0-10 V lighting control
This article relies largely or entirely on a single source. (July 2010)
0–10 V is one of the earliest and simplest electronic lighting control signaling systems; simply put, the control signal is a DC voltage that varies between zero and ten volts. There are two recognized standards current sourcing, and current sinking.
Typically used in theatrical dimming, the controller sends volts to the device. The controlled lighting should scale its output so that at 10 V, the controlled light should be at 100% of its potential output, and at 0 V it should at 0% output (i.e., off). Dimming devices may be designed to respond in various patterns to the intermediate voltages, giving output curves that are linear for: voltage output, actual light output, power output, or perceived light output.
Receivers have a nominal input impedance of 100±20 kΩ (i.e., maximum 1.0±0.2 mW at 10 V)
In production lighting this system was replaced by analog multiplexed systems such as D54 and AMX192, which themselves have been almost completely replaced by DMX512. For dimmable fluorescent lamps (where it operates instead at 1–10 V, where 1 V is minimum and 0 V is off), the system is being replaced by DSI, which itself is in the process of being replaced by DALI.
Typically utilized in architectural lighting, a current sinking control scheme uses ballast or driver provided 10V DC. The controller reduces the returned volts to the light. If the controller returns the full 10V, the light will be at its brightest level. The light will be at minimum level if no volts are returned. The current sinking scheme creates a fail safe situation. Should a control wire be cut or the controller fail, the lights will illuminate.
Commonly, the 10V control voltage is supplied through a resistor. Control is achieved (and current is sunk) by connecting a variable resistor between the control voltage terminal and ground. The two resistors form a voltage divider to produce a control voltage Vc = Vs * (Rc / (Rc + Rs)) where Vc is the returned control voltage, Vs is the source voltage, Rc is the variable control resistance, and Rs is the source resistance. Vs may be greater than 10v so that a maximum intended value of Rc produces a 10V maximum control voltage. Rc must be adjusted to a value of 0 ohms (a direct short) to return a 0V control voltage.
As a practical matter, many 0-10V dimming control inputs can be operated by replacing the variable control resistor with an electronic switch. When the switch is on, the control voltage is near 0 and the light is fully dim. When the switch is off, the control voltage is maximum and the light is fully bright. The switch is controlled by a PWM (Pulse Width Modulation) signal, which alternately turns the switch on and off at a rapid rate. The relative proportion of off time vs. on time determines brightness. For example, if the switch is off 10% of the time, the resulting control signal would be the equivalent of 1V produced with a variable resistor. The PWM method does not require selection of accurate resistance values. It can be applied simultaneously to control signals of multiple lights by connecting their control inputs in parallel.
Dimming fluorescent ballasts and dimming LED drivers often use 0–10 V control signals to control dimming functions. In many cases, the dimming range of the power supply or ballast is limited. If the light output can only be dimmed from 100% down to 10%, there must be a switch or relay available to kill power to the system and turn the light completely off. Some 0–10 V controllers offer a built-in line voltage relay, others require an external line voltage relay. Some 0-10V controllers, usually called 0-10V Blink'n'Dim adapters, create a 0-10V control signal in response to short blink signals from the power switch. Depending on the application, these options should be considered.
Advantages and disadvantages
The simplicity of the lighting system makes it straightforward to understand, implement and diagnose, and its low current (typically 1 mA) means it can be run along relatively thin cables with little voltage drop. However, since it requires one wire per control channel (plus a common return wire), a sophisticated system could have hundreds of wires, requiring expensive multicore cables and connectors. Over a long cable, the voltage drop requires every channel of the receiving device to be calibrated to compensate for the voltage losses. (This is only a theoretical limitation as the resistance of the thinnest practical wire is around 20 Ω/1000 m.) Capacitive coupling from nearby AC power cables can affect the signal to the fitting and even cause flickering. Signal wire running parallel to power cables for a fair distance would need to be screened. This is particularly difficult when control wires must be run inside closed and previously wired walls.
When using this system, one must take into consideration the actual application, since controlling office lights is not the same as controlling theatrical lighting. 0–10 V lighting control is widely used in commercial and industrial lighting by ballast manufacturers such as GE, Philips, Universal, Metrolight, Sylvania, Creative Lighting, and Lumascape. There are distributed control approaches on the market today that can be installed inside or very near the fixture(s) to be controlled thus eliminating the wire runs and the voltage drop.
- ESTA E1.3, Entertainment Technology - Lighting Control System - 0 to 10V Analog Control Protocol, Draft 9 June 1997 (CP/97-1003r1) (summarized)
- IEC Standard 60929 Annex E - AC and/or DC-supplied electronic control gear for tubular fluorescent lamps - Performance requirements (abstract)
- "GE Ballast dimming Brochure" (PDF). Archived from the original (PDF) on 19 July 2011. Retrieved 9 May 2011.
- Mark 7 0-10V - Products - Philips Lighting Electronics
- "Universal Lighting Technologies | Analog Dimming". Archived from the original on 6 September 2009. Retrieved 24 August 2018.
- Metrolight Electronic Ballasts
- "QUICKTRONIC POWERSENSE T8 Dimming Universal Voltage" (PDF). Sylvania.com. Archived from the original (PDF) on 16 July 2011.
- Creative Lighting