Condenser (heat transfer)
This article needs additional citations for verification. (March 2015) (Learn how and when to remove this template message)
In systems involving heat transfer, a condenser is a device or unit used to condense a substance from its gaseous to its liquid state, by cooling it. In so doing, the latent heat is given up by the substance and transferred to the surrounding environment. Condensers can be made according to numerous designs, and come in many sizes ranging from rather small (hand-held) to very large (industrial-scale units used in plant processes). For example, a refrigerator uses a condenser to get rid of heat extracted from the interior of the unit to the outside air. Condensers are used in air conditioning, industrial chemical processes such as distillation, steam power plants and other heat-exchange systems. Use of cooling water or surrounding air as the coolant is common in many condensers.
Examples of condensers
- A surface condenser is one in which condensing medium and vapors are physically separated and used when direct contact is not desired. It is a shell and tube heat exchanger installed at the outlet of every steam turbine in thermal power stations. Commonly, the cooling water flows through the tube side and the steam enters the shell side where the condensation occurs on the outside of the heat transfer tubes. The condensate drips down and collects at the bottom, often in a built-in pan called a hotwell. The shell side often operates at a vacuum or partial vacuum, produced by the difference in specific volume between the steam and condensate. Conversely, the vapor can be fed through the tubes with the coolant water or air flowing around the outside.
- In chemistry, a condenser is the apparatus which cools hot vapors, causing them to condense into a liquid. See "Condenser (laboratory)" for laboratory-scale condensers, as opposed to industrial-scale condensers. Examples include the Liebig condenser, Graham condenser, and Allihn condenser. This is not to be confused with a condensation reaction which links two fragments into a single molecule by an addition reaction and an elimination reaction.
- In laboratory distillation, reflux, and rotary evaporators, several types of condensers are commonly used. The Liebig condenser is simply a straight tube within a cooling water jacket, and is the simplest (and relatively least expensive) form of condenser. The Graham condenser is a spiral tube within a water jacket, and the Allihn condenser has a series of large and small constrictions on the inside tube, each increasing the surface area upon which the vapor constituents may condense. Being more complex shapes to manufacture, these latter types are also more expensive to purchase. These three types of condensers are laboratory glassware items since they are typically made of glass. Commercially available condensers usually are fitted with ground glass joints and come in standard lengths of 100, 200, and 400 mm. Air-cooled condensers are unjacketed, while water-cooled condensers contain a jacket for the water.
- Larger condensers are also used in industrial-scale distillation processes to cool distilled vapor into liquid distillate. Commonly, the coolant flows through the tube side and distilled vapor through the shell side with distillate collecting at or flowing out the bottom.
- A condenser unit used in central air conditioning systems typically has a heat exchanger section to cool down and condense incoming refrigerant vapor into liquid, a compressor to raise the pressure of the refrigerant and move it along, and a fan for blowing outside air through the heat exchanger section to cool the refrigerant inside. A typical configuration of such a condenser unit is as follows: The heat exchanger section wraps around the sides of the unit with the compressor inside. In this heat exchanger section, the refrigerant goes through multiple tube passes, which are surrounded by heat transfer fins through which cooling air can circulate from outside to inside the unit. There is a motorized fan inside the condenser unit near the top, which is covered by some grating to keep any objects from accidentally falling inside on the fan. The fan is used to pull outside cooling air in through the heat exchanger section at the sides and blow it out the top through the grating. These condenser units are located on the outside of the building they are trying to cool, with tubing between the unit and building, one for vapor refrigerant entering and another for liquid refrigerant leaving the unit. Of course, an electric power supply is needed for the compressor and fan inside the unit.
- In a direct-contact condenser, hot vapor and cool liquid are introduced into a vessel and allowed to mix directly, rather than being separated by a barrier such as the wall of a heat exchanger tube. The vapor gives up its latent heat and condenses to a liquid, while the liquid absorbs this heat and undergoes a temperature rise. The entering vapor and liquid typically contain a single condensable substance, such as a water spray being used to cool air and adjust its humidity.
Other Types of Condensers
There are three other condensers used in HVAC systems:
- Air cooled – If the condenser is located on the outside of the unit, the air cooled condenser can provide the easiest arrangement. These types of condensers eject heat to the outdoors and are simple to install.
Most common uses for this condenser are domestic refrigerators, upright freezers and in residential packaged air conditioning units. A great feature of the air cooled condenser is they are very easy to clean. Since dirt can cause serious issues with the condensers performance, it is highly recommended that these be kept clear of dirt.
- Water cooled – Although a little more pricey to install, these condensers are the more efficient type. Commonly used for swimming pools and condensers piped for city water flow, these condensers require regular service and maintenance.
They also require a cooling tower to conserve water. To prevent corrosion and the forming of algae, water cooled condensers require a constant supply of makeup water along with water treatment.
Depending on the application you can choose from tube in tube, shell and coil or shell and tube condensers. All are essentially made to produce the same outcome, but each in a different way.
- Evaporative – While these remain the least popular choice, they are used when either water supply is inadequate to operate water cooled condenser or condensation temperature is lower that can achieved by air cooled condenser. Evaporative condensers can be used inside or outside of a building and under typical conditions, operate at a low condensing temperature.
Typically these are used in large commercial air-conditioning units. Although effective, they are not necessarily the most efficient.
For an ideal single-pass condenser whose coolant has constant density, constant heat capacity, linear enthalpy over the temperature range, perfect cross-sectional heat transfer, and zero longitudinal heat transfer, and whose tubing has constant perimeter, constant thickness, and constant heat conductivity, and whose condensible fluid is perfectly mixed and at constant temperature, the coolant temperature varies along its tube according to:
- x is the distance from the coolant inlet;
- T(x) is the coolant temperature, and T(0) the coolant temperature at its inlet;
- TH is the hot fluid's temperature;
- NTU is the number of transfer units;
- m is the coolant's mass (or other) flow rate;
- c is the coolant's heat capacity at constant pressure per unit mass (or other);
- h is the heat transfer coefficient of the coolant tube;
- P is the perimeter of the coolant tube;
- G is the heat conductance of the coolant tube (often denoted UA);
- L is the length of the coolant tube.
|Wikimedia Commons has media related to Condensers.|