The SuperSmart Grid (SSG) is a hypothetical wide area electricity network connecting Europe with northern Africa, the Middle East, Turkey and the IPS/UPS system of CIS countries. The system would unify super grid and smart grid capabilities into a comprehensive network. There is no planned locations for infrastructure or schedule explicitly for the SSG; the name is used to discuss the economic and technological feasibility of such a network and ways that it might gain political support.
The ambitious upgrade and unification of current transmission and/or distribution grids finds support among advocates of large scale utilization of alternative energy, and as well as advocates of enhanced energy security for Europe. The SSG proposal was initiated by the European Climate Forum and at the Potsdam Institute for Climate Impact Research by Antonella Battaglini and colleagues.
The concept of a "Super Grid" is not new- the term itself was used to describe the emerging unification of the Great Britain grid in the 60s. Europe has been unifying its grids since the 1950s and its largest unified grid is the synchronous grid of Continental Europe serving 24 countries. There are studies and ongoing discussions regarding creation of a synchronous grid spanning 13 time zones that would result from unifying the UCTE grid with that of the IPS/UPS Interconnection serving Russia, Ukraine and other countries of the former Soviet Union. Such mega systems are experiencing scaling problems as a result of network complexity, transmission congestion, and the need for rapid diagnostic, coordination and control systems. Advocates of schemes such as the SuperSmart Grid claim that such a major technological upgrade is necessary to assure the practical operation and promised benefits of such transcontinental mega grids.
The concept of a wide area "Super grid" with centralized control and the concept of small-scale, local and decentralized smart grid are two approaches that are often perceived as being mutually exclusive alternatives. The SSG aims at reconciling the two approaches and considers them complementary and necessary to realize a transition towards a fully decarbonized electricity system. The super grid features would deliver inexpensive, high capacity, low loss transmission, interconnecting producers and consumers of electricity across vast distances. Smart grid capabilities use the local grid's transmission and distribution network to coordinate distributed generation, grid storage and consumption into a cluster that appears to the super grid as a virtual power plant.
The name SuperSmart Grid was invented by Antonella Battaglini and used the first time in the position paper for the energy conference in Lund in 2007. In the context of the SuperSmart Grid, advocates use the term "super grid" to refer to a network super imposed on top of local grid networks and should not be confused with the proper noun "SuperGrid" which refers to an undeveloped technology for combining hydrogen and electricity distribution.
The SSG relies on existing technology. The SuperSmart Grid would employ high voltage direct current (HVDC) cables in its first-generation implementation to integrate the European electricity market and possibly connect it to neighboring regions, such as North Africa, and their vast renewable energy resources, such as those that could be unlocked by the DESERTEC & Medgrid project. The SuperSmart Grid would operate 'on top' of the local high voltage AC (HVAC) grids. Existing AC grids would still transmit electricity over shorter domestic distances, but be upgraded to smart grids.
Dr Gregor Czisch of Kassel University, has constructed and optimized a model indicating that an entirely renewable electric supply system is possible at today's electric prices.
An initial project proposed by Irish wind farm developer Airtricity (Formerly Eirtricity) and Swiss engineering firm ABB would provide a chain of undersea cable connections extending from the Baltic Sea southward to Spain and servicing areas between the endpoints. Proponents of the project claim that this western corridor could be in service as early as 2015. The first segments would provide two 5000 megawatt links connecting a new 10,000 megawatt group of wind parks in the North Sea with consumers in the UK and continental Europe.
- Wide area synchronous grid
- Smart grid
- European super grid, Synchronous grid of Continental Europe
- Unified Smart Grid
- Super grid
- Pickens plan
- North Sea Offshore Grid
- David Charter (13 August 2008). "Power supergrid plan to protect Europe from Russian threat to choke off energy". The Times. Retrieved 2008-07-21.
- Alan Shaw (29 September 2005). Issues for Scotland's Energy Supply (pdf). Edinburgh, Scotland: Royal Society of Edinburgh. p. 10. Retrieved 2008-12-07. "In 1965 the first 400kV line was inaugurated, running for 150 mies from Sundon, Bedfordshire to West Burton in the Midlands. The two new 275 kV and 400kV systems running in parallel with each other became known as the Supergrid."
- Sergey Kouzmin RAO UES (5 April 2006). Synchronous Interconnection of IPS/UPS with UCTE - Study Overview (pdf). Bucharest, Romania: Black Sea Energy Conference. p. 2. Retrieved 2008-12-07.
- UCTE-IPS/UPS Study Group (7 December 2008). Feasibility Study: Synchronous Interconnection of the IPS/UPS with the UCTE (pdf ). TEN-Energy programme of the European Commission. p. 15,16.
- A. Battaglini, J. Lilliestam, C. Bals, A. Haas (18 June 2008). The SuperSmart Grid (PDF). European Climate Forum; Potsdam Institute for Climate Impact Research. Retrieved 2008-07-16.
- Gregor Czisch (24 October 2008). "Low Cost but Totally Renewable Electricity Supply for a Huge Supply Area – a European/Trans-European Example –" (pdf). 2008 Claverton Energy conference (University of Kassel). Retrieved 2008-07-16. The paper was presented at the Claverton Energy conference in Bath, 24 October 2008. See paper synopsis here.
- Peter Fairley (15 March 2006). "A Supergrid for Europe". Technology Review (Massachusetts Institute of Technology). Retrieved 2008-11-17.