Air changes per hour
Air changes per hour, or air change rate, abbreviated ACH or ac/h, is a measure of the air volume added to or removed from a space (normally a room or house) divided by the volume of the space. If the air in the space is either uniform or perfectly mixed, air changes per hour is a measure of how many times the air within a defined space is replaced.
In many air distribution arrangements, air is neither uniform or perfectly mixed. The actual percentage of an enclosure's air which is exchanged in a period depends on the airflow efficiency of the enclosure and the methods used to ventilate it. The actual amount of air changed in a well mixed ventilation scenario will be 63.2% after 1 hour and 1 ACH. In order to achieve equilibrium pressure, the amount of air leaving the space and entering the space must be the same.
ACH equation in Imperial units
- N = number of air changes per hour
- Q = Volumetric flow rate of air in cubic feet per minute (cfm)
- Vol = Space volume L × W × H, in cubic feet
Ventilation rates are often expressed as a volume rate per person (CFM per person, L/s per person). The conversion between air changes per hour and ventilation rate per person is as follows:
- Rp = ventilation rate per person (CFM per person, L/s per person)
- ACPH = Air changes per hour
- D = Occupant density (occupants per square foot, occupants per square meter)
- h = Ceiling height (ft, meters)
Air change rate
|This table needs additional citations for verification. (October 2013)|
Air change rates are often used as rules of thumb in ventilation design. However, they are seldom used as the actual basis of design or calculation. For example, laboratory ventilation standards indicate recommended ranges for air change rates, as a guideline for the actual design. Residential ventilation rates are calculated based on area of the residence and number of occupants. Non-residential ventilation rates are based on floor area and number of occupants, or a calculated dilution of known contaminants. Hospital design standards use air changes per hour, although this has been criticized.
|Commercial kitchens & Toilets||15–30|
The Passive House standard requires a 0.6 ACH. Many if not most uses of ACH are actually referring to results of a standard blower door test in which 50 pascals of pressure are applied (ACH50), rather than the volume of air changed under normal conditions.
- "ANSI/ASHRAE Standard 62.2-2013: Ventilation and Acceptable Indoor Air Quality in Low-Rise Residential Buildings". Atlanta, GA: American Society of Heating, Refrigerating and Air-Conditioning Engineers. 2013.
- Bearg, David W. (1993). Indoor Air Quality and HVAC Systems. CRC Press. p. 64. ISBN 0-87371-574-8.
- "Lab Ventilation ACH Rates Standards and Guidelines" (PDF). Retrieved 9 June 2014.
- "ANSI/ASHRAE Standard 62.1-2013: Ventilation for Acceptable Indoor Air Quality". Atlanta, GA: American Society of Heating, Refrigerating and Air-Conditioning Engineers. 2013.
- "ANSI/ASHE/ASHRAE Standard 170: Ventilation for Healthcare Facilities". Atlanta, GA: American Society of Heating, Refrigerating and Air-Conditioning Engineers. 2013.
- "Engineers' Perspectives on Hospital Ventilation". Retrieved 9 June 2014.
- "International Passive House Association - Guidelines". Retrieved 23 March 2013.
|This standards- or measurement-related article is a stub. You can help Wikipedia by expanding it.|