This article has multiple issues. Please help improve it or discuss these issues on the talk page. (Learn how and when to remove these template messages)(Learn how and when to remove this template message)
A diesel generator also known as diesel genset is the combination of a diesel engine with an electric generator (often an alternator) to generate electrical energy. This is a specific case of engine-generator. A diesel compression-ignition engine is usually designed to run on diesel fuel, but some types are adapted for other liquid fuels or natural gas.
Diesel generating sets are used in places without connection to a power grid, or as emergency power-supply if the grid fails, as well as for more complex applications such as peak-lopping, grid support and export to the power grid.
Proper sizing of diesel generators is critical to avoid low-load or a shortage of power. Sizing is complicated by the characteristics of modern electronics, specifically non-linear loads. In size ranges around 50 MW and above, an open cycle gas turbine is more efficient at full load than an array of diesel engines, and far more compact, with comparable capital costs; but for regular part-loading, even at these power levels, diesel arrays are sometimes preferred to open cycle gas turbines, due to their superior efficiencies.
Diesel generator set
The packaged combination of a diesel engine, a generator and various ancillary devices (such as base, canopy, sound attenuation, control systems, circuit breakers, jacket water heaters and starting system) is referred to as a "generating set" or a "genset" for short.
Set sizes range from 8 to 30 kW (also 8 to 30 kVA single phase) for homes, small shops and offices with the larger industrial generators from 8 kW (11 kVA) up to 2,000 kW (2,500 kVA three phase) used for large office complexes, factories. A 2,000 kW set can be housed in a 40 ft (12 m) ISO container with fuel tank, controls, power distribution equipment and all other equipment needed to operate as a standalone power station or as a standby backup to grid power. These units, referred to as power modules are gensets on large triple axle trailers weighing 85,000 pounds (38,555 kg) or more. A combination of these modules are used for small power stations and these may use from one to 20 units per power section and these sections can be combined to involve hundreds of power modules. In these larger sizes the power module (engine and generator) are brought to site on trailers separately and are connected together with large cables and a control cable to form a complete synchronized power plant. A number of options also exist to tailor specific needs, including control panels for autostart and mains paralleling, acoustic canopies for fixed or mobile applications, ventilation equipment, fuel supply systems, exhaust systems, etc. Diesel generators, sometimes as small as 200 kW (250 kVA) are widely used not only for emergency power, but also many have a secondary function of feeding power to utility grids either during peak periods, or periods when there is a shortage of large power generators.
Ships often also employ diesel generators, sometimes not only to provide auxiliary power for lights, fans, winches etc., but also indirectly for main propulsion. With electric propulsion the generators can be placed in a convenient position, to allow more cargo to be carried. Electric drives for ships were developed before World War I. Electric drives were specified in many warships built during World War II because manufacturing capacity for large reduction gears was in short supply, compared to capacity for manufacture of electrical equipment. Such a diesel-electric arrangement is also used in some very large land vehicles such as railroad locomotives.
Generating sets are selected based on the electrical load they are intended to supply, the electrical load's characteristics such as kW, kVA, var, harmonic content, surge currents (e.g., motor starting current) and non-linear loads. The expected duty (such as emergency, prime or continuous power) as well as environmental conditions (such as altitude, temperature and exhaust emissions regulations) must also be considered.
Power plants – electrical "island" mode
One or more diesel generators operating without a connection to an electrical grid are referred to as operating in island mode. Operating generators in parallel provides the advantage of redundancy, and can provide better efficiency at partial loads. The plant brings generator sets online and takes them off line depending on the demands of the system at a given time. An islanded power plant intended for primary power source of an isolated community will often have at least three diesel generators, any two of which are rated to carry the required load. Groups of up to 20 are not uncommon.
Generators can be electrically connected together through the process of synchronization. Synchronization involves matching voltage, frequency and phase before connecting the generator to the system. Failure to synchronize before connection could cause a high short circuit current or wear and tear on the generator or its switchgear. The synchronization process can be done automatically by an auto-synchronizer module, or manually by the instructed operator. The auto-synchronizer will read the voltage, frequency and phase parameters from the generator and busbar voltages, while regulating the speed through the engine governor or ECM (Engine Control Module).
Load can be shared among parallel running generators through load sharing. Load sharing can be achieved by using droop speed control controlled by the frequency at the generator, while it constantly adjusts the engine fuel control to shift load to and from the remaining power sources. A diesel generator will take more load when the fuel supply to its combustion system is increased, while load is released if fuel supply is decreased.
Supporting main utility grids
In addition to their well known role as power supplies during power failures, diesel generator sets also routinely support main power grids worldwide in two distinct ways:
Emergency standby diesel generators, such as those used in hospitals and water plants, are, as a secondary function, widely used in the US and, in the recent past, in Great Britain to support the respective national grids at times for a variety of reasons. In the UK the tenders known as the Short Term Operating Reserve have exhibited quite variable prices, and from 2012 the volume of demand-side participation, which mainly entails the use of on-site diesels, has dropped as the tendered prices fell. Some 0.5 GWe of diesels have at times been used to support the National Grid, whose peak load is about 60 GW. These are sets in the size range 200 kW to 2 MW. This usually occurs during, for example, the sudden loss of a large conventional 660 MW plant, or a sudden unexpected rise in power demand eroding the normal spinning reserve available.
This is beneficial for both parties - the diesels have already been purchased for other reasons; but to be reliable need to be fully load tested. Grid paralleling is a convenient way of doing this. This method of operation is normally undertaken by a third party aggregator who manages the operation of the generators and the interaction with the system operator.
These diesels can in some cases be up and running in parallel as quickly as two minutes, with no impact on the site (the office or factory need not shut down). This is far quicker than a base load power station which can take 12 hours from cold, and faster than a gas turbine, which can take several minutes. Whilst diesels are very expensive in fuel terms, they are only used a few hundred hours per year in this duty, and their availability can prevent the need for base load station running inefficiently at part load continuously. The diesel fuel used is fuel that would have been used in testing anyway.
In Great Britain, National Grid can generally rely upon about 2 GW of customer demand reduction via back-up diesels being self-despatched for about 10 to 40 hours a year at times of expected peak national demand. National Grid does not control these diesels - they are run by the customer to avoid "triad" transmission network use of system (TNUoS) charges which are levied only on consumption of each site, at the three half-hours of peak national demand. It is not known in advance when the three half-hours of peak national demand (the "triad" periods) will be, so the customer must run his diesels for a good deal more half-hours a year than just three.
The total capacity of reliably operable standby generation in Britain is estimated to be around 20 GW, nearly all of which is driven by diesel engines. This is equivalent to nearly 29% of the British system peak, although only a very small fraction will ever be generating at the same time. Most plant is for large offices blocks, hospitals, supermarkets, and various installations where continuous power is important such as airports. Therefore, most is in urban areas, particularly city and commercial centres. It is estimated that around 10% of plant exceeds 1 MW, about 50% is in the 200 kW-1 MW range, and the remaining 40% is sub-200 kW. Although it is growing, only a very small proportion is believed to be used regularly for peak lopping, the vast majority just being only for standby generation. The information in this paragraph is sourced from section 6.9 of the government report : "Overcoming Barriers To Scheduling Embedded Generation To Support Distribution Networks"
A similar system to Great Britain's Short Term Operating Reserve operates in France. It is known as EJP; at times of grid stress, special tariffs can mobilize at least 5 GW of diesel generating sets to become available. In this case, the diesels prime function is to feed power into the grid.
During normal operation in synchronization with the electricity net, powerplants are governed with a five percent droop speed control. This means the full load speed is 100% and the no load speed is 105%. This is required for the stable operation of the net without hunting and dropouts of power plants. Normally the changes in speed are minor. Adjustments in power output are made by slowly raising the droop curve by increasing the spring pressure on a centrifugal governor. Generally this is a basic system requirement for all powerplants because the older and newer plants have to be compatible in response to the instantaneous changes in frequency without depending on outside communication.
Cost of generating electricity
Typical operating costs
Fuel consumption is the major portion of diesel plant owning and operating cost for power applications, whereas capital cost is the primary concern for backup generators. Specific consumption varies, but a modern diesel plant will at its near-optimal 65-70% loading, generate 3 kWh per litre.
Generator sizing and rating
Generators must provide the anticipated power required reliably and without damage and this is achieved by the manufacturer giving one or more ratings to a specific generator set model. A specific model of a generator operated as a standby generator may only need to operate for a few hours per year, but the same model operated as a prime power generator must operate continuously. When running, the standby generator may be operated with a specified - e.g. 10% overload that can be tolerated for the expected short running time. The same model generator will carry a higher rating for standby service than it will for continuous duty. Manufacturers give each set a rating based on internationally agreed definitions.
These standard rating definitions are designed to allow valid comparisons among manufacturers, to prevent manufacturers from misrating their machines, and to guide designers.
Generator Rating Definitions
Standby Rating based on Applicable for supplying emergency power for the duration of normal power interruption. No sustained overload capability is available for this rating. (Equivalent to Fuel Stop Power in accordance with ISO3046, AS2789, DIN6271 and BS5514). Nominally rated.
Typical application - emergency power plant in hospitals, offices, factories etc. Not connected to grid.
Prime (Unlimited Running Time) Rating: Should not be used for Construction Power applications. Output available with varying load for an unlimited time. Typical peak demand 100% of prime-rated ekW with 10% of overload capability for emergency use for a maximum of 1 hour in 12. A 10% overload capability is available for limited time. (Equivalent to Prime Power in accordance with ISO8528 and Overload Power in accordance with ISO3046, AS2789, DIN6271, and BS5514). This rating is not applicable to all generator set models.
Typical application - where the generator is the sole source of power for say a remote mining or construction site, fairground, festival etc.
Base Load (Continuous) Rating based on: Applicable for supplying power continuously to a constant load up to the full output rating for unlimited hours. No sustained overload capability is available for this rating. Consult authorized distributor for rating. (Equivalent to Continuous Power in accordance with ISO8528, ISO3046, AS2789, DIN6271, and BS5514). This rating is not applicable to all generator set models
Typical application - a generator running a continuous unvarying load, or paralleled with the mains and continuously feeding power at the maximum permissible level 8,760 hours per year. This also applies to sets used for peak shaving /grid support even though this may only occur for say 200 hours per year.
As an example if in a particular set the Standby Rating were 1000 kW, then a Prime Power rating might be 850 kW, and the Continuous Rating 800 kW. However these ratings vary according to manufacturer and should be taken from the manufacturer's data sheet.
Often a set might be given all three ratings stamped on the data plate, but sometimes it may have only a standby rating, or only a prime rating.
Typically however it is the size of the maximum load that has to be connected and the acceptable maximum voltage drop which determines the set size, not the ratings themselves. If the set is required to start motors, then the set will have to be at least three times the largest motor, which is normally started first. This means it will be unlikely to operate at anywhere near the ratings of the chosen set.
Many gen-set manufacturers have software programs that enable the correct choice of set for any given load combination. Sizing is based on site conditions and the type of appliances, equipment, and devices that will be powered by the generator set.
Diesel fuel is named after diesel engines, and not vice versa; diesel engines are simply compression-ignition engines, and can operate on a variety of different fuels, depending on configuration and location. Where a gas grid connection is available, gas is often used, as the gas grid will remain pressurized during almost all power cuts. This is implemented by introducing gas with the intake air and using a small amount of diesel fuel for ignition. Conversion to 100% diesel fuel operation can be achieved instantaneously.
In more rural situations, or for low load factor plant, diesel fuel derived from crude oil is a common fuel; it is less likely to freeze than heavier oils. Endurance will be limited by tank size. Diesel engines can work with the full spectrum of crude oil distillates, from natural gas, alcohols, gasoline, wood gas to the fuel oils from diesel oil to cheaper residual fuels that are like lard at room temperature, and must be heated to enable them to flow down a fuel line.
Larger engines (from about 3 MWe to 30 MWe) sometimes use heavy oils, essentially tars, derived from the end of the refining process. The slight added complexity of keeping the fuel oil heated to enable it to flow, whilst mitigating the fire risks that come from over-heating fuel, make these fuels unpopular for smaller, often unmanned, generating stations.
- Calculating the cost of the UK Transmission network: cost per kWh of transmission
- Calculating the cost of back up: See spark spread
- Energy use and conservation in the United Kingdom
- Load management
- Single-phase generator
- Standby generator
- Three-phase electric power
- Wet stacking
- "Multiple options for diesel gensets exist to tailor specific needs". E. VAN WINGEN.
-  Archived November 7, 2008, at the Wayback Machine.
- "Commercial Opportunities for Back-Up Generation and Load Reduction via National Grid, the National Electricity Transmission System Operator (NETSO) for England, Scotland, Wales and Offshore". Claverton-energy.com. 2009-12-22. Retrieved 2012-07-13.
- https://web.archive.org/web/20100217164416/http://www.claverton-energy.com/download/131/. Archived from the original on February 17, 2010. Retrieved February 8, 2016. Missing or empty
- Andrews, David (June 2007). "Emergency diesel standby generators of Wessex Water potential contribution to dealing with renewable energy sources intermittency & variability". 11 (3). The Institution of Diesel and Gas Turbine Engineers.
- "Overcoming Barriers To Scheduling Embedded Generation To Support Distribution Networks" (PDF). BERR. Archived from the original (PDF) on 2010-03-04. Retrieved 2014-07-15.
-  Archived January 7, 2010, at the Wayback Machine.
- Speed Droop and Power Generation. Application Note 01302. 2. Woodward. Speed
- "Cummins Power Generation : Model DGDB" (PDF). Cumminspower.com. Retrieved 2013-10-28.
- "Approximate Diesel Generator Fuel Consumption Chart". Dieselserviceandsupply.com. Retrieved 2012-07-13.
- "Diesel Generators - Kubota, Honda, Kohler, Mitsubishi, Daewoo, John Deere, Volvo, Volkswagen, SDMO, VM". Allworlddieselgen.com. Retrieved 2012-07-13.
- "Caterpillar - Accurate Generator Set Sizing - Online Community". Caterpillar.lithium.com. Retrieved 2012-07-13.
- "Low Speed Engines". Manbw.com. 2008-11-19. Retrieved 2009-05-11.
- "Dual-fuel-electric LNG carrie" (PDF). Thedigitalship.com. Archived from the original (PDF) on 2010-11-18. Retrieved 2013-10-28.