Comparative Tracking Index
||This article includes a list of references, related reading or external links, but its sources remain unclear because it lacks inline citations. (March 2017) (Learn how and when to remove this template message)|
The Comparative Tracking Index or CTI is used to measure the electrical breakdown (tracking) properties of an insulating material. Tracking is an electrical breakdown on the surface of an insulating material wherein an initial exposure to heat chars the material, and the char is more conductive than the original insulator, producing more current flow, more heat, and eventually complete failure.
A large voltage difference gradually creates a conductive leakage path across the surface of the material by forming a carbonized track. Testing method is specified in IEC standard 60112.
To measure the tracking, 50 drops of 0.1% ammonium chloride solution are dropped on the material, and the voltage measured for a 3 mm thickness is considered representative of the material performance. Also term PTI (Proof Tracking Index) is used: it means voltage at which during testing on five samples the samples pass the test with no failures.
Performance Level Categories (PLC) were introduced to avoid excessive implied precision and bias.
The CTI value is used for electrical safety assessment of electrical apparatus, as for instance carried out by Underwriters Laboratory in USA and many other laboratories in the world. The minimum required creepage distances over an insulating material between electrically conducting parts in apparatus, especially between parts with a high voltage and parts that can be touched by human users, is dependent on the insulator's CTI value. Also for internal distances in an apparatus by maintaining CTI based distances, the risk of fire is reduced.
Creepage distance requirement depends on the CTI. Material which CTI is unknown are classified in IIIb group. There's no CTI requirement for glass, ceramic, and other inorganic material which don't breakdown on surface.
|Tracking Index (V)||PLC|
|600 and Greater||0|
|400 through 599||1|
|250 through 399||2|
|175 through 249||3|
|100 through 174||4|
In design of medical products, the CTI is treated differently. Material groups are classified as shown below, per IEC 60601-1:2005, International Standard published by the International Electrotechnical Commission:
|Comparative Tracking Index (CTI)||Material Group|
|600 ≤ CTI||I|
|400 ≤ CTI < 600||II|
|175 ≤ CTI < 400||IIIa|
|100 ≤ CTI < 175||IIIb|
- Underwriters Laboratory definition of CTI 
- IEC 60601-1:2005 Medical electrical equipment - Part 1: General requirements for basic safety and essential performance 
- IEC 61010-2-033:2012 specifies safety requirements for METERS. The METERS that have a primary purpose of measuring voltage on a live MAINS CIRCUIT 
|This engineering-related article is a stub. You can help Wikipedia by expanding it.|