# Solar thermal energy

(Redirected from Solar thermal)
Solar thermal system for water heating in Santorini, Greece.

Solar thermal energy (STE) is a technology for harnessing solar energy for thermal energy (heat). Solar thermal collectors are classified by the United States Energy Information Administration as low-, medium-, or high-temperature collectors. Low-temperature collectors are flat plates generally used to heat swimming pools. Medium-temperature collectors are also usually flat plates but are used for heating water or air for residential and commercial use. High-temperature collectors concentrate sunlight using mirrors or lenses and are generally used for electric power production. STE is different from and much more efficient than[1][2][3] photovoltaics, which converts solar energy directly into electricity. While existing generation facilities provide only 600 megawatts of solar thermal power worldwide in October 2009, [note 1] plants for an additional 400 megawatts are under construction and development is underway for concentrated solar power projects totalling 14,000 megawatts.[4]

## Low-temperature solar heating and cooling systems

MIT's Solar House #1 built in 1939 used Seasonal thermal energy storage (STES) for year round heating.

Systems for utilizing low-temperature solar thermal energy include means for heat collection; usually heat storage, either short-term or interseasonal; and distribution within a structure or a district heating network. In some cases more than one of these functions is inherent to a single feature of the system (e.g. some kinds of solar collectors also store heat). Some systems are passive, others are active (requiring other external energy to function).

Heating is the most obvious application, but solar cooling can be achieved for a building or district cooling network by using a heat-driven absorption or adsorption chiller (heat pump). There is a productive coincidence that the greater the driving heat from insolation, the greater the cooling output. In 1878, Auguste Mouchout pioneered solar cooling by making ice using a solar steam engine attached to a refrigeration device.[5]

In the United States, heating, ventilation, and air conditioning (HVAC) systems account for over 25 percent (4.75 EJ) of the energy used in commercial buildings and nearly half (10.1 EJ) of the energy used in residential buildings.[6][7] Solar heating, cooling, and ventilation technologies can be used to offset a portion of this energy.

In Europe, since the mid-1990s about 125 large solar-thermal district heating plants have been constructed, each with over 500 m2 (5400 ft2) of solar collectors. The largest are about 10,000 m2, with capacities of 7 MW-thermal and solar heat costs around 4 Eurocents/kWh without subsidies.[8] 40 of them have nominal capacities of 1 MW-thermal or more. The Solar District Heating program (SDH) has participation from 14 European Nations and the European Commission, and is working toward technical and market development, and holds annual conferences.[9]

### Low-temperature collectors

Glazed Solar Collectors are designed primarily for space heating and they recirculate building air through a solar air panel where the air is heated and then directed back into the building. These solar space heating systems require at least two penetrations into the building and only perform when the air in the solar collector is warmer than the building room temperature. Most glazed collectors are used in the residential sector.

Unglazed, "transpired" air collector

Unglazed Solar Collectors are primarily used to pre-heat make-up ventilation air in commercial, industrial and institutional buildings with a high ventilation load. They turn building walls or sections of walls into low cost, high performance, unglazed solar collectors. Also called, "transpired solar panels", they employ a painted perforated metal solar heat absorber that also serves as the exterior wall surface of the building. Heat conducts from the absorber surface to the thermal boundary layer of air 1 mm thick on the outside of the absorber and to air that passes behind the absorber. The boundary layer of air is drawn into a nearby perforation before the heat can escape by convection to the outside air. The heated air is then drawn from behind the absorber plate into the building's ventilation system.

A Trombe wall is a passive solar heating and ventilation system consisting of an air channel sandwiched between a window and a sun-facing thermal mass. During the ventilation cycle, sunlight stores heat in the thermal mass and warms the air channel causing circulation through vents at the top and bottom of the wall. During the heating cycle the Trombe wall radiates stored heat.[10]

Solar roof ponds are unique solar heating and cooling systems developed by Harold Hay in the 1960s. A basic system consists of a roof-mounted water bladder with a movable insulating cover. This system can control heat exchange between interior and exterior environments by covering and uncovering the bladder between night and day. When heating is a concern the bladder is uncovered during the day allowing sunlight to warm the water bladder and store heat for evening use. When cooling is a concern the covered bladder draws heat from the building's interior during the day and is uncovered at night to radiate heat to the cooler atmosphere. The Skytherm house in Atascadero, California uses a prototype roof pond for heating and cooling.[11]

Solar space heating with solar air heat collectors is more popular in the USA and Canada than heating with solar liquid collectors since most buildings already have a ventilation system for heating and cooling. The two main types of solar air panels are glazed and unglazed.

Of the 21,000,000 square feet (2,000,000 m2) of solar thermal collectors produced in the United States in 2007, 16,000,000 square feet (1,500,000 m2) were of the low-temperature variety.[12] Low-temperature collectors are generally installed to heat swimming pools, although they can also be used for space heating. Collectors can use air or water as the medium to transfer the heat to their destination.

### Heat storage in low-temperature solar thermal systems

Interseasonal storage. Solar heat (or heat from other sources) can be effectively stored between opposing seasons aquifers, underground geological strata, large specially constructed pits, and large tanks that are insulated and covered with earth. See the section below: Heat Storage for Space Heating.

Short-term storage. Thermal mass materials store solar energy during the day and release this energy during cooler periods. Common thermal mass materials include stone, concrete, and water. The proportion and placement of thermal mass should consider several factors such as climate, daylighting, and shading conditions. When properly incorporated, thermal mass can passively maintain comfortable temperatures while reducing energy consumption.

### Solar-driven cooling

Worldwide, by 2011 there were about 750 cooling systems with solar-driven heat pumps, and annual market growth was 40 to 70 percent over the prior seven years. It is a niche market because the economics are challenging, with the annual number of cooling hours a limiting factor. Respectively, the annual cooling hours are roughly 1000 in the Mediterranean, 2500 in Southeast Asia, and only 50 to 200 in Central Europe. However, systeme construction costs dropped about 50 percent between 2007 and 2011. The International Energy Agency (IEA) Solar Heating and Cooling program (IEA-SHC) task groups working on further development of the technologies involved. [13] The International Energy Agency (IEA) Solar Heating and Cooling program (IEA-SHC) task groups working on further development of the technologies involved.[14]

### Solar heat-driven ventilation

A solar chimney (or thermal chimney) is a passive solar ventilation system composed of a hollow thermal mass connecting the interior and exterior of a building. As the chimney warms, the air inside is heated causing an updraft that pulls air through the building. These systems have been in use since Roman times and remain common in the Middle East.

### Process heat

Solar Evaporation Ponds in the Atacama Desert.

Solar process heating systems are designed to provide large quantities of hot water or space heating for nonresidential buildings.[15]

Evaporation ponds are shallow ponds that concentrate dissolved solids through evaporation. The use of evaporation ponds to obtain salt from sea water is one of the oldest applications of solar energy. Modern uses include concentrating brine solutions used in leach mining and removing dissolved solids from waste streams. Altogether, evaporation ponds represent one of the largest commercial applications of solar energy in use today.[16]

Unglazed transpired collectors (UTC) are perforated sun-facing walls used for preheating ventilation air. UTCs can raise the incoming air temperature up to 22 °C and deliver outlet temperatures of 45-60 °C. The short payback period of transpired collectors (3 to 12 years) make them a more cost-effective alternative to glazed collection systems. As of 2009, over 1500 systems with a combined collector area of 300,000 m² had been installed worldwide. Representatives include an 860 m² collector in Costa Rica used for drying coffee beans and a 1300 m² collector in Coimbatore, India used for drying marigolds.[17][18]

A food processing facility in Modesto, California uses parabolic troughs to produce steam used in the manufacturing process. The 5,000 m² collector area is expected to provide 15 TJ per year.[19]

## Medium-temperature collectors

These collectors could be used to produce approximately 50% and more of the hot water needed for residential and commercial use in the United States.[20] In the United States, a typical system costs \$4000–\$6000 retail (\$1400 to \$2200 wholesale for the materials) and 30% of the system qualifies for a federal tax credit + additional state credit exists in about half of the states. Labor for a simple open loop system in southern climates can take 3–5 hours for the installation and 4–6 hours in Northern areas. Northern system require more collector area and more complex plumbing to protect the collector from freezing. With this incentive, the payback time for a typical household is four to nine years, depending on the state. Similar subsidies exist in parts of Europe. A crew of one solar plumber and two assistants with minimal training can install a system per day. Thermosiphon installation have negligible maintenance costs (costs rise if antifreeze and mains power are used for circulation) and in the US reduces a households' operating costs by \$6 per person per month. Solar water heating can reduce CO2 emissions of a family of four by 1 ton/year (if replacing natural gas) or 3 ton/year (if replacing electricity).[21] Medium-temperature installations can use any of several designs: common designs are pressurized glycol, drain back, batch systems and newer low pressure freeze tolerant systems using polymer pipes containing water with photovoltaic pumping. European and International standards are being reviewed to accommodate innovations in design and operation of medium temperature collectors. Operational innovations include "permanently wetted collector" operation. This innovation reduces or even eliminates the occurrence of no-flow high temperature stresses called stagnation which would otherwise reduce the life expectancy of collectors.

### Solar drying

Solar thermal energy can be useful for drying wood for construction and wood fuels such as wood chips for combustion. Solar is also used for food products such as fruits, grains, and fish. Crop drying by solar means is environmentally friendly as well as cost effective while improving the quality. The less money it takes to make a product, the less it can be sold for, pleasing both the buyers and the sellers. Technologies in solar drying include ultra low cost pumped transpired plate air collectors based on black fabrics. Solar thermal energy is helpful in the process of drying products such as wood chips and other forms of biomass by raising the temperature while allowing air to pass through and get rid of the moisture.[22]

### Cooking

The Solar Bowl above the Solar Kitchen in Auroville, India concentrates sunlight on a movable receiver to produce steam for cooking.

Solar cookers use sunlight for cooking, drying and pasteurization. Solar cooking offsets fuel costs, reduces demand for fuel or firewood, and improves air quality by reducing or removing a source of smoke.

The simplest type of solar cooker is the box cooker first built by Horace de Saussure in 1767. A basic box cooker consists of an insulated container with a transparent lid. These cookers can be used effectively with partially overcast skies and will typically reach temperatures of 50–100 °C.[23][24]

Concentrating solar cookers use reflectors to concentrate solar energy onto a cooking container. The most common reflector geometries are flat plate, disc and parabolic trough type. These designs cook faster and at higher temperatures (up to 350 °C) but require direct light to function properly.

The Solar Kitchen in Auroville, India uses a unique concentrating technology known as the solar bowl. Contrary to conventional tracking reflector/fixed receiver systems, the solar bowl uses a fixed spherical reflector with a receiver which tracks the focus of light as the Sun moves across the sky. The solar bowl's receiver reaches temperature of 150 °C that is used to produce steam that helps cook 2,000 daily meals.[25]

Many other solar kitchens in India use another unique concentrating technology known as the Scheffler reflector. This technology was first developed by Wolfgang Scheffler in 1986. A Scheffler reflector is a parabolic dish that uses single axis tracking to follow the Sun's daily course. These reflectors have a flexible reflective surface that is able to change its curvature to adjust to seasonal variations in the incident angle of sunlight. Scheffler reflectors have the advantage of having a fixed focal point which improves the ease of cooking and are able to reach temperatures of 450-650 °C.[26] Built in 1999, the world's largest Scheffler reflector system in Abu Road, Rajasthan India is capable of cooking up to 35,000 meals a day.[27] By early 2008, over 2000 large cookers of the Scheffler design had been built worldwide.

### Distillation

Solar stills can be used to make drinking water in areas where clean water is not common. Solar distillation is necessary in these situations to provide people with purified water. Solar energy heats up the water in the still. The water then evaporates and condenses on the bottom of the covering glass.[22]

## High-temperature collectors

The solar furnace at Odeillo in the French Pyrenees-Orientales can reach temperatures up to 3,800 degrees Celsius.
Concentrated solar power plant using parabolic trough design.

Where temperatures below about 95 °C are sufficient, as for space heating, flat-plate collectors of the nonconcentrating type are generally used. Because of the relatively high heat losses through the glazing, flat plate collectors will not reach temperatures much above 200 °C even when the heat transfer fluid is stagnant. Such temperatures are too low for efficient conversion to electricity.

The efficiency of heat engines increases with the temperature of the heat source. To achieve this in solar thermal energy plants, solar radiation is concentrated by mirrors or lenses to obtain higher temperatures – a technique called Concentrated Solar Power (CSP). The practical effect of high efficiencies is to reduce the plant's collector size and total land use per unit power generated, reducing the environmental impacts of a power plant as well as its expense.

As the temperature increases, different forms of conversion become practical. Up to 600 °C, steam turbines, standard technology, have an efficiency up to 41%. Above 600 °C, gas turbines can be more efficient. Higher temperatures are problematic because different materials and techniques are needed. One proposal for very high temperatures is to use liquid fluoride salts operating between 700 °C to 800 °C, using multi-stage turbine systems to achieve 50% or more thermal efficiencies.[28] The higher operating temperatures permit the plant to use higher-temperature dry heat exchangers for its thermal exhaust, reducing the plant's water use – critical in the deserts where large solar plants are practical. High temperatures also make heat storage more efficient, because more watt-hours are stored per unit of fluid.

Since the CSP plant generates heat first of all, it can store the heat before conversion to electricity. With current technology, storage of heat is much cheaper and more efficient than storage of electricity. In this way, the CSP plant can produce electricity day and night. If the CSP site has predictable solar radiation, then the CSP plant becomes a reliable power plant. Reliability can further be improved by installing a back-up combustion system. The back-up system can use most of the CSP plant, which decreases the cost of the back-up system.

CSP facilities utilize high electrical conductivity materials, such as copper, in field power cables, grounding networks, and motors for tracking and pumping fluids, as well as in the main generator and high voltage transformers. (See: Copper in concentrating solar thermal power facilities.)

With reliability, unused desert, no pollution, and no fuel costs, the obstacles for large deployment for CSP are cost, aesthetics, land use and similar factors for the necessary connecting high tension lines. Although only a small percentage of the desert is necessary to meet global electricity demand, still a large area must be covered with mirrors or lenses to obtain a significant amount of energy. An important way to decrease cost is the use of a simple design.

### System designs

During the day the sun has different positions. For low concentration systems (and low temperatures) tracking can be avoided (or limited to a few positions per year) if nonimaging optics are used.[29] For higher concentrations, however, if the mirrors or lenses do not move, then the focus of the mirrors or lenses changes (but also in these cases nonimaging optics provides the widest acceptance angles for a given concentration). Therefore it seems unavoidable that there needs to be a tracking system that follows the position of the sun (for solar photovoltaic a solar tracker is only optional). The tracking system increases the cost and complexity. With this in mind, different designs can be distinguished in how they concentrate the light and track the position of the sun.

#### Parabolic trough designs

Sketch of a parabolic trough design. A change of position of the sun parallel to the receiver does not require adjustment of the mirrors.

Parabolic trough power plants use a curved, mirrored trough which reflects the direct solar radiation onto a glass tube containing a fluid (also called a receiver, absorber or collector) running the length of the trough, positioned at the focal point of the reflectors. The trough is parabolic along one axis and linear in the orthogonal axis. For change of the daily position of the sun perpendicular to the receiver, the trough tilts east to west so that the direct radiation remains focused on the receiver. However, seasonal changes in the in angle of sunlight parallel to the trough does not require adjustment of the mirrors, since the light is simply concentrated elsewhere on the receiver. Thus the trough design does not require tracking on a second axis.

The receiver may be enclosed in a glass vacuum chamber. The vacuum significantly reduces convective heat loss.

A fluid (also called heat transfer fluid) passes through the receiver and becomes very hot. Common fluids are synthetic oil, molten salt and pressurized steam. The fluid containing the heat is transported to a heat engine where about a third of the heat is converted to electricity.

Andasol 1 in Guadix, Spain uses the Parabolic Trough design which consists of long parallel rows of modular solar collectors. Tracking the sun from East to West by rotation on one axis, the high precision reflector panels concentrate the solar radiation coming directly from the sun onto an absorber pipe located along the focal line of the collector. A heat transfer medium, a synthetic oil like in car engines, is circulated through the absorber pipes at temperatures up to 400 °C and generates live steam to drive the steam turbine generator of a conventional power block.

Full-scale parabolic trough systems consist of many such troughs laid out in parallel over a large area of land. Since 1985 a solar thermal system using this principle has been in full operation in California in the United States. It is called the SEGS system.[30] Other CSP designs lack this kind of long experience and therefore it can currently be said that the parabolic trough design is the most thoroughly proven CSP technology.

The Solar Energy Generating System (SEGS) is a collection of nine plants with a total capacity of 350 MW. It is currently the largest operational solar system (both thermal and non-thermal). A newer plant is Nevada Solar One plant with a capacity of 64 MW. Under construction are Andasol 1 and Andasol 2 in Spain with each site having a capacity of 50 MW. Note however, that those plants have heat storage which requires a larger field of solar collectors relative to the size of the steam turbine-generator to store heat and send heat to the steam turbine at the same time. Heat storage enables better utilization of the steam turbine. With day and some nighttime operation of the steam-turbine Andasol 1 at 50 MW peak capacity produces more energy than Nevada Solar One at 64 MW peak capacity, due to the former plant's thermal energy storage system and larger solar field.

553 MW new capacity is proposed in Mojave Solar Park, California.[31] Furthermore, 59 MW hybrid plant with heat storage is proposed near Barstow, California.[32] Near Kuraymat in Egypt, some 40 MW steam is used as input for a gas powered plant.[33][34] Finally, 25 MW steam input for a gas power plant in Hassi R'mel, Algeria.[35] The Government of India and its federation have embarked on a major initiative; The Jawaharlal Nehru National Solar Mission (also known as the National Solar Mission) to address India's energy security challenges. The first phase (up to 2013) will focus on capturing of the low hanging options in solar thermal specifically in Jaisalmer in the Western state of Rajasthan. Shriram EPC, one of the major EPC companies in India and a part of the Shriram Group has embarked on a 50 MW solar thermal plant in Jaisalmer for Corporate Ispat and Alloys Ltd. which is to be commissioned by April 2013. Several other projects are also in the works.

#### Power tower designs

Solar Two. Flat mirrors focus the light on the top of the tower. The white surfaces below the receiver are used for calibrating the mirror positions.

Power towers (also known as 'central tower' power plants or 'heliostat' power plants) capture and focus the sun's thermal energy with thousands of tracking mirrors (called heliostats) in roughly a two square mile field. A tower resides in the center of the heliostat field. The heliostats focus concentrated sunlight on a receiver which sits on top of the tower. Within the receiver the concentrated sunlight heats molten salt to over 1,000 °F (538 °C). The heated molten salt then flows into a thermal storage tank where it is stored, maintaining 98% thermal efficiency, and eventually pumped to a steam generator. The steam drives a standard turbine to generate electricity. This process, also known as the "Rankine cycle" is similar to a standard coal-fired power plant, except it is fueled by clean and free solar energy.

The advantage of this design above the parabolic trough design is the higher temperature. Thermal energy at higher temperatures can be converted to electricity more efficiently and can be more cheaply stored for later use. Furthermore, there is less need to flatten the ground area. In principle a power tower can be built on the side of a hill. Mirrors can be flat and plumbing is concentrated in the tower. The disadvantage is that each mirror must have its own dual-axis control, while in the parabolic trough design single axis tracking can be shared for a large array of mirrors.

In June 2008, eSolar,[36] a Pasadena, CA-based company founded by Idealab CEO Bill Gross with funding from Google,[37] announced a Power Purchase Agreement (PPA) with the utility Southern California Edison to produce 245 megawatts of power.[38] Also, in February 2009, eSolar announced it had licensed its technology to two development partners, the Princeton, N.J.-based NRG Energy, Inc., and the India-based ACME Group. In the deal with NRG, the companies announced plans to jointly build 500 megawatts of concentrating solar thermal plants throughout the United States. The target goal for the ACME Group was nearly double; ACME plans to start construction on its first eSolar power plant this year, and will build a total of 1 gigawatt over the next 10 years.[39]

eSolar's proprietary sun-tracking software coordinates the movement of 24,000 1 meter-square mirrors per 1 tower using optical sensors[40] to adjust and calibrate the mirrors in real time. This allows for a high density of reflective material which enables the development of modular concentrating solar thermal (CSP) power plants in 46 megawatt (MW) units on approximately π square mile parcels of land, resulting in a land-to-power ratio of 44 acres (180,000 m2) per 1 megawatt.

BrightSource Energy entered into a series of power purchase agreements with Pacific Gas and Electric Company in March 2008 for up to 900 MW of electricity, the largest solar power commitment ever made by a utility.[41] BrightSource is currently developing a number of solar power plants in Southern California, with construction of the first plant planned to start in 2009.

In June 2008, BrightSource Energy dedicated its 4-6 MW [42] Solar Energy Development Center (SEDC) in Israel's Negev Desert. The site, located in the Rotem Industrial Park, features more than 1,600 heliostats that track the sun and reflect light onto a 60 meter-high tower. The concentrated energy is then used to heat a boiler atop the tower to 550 degrees Celsius, generating superheated steam.[43]

A working tower power plant is PS10 in Spain with a capacity of 11 MW.

The 15 MW Solar Tres plant with heat storage is under construction in Spain. In South Africa, a 100 MW solar power plant is planned with 4000 to 5000 heliostat mirrors, each having an area of 140 m².[44] A 10 MW power plant in Cloncurry, Australia (with purified graphite as heat storage located on the tower directly by the receiver).[45]

Morocco is building five solar thermal power plants around Ouasarzate. The sites will produce about 2000 MW by 2012. Over ten thousand hectors of land will be needed to sustain all of the sites.[46]

Out of commission are the 10 MW Solar One (later redeveloped and made into Solar Two) and the 2 MW Themis plants.

A cost/performance comparison between power tower and parabolic trough concentrators was made by the NREL which estimated that by 2020 electricity could be produced from power towers for 5.47 ¢/kWh and for 6.21 ¢/kWh from parabolic troughs. The capacity factor for power towers was estimated to be 72.9% and 56.2% for parabolic troughs.[47] There is some hope that the development of cheap, durable, mass producible heliostat power plant components could bring this cost down.[48]

#### Dish designs

A parabolic solar dish concentrating the sun's rays on the heating element of a Stirling engine. The entire unit acts as a solar tracker.

CSP-Stirling is known to have the highest efficiency of all solar technologies around 30% compared to solar PV approximately 15%,and is predicted to be able to produce the cheapest energy among all renewable energy sources in high scale production and hot areas, semi deserts etc. A dish Stirling system uses a large, reflective, parabolic dish (similar in shape to satellite television dish). It focuses all the sunlight that strikes the dish up onto a single point above the dish, where a receiver captures the heat and transforms it into a useful form. Typically the dish is coupled with a Stirling engine in a Dish-Stirling System, but also sometimes a steam engine is used.[49] These create rotational kinetic energy that can be converted to electricity using an electric generator.[50]

The advantage of a dish system is that it can achieve much higher temperatures due to the higher concentration of light (as in tower designs). Higher temperatures lead to better conversion to electricity and the dish system is very efficient on this point. However, there are also some disadvantages. Heat to electricity conversion requires moving parts and that results in maintenance. In general, a centralized approach for this conversion is better than the decentralized concept in the dish design. Second, the (heavy) engine is part of the moving structure, which requires a rigid frame and strong tracking system. Furthermore, parabolic mirrors are used instead of flat mirrors and tracking must be dual-axis.

In 2005 Southern California Edison announced an agreement to purchase solar powered Stirling engines from Stirling Energy Systems over a twenty-year period and in quantities (20,000 units) sufficient to generate 500 megawatts of electricity. In January 2010, Stirling Energy Systems and Tessera Solar commissioned the first demonstration 1.5-megawatt power plant ("Maricopa Solar") using Stirling technology in Peoria, Arizona.[51] At the beginning of 2011 Stirling Energy's development arm, Tessera Solar, sold off its two large projects, the 709 MW Imperial project and the 850 MW Calico project to AES Solar and K.Road, respectively,[52][53] and in the fall of 2011 Stirling Energy Systems applied for Chapter 7 bankruptcy due to competition from low cost photovoltaics, Later confirmed to be incorrect when Chinese subsidies pushed down the prices of PV to an unrealistic level.In 2012 the Maricopa plant and Teserra Solar was bought by United Sun Systems As the technology is confirmed to be the cheapest solar energy, in large scale, the installation in maricopa was taken down and partly moved to China to start building CSP-Stirling in utility scale in accordance to Chinese Governmental orders. .[54]

#### Fresnel reflectors

Fresnel reflector

A linear Fresnel reflector power plant uses a series of long, narrow, shallow-curvature (or even flat) mirrors to focus light onto one or more linear receivers positioned above the mirrors. On top of the receiver a small parabolic mirror can be attached for further focusing the light. These systems aim to offer lower overall costs by sharing a receiver between several mirrors (as compared with trough and dish concepts), while still using the simple line-focus geometry with one axis for tracking. This is similar to the trough design (and different from central towers and dishes with dual-axis). The receiver is stationary and so fluid couplings are not required (as in troughs and dishes). The mirrors also do not need to support the receiver, so they are structurally simpler. When suitable aiming strategies are used (mirrors aimed at different receivers at different times of day), this can allow a denser packing of mirrors on available land area.

Recent prototypes of these types of systems have been built in Australia (CLFR[55]) and by Solarmundo in Belgium.

The Solarmundo research and development project, with its pilot plant at Liège, was closed down after successful proof of concept of the Linear Fresnel technology. Subsequently, Solar Power Group GmbH (SPG), based in Munich, Germany, was founded by some Solarmundo team members. A Fresnel-based prototype with direct steam generation was built by SPG in conjunction with the German Aerospace Center (DLR).[56]

Based on the Australian prototype, a 177 MW plant had been proposed near San Luis Obispo in California and would be built by Ausra.[57] But Ausra sold its planned California solar farm to First Solar. First Solar (a manufacturer of thin-film photovoltaic solar cells) will not build the Carrizo project, and the deal has resulted in the cancellation of Ausra’s contract to provide 177 megawatts to P.G.& E.[58] Small capacity plants are an enormous economical challenge with conventional parabolic trough and drive design – few companies build such small projects. There are plans for SHP Europe, former Ausra subsidiary, to build a 6.5 MW combined cycle plant in Portugal. The German company SK Energy GmbH has plans to build several small 1-3 MW plants in Southern Europe (esp. in Spain) using Fresnel mirror and steam drive technology (Press Release).[59]

In May 2008, the German Solar Power Group GmbH and the Spanish Laer S.L. agreed the joint execution of a solar thermal power plant in central Spain. This will be the first commercial solar thermal power plant in Spain based on the Fresnel collector technology of the Solar Power Group. The planned size of the power plant will be 10 MW a solar thermal collector field with a fossil co-firing unit as backup system. The start of constructions is planned for 2009. The project is located in Gotarrendura, a small renewable energy pioneering village, about 100 km northwest of Madrid, Spain.

A Multi-Tower Solar Array (MTSA) concept, that uses a point-focus Fresnel reflector idea, has also been developed,[60] but has not yet been prototyped.

Since March 2009, the Fresnel solar power plant Puerto Errado 1 (PE 1) of the German company Novatec Solar is in commercial operation in southern Spain . The solar thermal power plant is based on linear Fresnel collector technology and has an electrical capacity of 1.4 MW. Beside a conventional power block, PE 1 comprises a solar boiler with mirror surface of around 18,000m². The steam is generated by concentrating direct solar irradiation onto a linear receiver which is 7.40m above the ground. An absorber tube is positioned in the focal line of the mirror field in which water is evaporated directly into saturated steam at 270 °C and at a pressure of 55 bar by the concentrated solar energy. Since September 2011, due to a new receiver design developed by Novatec Solar, superheated steam with temperatures above 500°C can be generated.

The 30 MW solar thermal power plant Puerto Errado 2 (PE2) is a scale up of PE 1 and also based on the Fresnel collector technology developed by the German company Novatec Solar. It comprises a mirror surface of 302,000m² and is in operation since August 2012. The plant is located in the region of Murcia. Five Swiss utilities (EBL, IWB, Ekz, ewz, ewb) are the owners of the world's largest Fresnel CSP power station.

#### Linear Fresnel reflector technologies

Fresnel solar power plant PE 1 in southern Spain

Rival single axis tracking technologies include the relatively new linear Fresnel reflector (LFR) and compact-LFR (CLFR) technologies. The LFR differs from that of the parabolic trough in that the absorber is fixed in space above the mirror field. Also, the reflector is composed of many low row segments, which focus collectively on an elevated long tower receiver running parallel to the reflector rotational axis.[61]

This system offers a lower cost solution as the absorber row is shared among several rows of mirrors. However, one fundamental difficulty with the LFR technology is the avoidance of shading of incoming solar radiation and blocking of reflected solar radiation by adjacent reflectors. Blocking and shading can be reduced by using absorber towers elevated higher or by increasing the absorber size, which allows increased spacing between reflectors remote from the absorber. Both these solutions increase costs, as larger ground usage is required.

The CLFR offers an alternate solution to the LFR problem. The classic LFR has only one linear absorber on a single linear tower. This prohibits any option of the direction of orientation of a given reflector. Since this technology would be introduced in a large field, one can assume that there will be many linear absorbers in the system. Therefore, if the linear absorbers are close enough, individual reflectors will have the option of directing reflected solar radiation to at least two absorbers. This additional factor gives potential for more densely packed arrays, since patterns of alternative reflector inclination can be set up such that closely packed reflectors can be positioned without shading and blocking.[62]

CLFR power plants offer reduced costs in all elements of the solar array.[62] These reduced costs encourage the advancement of this technology. Features that enhance the cost effectiveness of this system compared to that of the parabolic trough technology include minimized structural costs, minimized parasitic pumping losses, and low maintenance. Minimized structural costs are attributed to the use of flat or elastically curved glass reflectors instead of costly sagged glass reflectors are mounted close to the ground. Also, the heat transfer loop is separated from the reflector field, avoiding the cost of flexible high pressure lines required in trough systems. Minimized parasitic pumping losses are due to the use of water for the heat transfer fluid with passive direct boiling. The use of glass-evacuated tubes ensures low radiative losses and is inexpensive. Studies of existing CLFR plants have been shown to deliver tracked beam to electricity efficiency of 19% on an annual basis as a preheater.[61]

#### Fresnel lenses

Prototypes of Fresnel lens concentrators have been produced for the collection of thermal energy by International Automated Systems.[63] No full-scale thermal systems using Fresnel lenses are known to be in operation, although products incorporating Fresnel lenses in conjunction with photovoltaic cells are already available.[64]

The advantage of this design is that lenses are cheaper than mirrors. Furthermore, if a material is chosen that has some flexibility, then a less rigid frame is required to withstand wind load. A new concept of a lightweight, 'non-disruptive' solar concentrator technology using asymmetric Fresnel lenses that occupies minimal ground surface area and allows for large amounts of concentrated solar energy per concentrator is seen in the 'Desert Blooms' [65] project, though a prototype has yet to be made.

#### MicroCSP

"MicroCSP"[66][67] references solar thermal technologies in which concentrating solar power (CSP) collectors are based on the designs used in traditional Concentrating Solar Power systems found in the Mojave Desert[68] but are smaller in collector size, lighter and operate at lower thermal temperatures usually below 315 °C (600 °F). These systems are designed for modular field or rooftop installation where they are easy to protect from high winds, snow and humid deployments.[69] Solar manufacturer Sopogy completed construction on a 1 MW CSP plant at the Natural Energy Laboratory of Hawaii.[70]

MicroCSP is used for community-sized power plants (1 MW to 50 MW), for industrial, agricultural and manufacturing 'process heat' applications, and when large amounts of hot water are needed, such as resort swimming pools, water parks, large laundry facilities, sterilization, distillation and other such uses.

#### Enclosed parabolic trough

The enclosed parabolic trough solar thermal system encapsulates the components within a greenhouse-like glasshouse. The glasshouse protects the components from the elements that can negatively impact system reliability and efficiency.[71] Lightweight curved solar-reflecting mirrors are suspended from the ceiling of the glasshouse by wires. A single-axis tracking system positions the mirrors to retrieve the optimal amount of sunlight. The mirrors concentrate the sunlight and focus it on a network of stationary steel pipes, also suspended from the glasshouse structure.[72] Water is pumped through the pipes and boiled to generate steam when intense sun radiation is applied. The steam is available for process heat. Sheltering the mirrors from the wind allows them to achieve higher temperature rates and prevents dust from building up on the mirrors as a result from exposure to humidity.[71]

## Heat collection and exchange

More energy is contained in higher frequency light based upon the formula of $E = h nu$, where h is the Planck constant and $nu$ is frequency. Metal collectors down convert higher frequency light by producing a series of Compton shifts into an abundance of lower frequency light. Glass or ceramic coatings with high transmission in the visible and UV and effective absorption in the IR (heat blocking) trap metal absorbed low frequency light from radiation loss. Convection insulation prevents mechanical losses transferred through gas. Once collected as heat, thermos containment efficiency improves significantly with increased size. Unlike Photovoltaic technologies that often degrade under concentrated light, Solar Thermal depends upon light concentration that requires a clear sky to reach suitable temperatures.

Heat in a solar thermal system is guided by five basic principles: heat gain; heat transfer; heat storage; heat transport; and heat insulation.[73] Here, heat is the measure of the amount of thermal energy an object contains and is determined by the temperature, mass and specific heat of the object. Solar thermal power plants use heat exchangers that are designed for constant working conditions, to provide heat exchange. Copper heat exchangers are important in solar thermal heating and cooling systems because of copper’s high thermal conductivity, resistance to atmospheric and water corrosion, sealing and joining by soldering, and mechanical strength. Copper is used both in receivers and in primary circuits (pipes and heat exchangers for water tanks) of solar thermal water systems.[74]

Heat gain is the heat accumulated from the sun in the system. Solar thermal heat is trapped using the greenhouse effect; the greenhouse effect in this case is the ability of a reflective surface to transmit short wave radiation and reflect long wave radiation. Heat and infrared radiation (IR) are produced when short wave radiation light hits the absorber plate, which is then trapped inside the collector. Fluid, usually water, in the absorber tubes collect the trapped heat and transfer it to a heat storage vault.

Heat is transferred either by conduction or convection. When water is heated, kinetic energy is transferred by conduction to water molecules throughout the medium. These molecules spread their thermal energy by conduction and occupy more space than the cold slow moving molecules above them. The distribution of energy from the rising hot water to the sinking cold water contributes to the convection process. Heat is transferred from the absorber plates of the collector in the fluid by conduction. The collector fluid is circulated through the carrier pipes to the heat transfer vault. Inside the vault, heat is transferred throughout the medium through convection.

Heat storage enables solar thermal plants to produce electricity during hours without sunlight. Heat is transferred to a thermal storage medium in an insulated reservoir during hours with sunlight, and is withdrawn for power generation during hours lacking sunlight. Thermal storage mediums will be discussed in a heat storage section. Rate of heat transfer is related to the conductive and convection medium as well as the temperature differences. Bodies with large temperature differences transfer heat faster than bodies with lower temperature differences.

Heat transport refers to the activity in which heat from a solar collector is transported to the heat storage vault. Heat insulation is vital in both heat transport tubing as well as the storage vault. It prevents heat loss, which in turn relates to energy loss, or decrease in the efficiency of the system.

## Heat storage for space heating

A collection of mature technologies called Seasonal thermal energy storage (STES) is capable of storing heat for months at a time, so solar heat collected primarily in Summer can be used for all-year heating. Solar-supplied STES technology has been advanced primarily in Denmark,[75] Germany,[76] and Canada,[77] and applications include individual buildings and district heating networks. Drake Landing Solar Community in Alberta, Canada has a small district system and in 2012 achieved a world record of providing 97% of the a community's all-year space heating needs from the sun.[78] STES thermal storage mediums include deep aquifers; native rock surrounding clusters of small-diameter, heat exchanger eqipped boreholes; large, shallow, lined pits that are filled with gravel and top-insulated; and large, insulated and buried surface water tanks.

## Heat storage to stabilize solar-electric power generation

Heat storage allows a solar thermal plant to produce electricity at night and on overcast days. This allows the use of solar power for baseload generation as well as peak power generation, with the potential of displacing both coal- and natural gas-fired power plants. Additionally, the utilization of the generator is higher which reduces cost.

Heat is transferred to a thermal storage medium in an insulated reservoir during the day, and withdrawn for power generation at night. Thermal storage media include pressurized steam, concrete, a variety of phase change materials, and molten salts such as calcium, sodium and potassium nitrate.[79][80]

### Steam accumulator

The PS10 solar power tower stores heat in tanks as pressurized steam at 50 bar and 285 °C. The steam condenses and flashes back to steam, when pressure is lowered. Storage is for one hour. It is suggested that longer storage is possible, but that has not been proven yet in an existing power plant.[81]

### Molten salt storage

A variety of fluids have been tested to transport the sun's heat, including water, air, oil, and sodium, but Rockwell International[82] selected molten salt as best.[83] Molten salt is used in solar power tower systems because it is liquid at atmospheric pressure, provides a low-cost medium to store thermal energy, its operating temperatures are compatible with today's steam turbines, and it is non-flammable and nontoxic. Molten salt is used in the chemical and metals industries to transport heat, so industry has experience with it.

The first commercial molten salt mixture was a common form of saltpeter, 60 percent sodium nitrate and 40 percent potassium nitrate. Saltpeter melts at 220 °C (430 °F) and is kept liquid at 290 °C (550 °F) in an insulated storage tank. Calcium nitrate can reduce the melting point to 131°C, permitting more energy to be extracted before the salt freezes. There are now several technical calcium nitrate grades stable at more than 500°C.

(talk section 21)

This solar power system can generate power in cloudy weather or at night using the heat in the tank of hot salt. The tanks are insulated, able to store heat for a week. Tanks that power a 100-megawatt turbine for four hours would be about 9 m (30 ft) tall and 24 m (80 ft) in diameter.

The Andasol power plant in Spain is the first commercial solar thermal power plant using molten salt for heat storage and nighttime generation. It came on line March 2009.[84] On July 4, 2011, a company in Spain celebrated an historic moment for the solar industry: Torresol’s 19.9 MW concentrating solar power plant became the first ever to generate uninterrupted electricity for 24 hours straight, using a molten salt heat storage.[85]

### Graphite heat storage

Direct
The proposed power plant in Cloncurry Australia will store heat in purified graphite. The plant has a power tower design. The graphite is located on top of the tower. Heat from the heliostats goes directly to the storage. Heat for energy production is drawn from the graphite. This simplifies the design.[86]

Indirect
Molten salt coolants are used to transfer heat from the reflectors to heat storage vaults. The heat from the salts are transferred to a secondary heat transfer fluid via a heat exchanger and then to the storage media, or alternatively, the salts can be used to directly heat graphite. Graphite is used as it has relatively low costs and compatibility with liquid fluoride salts. The high mass and volumetric heat capacity of graphite provide an efficient storage medium.[87]

### Phase-change materials for storage

Phase Change Material (PCMs) offer an alternative solution in energy storage. Using a similar heat transfer infrastructure, PCMs have the potential of providing a more efficient means of storage. PCMs can be either organic or inorganic materials. Advantages of organic PCMs include no corrosives, low or no undercooling, and chemical and thermal stability. Disadvantages include low phase-change enthalpy, low thermal conductivity, and flammability. Inorganics are advantageous with greater phase-change enthalpy, but exhibit disadvantages with undercooling, corrosion, phase separation, and lack of thermal stability. The greater phase-change enthalpy in inorganic PCMs make hydrate salts a strong candidate in the solar energy storage field.[88]

## Use of water

A design which requires water for condensation or cooling may conflict with location of solar thermal plants in desert areas with good solar radiation but limited water resources. The conflict is illustrated by plans of Solar Millennium, a German company, to build a plant in the Amargosa Valley of Nevada which would require 20% of the water available in the area. Some other projected plants by the same and other companies in the Mojave Desert of California may also be affected by difficulty in obtaining adequate and appropriate water rights. California water law currently prohibits use of potable water for cooling.[89]

Other designs require less water. The proposed Ivanpah Solar Power Facility in south-eastern California will conserve scarce desert water by using air-cooling to convert the steam back into water. Compared to conventional wet-cooling, this results in a 90 percent reduction in water usage at the cost of some loss of efficiency. The water is then returned to the boiler in a closed process which is environmentally friendly.[90]

## Conversion rates from solar energy to electrical energy

Of all of these technologies the solar dish/Stirling engine has the highest energy efficiency. A single solar dish-Stirling engine installed at Sandia National Laboratories National Solar Thermal Test Facility (NSTTF) produces as much as 25 kW of electricity, with a conversion efficiency of 31.25%.[91]

Solar parabolic trough plants have been built with efficiencies of about 20%.[citation needed] Fresnel reflectors have an efficiency that is slightly lower (but this is compensated by the denser packing).

The gross conversion efficiencies (taking into account that the solar dishes or troughs occupy only a fraction of the total area of the power plant) are determined by net generating capacity over the solar energy that falls on the total area of the solar plant. The 500-megawatt (MW) SCE/SES plant would extract about 2.75% of the radiation (1 kW/m²; see Solar power for a discussion) that falls on its 4,500 acres (18.2 km²).[92] For the 50 MW AndaSol Power Plant[93] that is being built in Spain (total area of 1,300×1,500 m = 1.95 km²) gross conversion efficiency comes out at 2.6%

Furthermore, efficiency does not directly relate to cost: on calculating total cost, both efficiency and the cost of construction and maintenance should be taken into account.

## Levelised cost

Since a solar power plant does not use any fuel, the cost consists primarily of capital cost with minor operational and maintenance cost. If the lifetime of the plant and the interest rate is known, the cost per kWh can be calculated. This is called the levelised energy cost.

The first step in the calculation is to determining the investment for the production of 1 kWh in a year. Example, the fact sheet of the Andasol 1 project shows a total investment of 310 million euros for a production of 179 GWh a year. Since 179 GWh is 179 million kWh, the investment per kWh a year production is 310 / 179 = 1.73 euro. Another example is Cloncurry solar power station in Australia. It was planned to produce 30 million kWh a year for an investment of 31 million Australian dollars. So, if this is achieved in reality, the cost would have been 1.03 Australian dollar for the production of 1 kWh in a year. This would have been significantly cheaper than Andasol 1, which can be partially explained by the higher radiation in Cloncurry over Spain. The investment per kWh cost for one year should not be confused with the cost per kWh over the complete lifetime of such a plant.

In most cases the capacity is specified for a power plant (for instance Andasol 1 has a capacity of 50 MW). This number is not suitable for comparison, because the capacity factor can differ. If a solar power plant has heat storage, it can also produce output after sunset, but that will not change the capacity factor; it simply displaces the output. The average capacity factor for a solar power plant, which is a function of tracking, shading and location, is about 20%, meaning that a 50 MW capacity power plant will typically provide a yearly output of 50 MW × 24 hrs × 365 days × 20% = 87,600 MWh/year, or 87.6 GWh/yr.

Although the investment for one kWh year production is suitable for comparing the price of different solar power plants, it does not give the price per kWh yet. The way of financing has a great influence on the final price. If the technology is proven, an interest rate of 7%[94] should be possible. However, for a new technology investors want a much higher rate to compensate for the higher risk. This has a significant negative effect on the price per kWh. Independent of the way of financing, there is always a linear relation between the investment per kWh production in a year and the price for 1 kWh (before adding operational and maintenance cost). In other words, if by enhancements of the technology the investments drop by 20%, the price per kWh also drops by 20%.

If a way of financing is assumed whereby the money is borrowed and repaid every year, in such way that the debt and interest decreases, the following formula can be used to calculate the division factor: (1 - (1 + interest / 100) ^ -lifetime) / (interest / 100). For a lifetime of 25 years and an interest rate of 7%, the division factor is 11.65. For example, the investment of Andasol 1 was 1.73 euro per kWh, divided by 11.65 results in a price of 0.15 euro per kWh. If one cent operation and maintenance cost is added, then the novelized cost is 0.16 euro per kWh. Other ways of financing, different way of debt repayment, different lifetime expectation, different interest rate, can lead to a significantly different number.

If the cost per kWh may follow the inflation, the inflation rate can be added to the interest rate. If an investor puts his money in a savings account for 7%, then he is not compensated for inflation. However, if the cost per kWh is raised with inflation, then he is compensated and can add 2% (a normal inflation rate) to his return. The Andasol 1 plant has a guaranteed feed-in tariff of 0.21 euro for 25 years. If this number is fixed, after 25 years with 2% inflation, 0.21 euro will have a value comparable with 0.13 euro now.

Finally, there is some gap between the first investment and the first production of electricity. This increases the investment by the interest realised over the period in which the plant is not active. The modular solar dish (but also solar photovoltaic and wind power) have the advantage that electricity production starts after first construction.

Given the facts that solar thermal power is reliable, can deliver peak load and does not cause pollution, a price of US\$0.10 per kWh[95] starts to become competitive, although a price of US\$0.06 has been claimed[96] With some operational cost a simple target is 1 dollar (or lower) investment for 1 kWh production in a year.

## Standards

• EN 12975 (efficiency test)

## Notes

1. ^ according to Dr David Mills of Ausra

## References

1. ^
2. ^
3. ^
4. ^ Manning, Paddy (10 October 2009). "With green power comes great responsibility". Sydney Morning Herald. Retrieved 2009-10-12.
5. ^ Butti and Perlin (1981), p.72
6. ^ "Energy Consumption Characteristics of Commercial Building HVAC Systems" (PDF). United States Department of Energy. pp. 1–6, 2–1. Archived from the original on 2008-04-10. Retrieved 2008-04-09.
7. ^ Apte, J. et al. "Future Advanced Windows for Zero-Energy Homes" (PDF). ASHRAE. Retrieved 2008-04-09.
8. ^ SDH (2011). Supplying Renewable Zero-Emission Heat. The SDH Project, of Intelligent Energy Europe.
9. ^ SDH - Solar District Heating program. [Website http://www.solar-district-heating.eu/SDH.aspx]. (Europe)
10. ^ "Indirect Gain (Trombe Walls)". United States Department of Energy. Retrieved 2007-09-29.
11. ^ Douglass, Elizabeth (2007-11-10). "His passion for solar still burns". Los Angeles Times. Archived from the original on 2007-12-15. Retrieved 2007-11-14.
12. ^ EIA Renewable Energy- Shipments of Solar Thermal Collectors by Market Sector, End Use, and Type
13. ^ Mugnier, D.; Jakob, U. (2012) Keeping Cool with the Sun. International Sustainable Energy Review, 6:1{28-30.
14. ^ IEA-SHC website. Research Projects (Tasks).
15. ^ Solar Process Heat
16. ^ Bartlett (1998), p.393-394
17. ^ Leon (2006), p.62
18. ^ "Solar Buildings (Transpired Air Collectors – Ventilation Preheating)" (PDF). National Renewable Energy Laboratory. Retrieved 2007-09-29.
19. ^ "Frito-Lay solar system puts the sun in SunChips, takes advantage of renewable energy". The Modesto Bee. Retrieved 2008-04-25.
20. ^ Denholm, P. (March 2007). The Technical Potential of Solar Water Heating to Reduce Fossil Fuel Use and Greenhouse Gas Emissions in the United States (PDF). National Renewable Energy Laboratory. Retrieved 2007-12-28.
21. ^ Kincaid, J. (May 2006). Durham Campaign for Solar Jobs. Archived from the original on 2007-07-15. Retrieved 2007-12-28.
22. ^ a b "Solar Thermal Energy". Retrieved Oct. 8, 2009.
23. ^ Butti and Perlin (1981), p.54-59
24. ^ "Design of Solar Cookers". Arizona Solar Center. Retrieved 2007-09-30.
25. ^ "The Solar Bowl". Auroville Universal Township. Retrieved 2008-04-25.
26. ^ "Scheffler-Reflector". Solare Bruecke. Retrieved 2008-04-25.
27. ^ "Solar Steam Cooking System". Gadhia Solar. Archived from the original on 2007-11-11. Retrieved 2008-04-25.
28. ^ ORNL's liquid fluoride proposal.
29. ^ Roland Winston et al.,, Nonimaging Optics, Academic Press, 2004 ISBN 978-0127597515
30. ^ SEGS system
31. ^ Israeli company to build largest solar park in world in US Ynetnews, 26 July 2007.
32. ^ Solar thermal electric hybrid power plant for barstow
33. ^ Iberdrola to build 150 MW Egyptian thermal solar plant
34. ^ Solar Millennium Tochter Flagsol erhält Auftrag für erstes Parabolrinnen-Kraftwerk Ägyptens
35. ^
36. ^ eSolar
37. ^ Award from Los Angeles Venture Association Honors \$130 Million Investment Round from Oak Investment Partners, Google.org and Idealab
38. ^ eSolar and Southern California Edison to Produce 245 MW of Solar Power
39. ^ eSolar Signs Exclusive License with ACME to Construct 1 Gigawatt of Solar Power Plants in India
40. ^ eSolar Launches Operating Platform for Concentrated Solar Heat and Energy Production
41. ^ "BrightSource Energy signs whopper solar contract with PG&E". CNET News. 2008-03-31. Retrieved 2008-06-11.
42. ^ "SOLAR ENERGY DEVELOPMENT CENTER (SEDC) – NEGEV, ISRAEL". BrightSource Energy.
43. ^ "BrightSource / Luz II Dedicate Negev Solar Energy Development Center". Cleantech Investing in Israel. 2008-06-12. Retrieved 2008-06-12.
44. ^ 100 MW Solar Thermal Electric Project in South Africa
45. ^ Cloncurry to run on solar alone
46. ^ "Ain Beni Mathar, Morocco Solar Thermal Power Station Project". Retrieved 2011-05-18.
47. ^ Assessment of Parabolic Trough and Power Tower Solar Technology Cost and Performance Forecasts
48. ^ Google's Goal: Renewable Energy Cheaper than Coal November 27, 2007
49. ^ ANU 'Big Dish', http://solar-thermal.anu.edu.au/
50. ^ Stirling Energy Systems Inc. - Solar Overview
51. ^ O'Grady, Patrick (23 January 2010). "SES, Tessera debut new solar plant in Peoria". Phoenix Business Journal. Retrieved June 17, 2010.
52. ^ Solar buys Tessera Solar’s Imperial Valley project with intent to turn CSP into PV
53. ^ Tessera Solar Sells Troubled 850 MW Project
54. ^ Runyon, Jennifer (2011 [last update]). "Solar Shakeout Continues: Stirling Energy Systems Files for Chapter 7 Bankruptcy". renewableenergyworld.com. Retrieved November 14, 2011.
55. ^ CLFR
56. ^ DLR - Institut für Technische Thermodynamik - Home
57. ^ PG&E links with Ausra for 177 megawatts of solar thermal power
58. ^ Ausra Sells Planned Plant to First Solar
59. ^ SK Energy GmbH: neuer deutscher Hersteller steigt in den Markt für kleine bis mittelgroße solarthermische Kraftwerke ein
60. ^ Mills, D (January 2004). "Advances in solar thermal electricity technology". Solar Energy (Elsevier) 76 (1): 19. doi:10.1016/S0038-092X(03)00102-6.
61. ^ a b Mills, D. "Advances in Solar Thermal Electricity Technology." Solar Energy 76 (2004): 19-31. 28 May 2008.
62. ^ a b Mills, D, and Morrison L. Graham. "Compact Linear Fresnel Reflector Solar Thermal Powerplants." Solar Energy 68 (2000): 263-283. 28 May 2008.
63. ^ Web site of the International Automated Systems showing concepts about Fresnel lens
64. ^ SunCube
65. ^ Desert Blooms Land Art Generator Initiative Competition
66. ^ US Solar Industry Year in Review 2008
67. ^ Hawaiian Firm Shrinks Solar Thermal Power
68. ^ SEGS
69. ^ MicroCSP in Idaho
70. ^ Sopogy introduces new solar technology at NELHA
71. ^ a b Deloitte Touche Tohmatsu Ltd, "Energy & Resources Predictions 2012", 2 November 2011
72. ^ Helman, Christopher, "Oil from the sun", "Forbes", April 25, 2011
73. ^ Five Solar Thermal Principles Canivan, John, JC Solarhomes, 26 May 2008
74. ^ 2011 global status report by Renewable Energy Policy Network for the 21st Century (REN21)); http://www.ren21.net/default.aspx?tabid=5434
75. ^ Holm L. (2012). Long Term Experiences with Solar District Heating in Denmark. Presentation. European Sustainable Energy Week, Brussels. 18 - 22 June 2012.
76. ^ Pauschinger T. (2012). Solar District Heating with Seasonal Thermal Energy Storage in Germany. Presentation. European Sustainable Energy Week, Brussels. 18 - 22 June 2012.
77. ^ Wong B. (2011). [http://www.districtenergy.org/assets/pdfs/2011Annual_Conf/Proceedings/A24WONG-v03.pdf Drake Landing Solar Community. Presentation. IDEA/CDEA District Energy/CHP 2011 Conference. Toronto, June 26-29, 2011.
78. ^ Wong B., Thornton J. (2013). Integrating Solar & Heat Pumps. Presentation. Renewable Heat Workshop.
79. ^ Sandia National Lab Solar Thermal Test Facility
80. ^ National Renewable Energy Laboratory
81. ^ Ausra Scientific American
82. ^ "Solar Reserve: How Our Technology Works". Retrieved 5 November 2012.
83. ^ "High temperature storage - Solar thermal application". Retrieved 11 October 2011.
84. ^ The Construction of the Andasol Power Plants
85. ^ Solar Can Be Baseload: Spanish CSP Plant with Storage Produces Electricity for 24 Hours Straight
86. ^ Lloyd Energy Storage, see news, Cloncurry Solar Thermal Storage Project
87. ^ Forsberg, Charles W., Per F. Peterson, and Haihua Zhao. "High Temperature Liquied Fluoride Salt Closed Brayton Cycle Solar Power Towers." Journal of Solar Energy Engineering 129 (2007): 141
88. ^ Zalba, Belen, Jose M. Marin, Luisa F. Cabeza, and Harald Mehling. "Review on Thermal Energy Storage with Phase Change: Materials, Heat Transfer Analysis and Applications." Applied Thermal Engineering 23 (2003): 251-283.
89. ^ "Alternative Energy Projects Stumble on a Need for Water" article by Todd Woody in The New York Times September 29, 2009
90. ^ BrightSource & Bechtel Partner on 440-MW Ivanpah CSP Project Renewable Energy World, September 10, 2009.
91. ^
92. ^
93. ^ 2x50 MW AndaSol Power Plant Projects in Spain
94. ^ Solar Thermal Industry Needs Loan Guarantees
95. ^ "Under 10 cents is sort of the magic line"
96. ^ Development of Two Solar-thermal Electric Hybridized Power Plant Debuts in Southern California