low self discharge as well as low investment and maintenance costs, they are currently the predominant technology used in small-scale, residential PV systems, as lithium-ion batteries are still being developed and about 3.5 times as expensive as lead-acid batteries. Furthermore, as storage devices for PV systems are used stationary, the lower energy and power density and therefore higher weight of lead-acid batteries are not as critical as, for example, in electric transportation[8]:4,9

Other rechargeable batteries that are considered for distributed PV systems include, sodium–sulfur and vanadium redox batteries, two prominent types of a molten salt and a flow battery, respectively.[8]:4

### Monitoring and metering

The metering must be able to accumulate energy units in both directions or two meters must be used. Many meters accumulate bidirectionally, some systems use two meters, but a unidirectional meter (with detent) will not accumulate energy from any resultant feed into the grid.[68]

In some countries, for installations over 30 kWp a frequency and a voltage monitor with disconnection of all phases is required. This is done where more solar power is being generated than can be accommodated by the utility, and the excess can not either be exported or stored. Grid operators historically have needed to provide transmission lines and generation capacity. Now they need to also provide storage. This is normally hydro-storage, but other means of storage are used. Initially storage was used so that baseload generators could operate at full output. With variable renewable energy, storage is needed to allow power generation whenever it is available, and consumption whenever it is needed. The two variables a grid operator have are storing electricity for when it is needed, or transmitting it to where it is needed. If both of those fail, installations over 30kWp can automatically shut down, although in practice all inverters maintain voltage regulation and stop supplying power if the load is inadequate. Grid operators have the option of curtailing excess generation from large systems, although this is more commonly done with wind power than solar power, and results in a substantial loss of revenue.[69] Three-phase inverters have the unique option of supplying reactive power which can be advantageous in matching load requirements.[70]

Photovoltaic systems need to be monitored to detect breakdown and optimize their operation. Several photovoltaic monitoring strategies depending on the output of the installation and its nature. Monitoring can be performed on site or remotely. It can measure production only, retrieve all the data from the inverter or retrieve all of the data from the communicating equipment (probes, meters, etc.). Monitoring tools can be dedicated to supervision only or offer additional functions. Individual inverters and battery charge controllers may include monitoring using manufacturer specific protocols and software.[71] Energy metering of an inverter may be of limited accuracy and not suitable for revenue metering purposes. A third-party data acquisition system can monitor multiple inverters, using the inverter manufacturer's protocols, and also acquire weather-related information. Independent smart meters may measure the total energy production of a PV array system. Separate measures such as satellite image analysis or a solar radiation meter (a pyranometer) can be used to estimate total insolation for comparison.[72] Data collected from a monitoring system can be displayed remotely over the World Wide Web. For example, the Open Solar Outdoors Test Field (OSOTF)[73] is a grid-connected photovoltaic test system, which continuously monitors the output of a number of photovoltaic modules and correlates their performance to a long list of highly accurate meteorological readings. The OSOTF is organized under open source principles—All data and analysis is be made freely available to the entire photovoltaic community and the general public.[74] The Fraunhofer Center for Sustainable Energy Systems maintains two test systems, one in Massachusetts, and the Outdoor Solar Test Field OTF-1 in Albuquerque, New Mexico, which opened in June 2012. A third site, OTF-2, also in Albuquerque, is under construction.[75] Some companies offer analysis software to analyze system performance. Small residential systems may have minimal data analysis requirements other than perhaps total energy production; larger grid-connected power plants can benefit from more detailed investigations of performance.[76][77][78]

## Other systems

This section includes systems that are either highly specialized and uncommon or still an emerging new technology with limited significance. However, standalone or off-grid systems take a special place. They were the most common type of systems during the 1980s and 1990s, when PV technology was still very expensive. Only in places where no electrical grid was available, they were economically viable. Although new stand-alone systems are still being deployed all around the world, their contribution to the overall installed photovoltaic capacity is decreasing. In Europe, off-grid systems account for 1 percent of installed capacity. In the United States, they account for about 10 percent. Off-grid systems are still common in Australia and South Korea, and in many deveolping countries.[7]:14

### Standalone system

Solar parking meter in Edinburgh, Scotland.
An isolated mountain hut in Catalonia, Spain

A stand-alone, or off-grid system is not connected to the electrical grid. Standalone systems vary widely in size and application from wristwatches or calculators to remote buildings or spacecraft. If the load is to be supplied independently of solar insolation, the generated power is stored and buffered with a battery. In non-portable applications where weight is not an issue, such as in buildings, lead acid batteries are most commonly used for their low cost and tolerance for abuse.

A charge controller may be incorporated in the system to: a) avoid battery damage by excessive charging or discharging and, b) optimizing the production of the cells or modules by maximum power point tracking (MPPT). However, in simple PV systems where the PV module voltage is matched to the battery voltage, the use of MPPT electronics is generally considered unnecessary, since the battery voltage is stable enough to provide near-maximum power collection from the PV module. In small devices (e.g. calculators, parking meters) only direct current (DC) is consumed. In larger systems (e.g. buildings, remote water pumps) AC is usually required. To convert the DC from the modules or batteries into AC, an inverter is used.

In agricultural settings, the array may be used to directly power DC pumps, without the need for an inverter. In remote settings such as mountainous areas, islands, or other places where a power grid is unavailable, solar arrays can be used as the sole source of electricity, usually by charging a storage battery.[citation needed]

Solar vehicle
The Japanese winner of 2009 World Solar Challenge in Australia.
Main article: Solar vehicle

Ground, water, air or space vehicles may obtain some or all of the energy required for their operation from the sun. Surface vehicles generally require higher power levels than can be sustained by a practically sized solar array, so a battery is used to meet peak power demand, and the solar array recharges it. Space vehicles have successfully used solar photovoltaic systems for years of operation, eliminating the weight of fuel or primary batteries.

Solar pump
A small solar water pump system with 5 hp

One of the most cost effective solar applications is a solar powered pump, as it is far cheaper to purchase a solar panel than it is to run power lines.[79][80][81] They often meet a need for water beyond the reach of power lines, taking the place of a windmill or windpump. One common application is the filling of livestock watering tanks, so that grazing cattle may drink. Another is the refilling of drinking water storage tanks on remote or self-sufficient homes.

Fan

Connecting a photovoltaic panel directly to a DC mechanical fan motor can provide air movement when it is most needed during the day. Common applications include both attic and greenhouse ventilation. Increased efficiency can be obtained by interposing a linear current booster (LCB) between the solar panel and the fan motor, to more closely coordinate varying panel output with motor energy requirements. Other controls sometimes used are timers and thermostats, so that the fan does not run when not wanted, even if the sun is shining.

Micro system
Main article: Microgeneration

With a growing DIY-community and an increasing interest in environmentally friendly "green energy", some hobbyists have endeavored to build their own PV solar systems from kits[82] or partly diy.[83] Usually, the DIY-community uses inexpensive[84] or high efficiency systems[85] (such as those with solar tracking) to generate their own power. As a result, the DIY-systems often end up cheaper than their commercial counterparts.[86] Often, the system is also hooked up into the regular power grid, using net metering instead of a battery for backup. These systems usually generate power amount of ~2 kW or less. Through the internet, the community is now able to obtain plans to construct the system (at least partly DIY) and there is a growing trend toward building them for domestic requirements. Small scale solar systems are now also being used both in developed countries and in developing countries, for residences and small businesses.[87][88]

Gallery of standalone systems

### CPV and HCPV system

Concentrated photovoltaic (CPV) and high concentrated photovoltaic (HCPV) systems use optical lenses or curved mirrors to concentrate sunlight onto small but highly efficient solar cells. Besides concentrating optics, CVP systems sometime use solar trackers and cooling systems and are more expensive.

Especially HCPV systems are best suited in location with high solar irradiance, concentrating sunlight up to 400 times or more, with efficiencies of 24–28 percent, exceeding those of regular systems. Various designs of CPV and HCPV systems are commercially available but not very common. However, ongoing research and development is taking place.[1]:26

CPV is often confused with CSP (concentrated solar power) that does not use photovoltaics. Both technologies favor locations that receive much sunlight and are directly competing with each other.

### Hybrid system

Schematics of a hybrid system

A hybrid system combines PV with other forms of generation, usually a diesel generator. Biogas is also used. The other form of generation may be a type able to modulate power output as a function of demand. However more than one renewable form of energy may be used e.g. wind. The photovoltaic power generation serves to reduce the consumption of non renewable fuel. Hybrid systems are most often found on islands. Pellworm island in Germany and Kythnos island in Greece are notable examples (both are combined with wind).[89][90] The Kythnos plant has reduced diesel consumption by 11.2%.[91]

There has also been recent work showing that the PV penetration limit can be increased by deploying a distributed network of PV+CHP hybrid systems in the U.S.[92] The temporal distribution of solar flux, electrical and heating requirements for representative U.S. single family residences were analyzed and the results clearly show that hybridizing CHP with PV can enable additional PV deployment above what is possible with a conventional centralized electric generation system. This theory was reconfirmed with numerical simulations using per second solar flux data to determine that the necessary battery backup to provide for such a hybrid system is possible with relatively small and inexpensive battery systems.[93] In addition, large PV+CHP systems are possible for institutional buildings, which again provide back up for intermittent PV and reduce CHP runtime.[94]

PVT system

A hybrid PV/T, or PVT system uses photovoltaic thermal hybrid solar collectors that convert solar radiation into thermal and electrical energy. Such a system combines solar (PV) module with a solar thermal collector in an complementary way.

CPVT system

A concentrated photovoltaic thermal hybrid (CPVT) system is s PVT system, that uses concentrated photovoltaics (CPV) instead of conventional PV technology.

### Floatovoltaic system

Floatovoltaics are PV systems that float on the surface of drinking water reservoirs, quarry lakes, irrigation canals or remediation and tailing ponds. A small number of such systems exist in Japan and France, as well as in the UK and the United States.[95][96]

### DC-grid system

DC grids are found in electric powered transport: railways trams and trolleybuses. A few pilot plants for such applications have been built, such as the tram depots in Hannover Leinhausen, using photovoltaic contributors[97] and Geneva (Bachet de Pesay).[98] The 150 kWp Geneva site feeds 600V DC directly into the tram/trolleybus electricity network whereas before it provided about 15% of the electricity at its opening in 1999.

## Costs and economy

Median installed system prices for residential PV Systems in Japan, Germany and the United States ($/W) History of PV roof-top prices since 2006. Comparison for differnt markets in US$ per installed watt.[99][100]:16,27[101]
 Japan United States Germany

Costs of production have been reduced dramatically in recent years for more widespread use through production and technological advances. For large-scale installations, prices below $1.00 per watt are now common.[102] A price decrease of 50% had been achieved in Europe from 2006 to 2011 and there is a potential to lower the generation cost by 50% by 2020.[103] Crystal silicon solar cells have largely been replaced by less expensive multicrystalline silicon solar cells, and thin film silicon solar cells have also been developed recently at lower costs of production. Although they are reduced in energy conversion efficiency from single crystalline "siwafers", they are also much easier to produce at comparably lower costs.[104] The table below shows the total cost in US cents per kWh of electricity generated by a photovoltaic system.[105][106] The row headings on the left show the total cost, per peak kilowatt (kWp), of a photovoltaic installation. Photovoltaic system costs have been declining and in Germany, for example, were reported to have fallen to USD 2200/kWp by the second quarter of 2012.[107] The column headings across the top refer to the annual energy output in kWh expected from each installed kWp. This varies by geographic region because the average insolation depends on the average cloudiness and the thickness of atmosphere traversed by the sunlight. It also depends on the path of the sun relative to the panel and the horizon. Panels are usually mounted at an angle based on latitude, and often they are adjusted seasonally to meet the changing solar declination. Solar tracking can also be utilized to access even more perpendicular sunlight, thereby raising the total energy output. The calculated values in the table reflect the total cost in cents per kWh produced. They assume a 10% total capital cost (for instance 4% interest rate, 1% operating and maintenance cost,[108] and depreciation of the capital outlay over 20 years). Normally, photovoltaic modules have a 25 year warranty.[109][110] Cost of generated kilowatt-hour by a PV-System in US¢/kWh depending on insolation and installation cost (over 20 years) Installation cost in$ per watt
Insolation anually generated kilowatt-hours per installed kW-capacity (kWh/kWp•y)
2400 2200 2000 1800 1600 1400 1200 1000 800
$0.20 0.8 0.9 1.0 1.1 1.3 1.4 1.7 2.0 2.5$0.60 2.5 2.7 3.0 3.3 3.8 4.3 5.0 6.0 7.5
$1.00 4.2 4.5 5.0 5.6 6.3 7.1 8.3 10.0 12.5$1.40 5.8 6.4 7.0 7.8 8.8 10.0 11.7 14.0 17.5
$1.80 7.5 8.2 9.0 10.0 11.3 12.9 15.0 18.0 22.5$2.20 9.2 10.0 11.0 12.2 13.8 15.7 18.3 22.0 27.5
$2.60 10.8 11.8 13.0 14.4 16.3 18.6 21.7 26.0 32.5$3.00 12.5 13.6 15.0 16.7 18.8 21.4 25.0 30.0 37.5
$3.40 14.2 15.5 17.0 18.9 21.3 24.3 28.3 34.0 42.5$3.80 15.8 17.3 19.0 21.1 23.8 27.1 31.7 38.0 47.5
$4.20 17.5 19.1 21.0 23.3 26.3 30.0 35.0 42.0 52.5$4.60 19.2 20.9 23.0 25.6 28.8 32.9 38.3 46.0 57.5

## References

1. "Photovoltaics Report". Fraunhofer ISE. 28 July 2014. Archived from the original on 31 August 2014. Retrieved 31 August 2014.
2. ^ Service Lifetime Prediction for Encapsulated Photovoltaic Cells/Minimodules, A.W. Czanderna and G.J. Jorgensen, National Renewable Energy Laboratory, Golden, CO.
3. ^ a b M. Bazilian, I. Onyeji, M. Liebreich et al. (2013). "Re-considering the economics of photovoltaic power". Renewable Energy (53). Archived from the original on 31 August 2014. Retrieved 31 August 2014.
4. ^ Installed Price of Solar Photovoltaic Systems in the U.S. Continues to Decline at a Rapid Pace
5. ^ http://www.photovoltaik-guide.de [1] History of monthly turn-key prices for roof-top PV systems up to 100 kWp in euros per kilowatt
6. ^ Fraunhofer ISE Levelized Cost of Electricity Study, Novermber 2013, p. 19
7. ^ a b c d "Global Market Outlook for Photovoltaics 2014-2018". www.epia.org. EPIA - European Photovoltaic Industry Association. Archived from the original on 12 June 2014. Retrieved 12 June 2014.
8. ^ a b c ETH Zürich, Harvard University The Economic Viability of Battery Storage for Residential Solar Photovoltaic Systems - A Review and a Simulation Model Joern Hoppmann, Jonas Volland, Tobias S. Schmidt, Volker H. Hoffmann, July 2014
9. ^ FORBES, Justin Gerdes, Solar Energy Storage About To Take Off In Germany and California, 18 July 2013
10. ^ "Snapshot of Global PV 1992-2013". 2nd Edition ISBN 978-3-906042-19-0. International Energy Agency - Photovoltaic Power Systems Programme. 2014. Archived from the original on 5 April 2014.
12. ^ Renewable Energy Policy Network for the 21st century (REN21), Renewables 2010 Global Status Report, Paris, 2010, pp. 1–80.
13. ^ Branker, K.; Pathak, M.J.M.; Pearce, J.M. (2011). "A Review of Solar Photovoltaic Levelized Cost of Electricity". Renewable and Sustainable Energy Reviews 15 (9): 4470. doi:10.1016/j.rser.2011.07.104. hdl:1974/6879.
14. ^ "Levelized Cost of Electricity—Renewable Energy Technologies" (PDF). http://www.ise.fraunhofer.de. Fraunhofer ISE. November 2013. p. 4. Archived from the original on 3 August 2014. Retrieved 3 August 2014.
15. ^ How Solar Power Works
16. ^ Photovoltaic... Cell, Module, String, Array
17. ^ NREL.gov Residential, Commercial, and Utility-Scale Photovoltaic (PV) System Prices in the United States, p.6 February 2012
18. ^ Army evaluating transportable solar-powered tents | Article | The United States Army. Army.mil (2010-12-08). Retrieved on 2013-07-17.
19. ^ [2]
20. ^ Types of PV systems. Florida Solar Energy Center (FSEC), a research institute of the University of Central Florida.
21. ^ Rahmani, R.; Fard, M.; Shojaei, A.A.; Othman, M.F.; Yusof, R., A complete model of stand-alone photovoltaic array in MATLAB-Simulink environment, 2011 IEEE Student Conference on Research and Development (SCOReD), pp 46–51, 2011.
22. ^ Rob Andrews, Andrew Pollard, Joshua M. Pearce, “Improved parametric empirical determination of module short circuit current for modelling and optimization of solar photovoltaic systems”, Solar Energy 86, 2240-2254 (2012). DOI, open access
23. ^ a b Rob Andrews and Joshua M. Pearce, “Prediction of Energy Effects on Photovoltaic Systems due to Snowfall Events” in: 2012 38th IEEE Photovoltaic Specialists Conference (PVSC). Presented at the 2012 38th IEEE Photovoltaic Specialists Conference (PVSC), pp. 003386 –003391. Available: DOI open access
24. ^ a b Rob W. Andrews, Andrew Pollard, Joshua M. Pearce, “The Effects of Snowfall on Solar Photovoltaic Performance ”, Solar Energy 92, 8497 (2013). DOI: http://dx.doi.org/10.1016/j.solener.2013.02.014 open access
25. ^ Rob W. Andrews, Andrew Pollard, Joshua M. Pearce, A new method to determine the effects of hydrodynamic surface coatings on the snow shedding effectiveness of solar photovoltaic modules. Solar Energy Materials and Solar Cells 113 (2013) 71–78. open access
26. ^ PV Education.org Module Materials
27. ^ a b "Small Photovoltaic Arrays". Research Institute for Sustainable Energy (RISE), Murdoch University. Retrieved 5 February 2010.
28. ^ Key Factors in selecting solar components
29. ^ List of Eligible SB1 Guidelines Compliant Photovoltaic Modules
30. ^ Santbergen, R; R.J.C. van Zolingen (22 October 2007). "The absorption factor of crystalline silicon PV cells: A numerical and experimental study". Solar Energy Materials & Solar Cells.
31. ^ El-Sharkawi, Mohamed A. (2005). Electric energy. CRC Press. pp. 87–88. ISBN 978-0-8493-3078-0.
32. ^ Optimum Tilt of Solar Panels
33. ^ Stand Alone Photovoltaic Lighting Systems
34. ^ Rob W. Andrews and Joshua M. Pearce, The effect of spectral albedo on amorphous silicon and crystalline silicon solar photovoltaic device performance, Solar Energy, 91,233–241 (2013). DOI:10.1016/j.solener.2013.01.030 open access
35. ^ M.P. Brennan, A.L. Abramase, R.W. Andrews, J. M. Pearce, Effects of spectral albedo on solar photovoltaic devices, Solar Energy Materials and Solar Cells, 124, pp. 111-116,(2014). DOI: http://dx.doi.org/10.1016/j.solmat.2014.01.046.
36. ^ "How much energy will my solar cells produce?". Retrieved 2012-05-30.
37. ^ Sahara's solar power potential underlined
38. ^ "Solar Power (Photovoltaic, PV)". Agriculture and Agri-Food Canada. Retrieved 5 February 2010.
39. ^ The Worst Metric in Renewables: 'The Payback Period'. Renewable Energy World (2010-04-19). Retrieved on 2012-10-01.
40. ^ It's payback time for home generation. BBC News (2010-06-22). Retrieved on 2012-04-23.
41. ^ "Solar Panel Comparison Table". Retrieved 2012-10-21.
42. ^ Andresen, Bjarne; R. Stephen Berry (May 1977). "Thermodynamics in finite time. I. The step-Carnot cycle". Physical Review A.
43. ^ Fraunhofer Institute for Solar Energy Systems. "World Record Solar Cell with 44.7% Efficiency". Fraunhofer ISE.
44. ^ "Concentrix Solar: Concentrator Modules". Retrieved 2008-12-03.
45. ^ CPV Solar Cell Reach 27% System Efficiency
46. ^ Kajihara, Atsushi, and A. T. Harakawa. "Model of photovoltaic cell circuits under partial shading." Industrial Technology, 2005. ICIT 2005. IEEE International Conference on. IEEE, 2005.
47. ^ Drif, M., Perez, P. J., Aguilera, J., & Aguilar, J. D. (2008). A new estimation method of irradiance on a partially shaded PV generator in grid-connected photovoltaic systems. Renewable Energy, 33(9), 2048-2056.
48. ^ VENTRE, JERRY AUTOR. Photovoltaic systems engineering. CRC press, 2004.
49. ^ Ursula Eicker, Solar Technologies for Buildings, Wiley 2003, ISBN 0-471-48637-X, page 226
50. ^ H. T. Nguyen and J. M. Pearce, Incorporating Shading Losses in Solar Photovoltaic Potential Assessment at the Municipal Scale, Solar Energy 86(5), pp. 1245–1260 (2012). Source: http://www.academia.edu/1499891/Incorporating_Shading_Losses_in_Solar_Photovoltaic_Potential_Assessment_at_the_Municipal_Scale
51. ^ Z. Dereli, C. Yücedağ and J. M. Pearce, Simple and Low-Cost Method of Planning for Tree Growth and Lifetime Effects on Solar Photovoltaic Systems Performance, Solar Energy, 95, pp.300-307 (2013). Available: http://www.academia.edu/4074627/Simple_and_low-cost_method_of_planning_for_tree_growth_and_lifetime_effects_on_solar_photovoltaic_systems_performance
52. ^ Should you spring clean your solar panels?
53. ^ A Performance Calculator. Rredc.nrel.gov. Retrieved on 2012-04-23.
54. ^ Technological advantages. Mecasolar.com. Retrieved on 2012-04-23.
55. ^ o Al-Mohamad, Ali. "Efficiency improvements of photo-voltaic panels using a Sun-tracking system." Applied Energy 79, no. 3 (2004): 345-354.
56. ^ Reflective Coating Silicon Solar Cells Boosts Absorption Over 96 Percent. Scientificblogging.com (2008-11-03). Retrieved on 2012-04-23.
57. ^ Beginners' Guide to Solar Trackers: How to Increase Output for Your Home Solar Panel System
58. ^ Insolation Levels (Europe)
59. ^ 10 years Average Insolation Data
60. ^ Utility Scale Solar Power Plants
61. ^ Should You Install a Solar Tracker?
62. ^ Grid-Tied Inverter Safety. Homepower.com. Retrieved on 2012-04-23.
63. ^ Trend watch: Microinverters invade solar
64. ^ Services and Solutions for Photovoltaic Systems
65. ^
66. ^ EDN.com Solar power anti-islanding and control, 7 August 2012
67. ^ Dan Fink, www.homepower.com Charge Controller Buyer's Guide, January 2012
68. ^ Residential Photovoltaic Metering and Interconnection Study
69. ^ Integrating Variable Renewable Energy in Electric Power Markets
70. ^ Smart PV Inverter Benefits for Utilities
71. ^ Enphase Technology
73. ^ Pearce, Joshua. M; Adegboyega Babasola; Rob Andrews (2012). "Open Solar Photovoltaic Systems Optimization". Proceedings of the 16th Annual National Collegiate Inventors and Innovators Alliance Conference (NCIIA): 1–7.
74. ^ Open Solar Photovoltaic Systems Optimization
75. ^ Fraunhofer Center for Sustainable Energy Systems Announces Opening of Albuquerque Outdoor Solar Test Field
76. ^ CSI—Metering and Performance Monitoring
77. ^ Solar Energy
78. ^ SolarGuard
79. ^ 'Pay bill for 4 months, get power for 25 years'
80. ^ "Pumping Water with Sunshine". Retrieved 7 January 2014.
81. ^ "Solar Well Pumps". Retrieved 7 January 2014.
82. ^ People building their own solar systems from kits. Greenplanet4energy.com. Retrieved on 2012-04-23.
83. ^ Example of diy PV system with pictures. Instructables.com (2007-11-05). Retrieved on 2012-04-23.
84. ^ Graham, Michael. (2005-10-15) Low-cost PV solar kit preferred by diy-communities. Treehugger.com. Retrieved on 2012-04-23.
85. ^ Ken Darrow and Mike Saxenian Appropriate Technology Sourcebook at the Wayback Machine (archived September 22, 2010). villageearth.org
86. ^ "Alternative Energy Development: Michigan will be Nation’s Leader in Alternative Energy Technology, Jobs". State of Michigan, Office Of The Governor. Retrieved February 22, 2012.
87. ^ Energy
88. ^ Solar Lamps
89. ^ PV resources website, Hybrid power station accessed 10 Feb 08
90. ^ Daten und Fakten at the Wayback Machine (archived July 19, 2011). Pellworm island website (in German)
91. ^ Darul’a, Ivan; Stefan Marko (2007). "Large scale integration of renewable electricity production into the grids" (PDF). Journal of Eelectrical Engineering 58 (1): 58–60. ISSN 1335-3632. Retrieved 2008-02-10.
92. ^ J. M. Pearce (2009). "Expanding Photovoltaic Penetration with Residential Distributed Generation from Hybrid Solar Photovoltaic + Combined Heat and Power Systems". Energy 34: 1947–1954. doi:10.1016/j.energy.2009.08.012.
93. ^ P. Derewonko and J.M. Pearce, “Optimizing Design of Household Scale Hybrid Solar Photovoltaic + Combined Heat and Power Systems for Ontario”, Photovoltaic Specialists Conference (PVSC), 2009 34th IEEE, pp.1274–1279, 7–12 June 2009.
94. ^ M. Mostofi, A. H. Nosrat, and J. M. Pearce, “Institutional-Scale Operational Symbiosis of Photovoltaic and Cogeneration Energy Systems” International Journal of Environmental Science and Technology 8(1), pp. 31–44, 2011. Available open access: [3]
95. ^ SolarServer.com Kyocera, partners announce construction of the world's largest floating solar PV Plant in Hyogo prefecture, Japan 4 September 2014
96. ^ EnergyWorld.com Running Out of Precious Land? Floating Solar PV Systems May Be a Solution 7 novermber 2013
97. ^ Innovative Electrical Concepts at the Wayback Machine (archived March 18, 2009). International Energy Agency (2001)
98. ^ site7. Ecotourisme.ch. Retrieved on 2012-04-23.
99. ^ Average turn-key prices for roof-top PV systems up to 100 kWp. Sources: for data since 2009 photovoltaik-guide.de, pv-preisindex , displaying for each year average price of month of January. Data source for previous years (2006-2008), see Bundesverband Solarwirtschaft e.V. (BSW-Solar), September 2009, page 4, quarterly figures from EUPD-Research.
100. ^
101. ^ "Rooftop size for US and Japan is 10kW or less, while for Germany it is 100kW or less. Exchange rate of 0.74 euro-cents for one US\$ used for conversion.p"
102. ^ John Quiggin (January 3, 2012). "The End of the Nuclear Renaissance |". National Interest.
103. ^ "Solar photovoltaics: Competing in the energy sector". European Photovoltaic Industry Association (EPIA). 2011-09-01. Retrieved 2014-04-05.
104. ^ A Comparison of PV Technologies
105. ^ $p = \frac{I\cdot (1+i)+\sum_{t=0}^T \frac{I \cdot b}{(1+i)^t}}{\sum_{t=0}^T\frac{E\cdot (1-v)^t}{(1+i)^t}}$
106. ^ What is Levelized Cost?
107. ^ IRENA: Renewable Power Generation Costs (German Photovoltaic System Costs: USD 2200/kW; Page 9)
108. ^ PV operation and maintenance costs. (PDF) . Retrieved on 2012-04-23.
109. ^ Solar PV warranties
110. ^ Understanding Solar Panel Warrantees
111. ^ Jasenek, J; U. Rau (17 April 2001). "Defect generation in Cu(In,Ga)Se2 heterojunction solar cells by high-energy electron and proton irradiation". Journal of Applied Physics 90 (650): 9. doi:10.1063/1.1379348.
112. ^ Brooks, Bill (February–March 2011). "The Bakersfield Fire: A Lesson in Ground-Fault Protection". Solar Pro (4.2).
113. ^ Regan Arndt and Dr. Ing Robert Puto. Basic Understanding of IEC Standard Testing For Photovoltaic Panels. Available: http://tuvamerica.com/services/photovoltaics/ArticleBasicUnderstandingPV.pdf
114. ^ a b Solar Power World
115. ^ Solar Panels. Planning Portal. Retrieved on 2013-07-17.
116. ^ "Requirements for Solar Installations". bootsontheroof.com. 2011. Retrieved March 31, 2011.
117. ^ "California Solar Rights Act". Retrieved February 25, 2012.
118. ^ Hunt, Tam. "Spain and Portugal Lead the Way on Renewable Energy Transformation". Renewable Energy World.
119. ^ Phillips Erb, Kelly (2013-08-19). "Out Of Ideas And In Debt, Spain Sets Sights On Taxing The Sun". Forbes. Retrieved 10/4/13.