Flexible AC transmission system
A flexible alternating current transmission system (FACTS) is a system composed of static equipment used for the AC transmission of electrical energy. It is meant to enhance controllability and increase power transfer capability of the network. It is generally a power electronics-based system.
FACTS is defined by the IEEE as "a power electronic based system and other static equipment that provide control of one or more AC transmission system parameters to enhance controllability and increase power transfer capability."
According to Siemens "FACTS Increase the reliability of AC grids and reduce power delivery costs. They improve transmission quality and efficiency of power transmission by supplying inductive or reactive power to the grid.
In series compensation, the FACTS is connected in series with the power system. It works as a controllable voltage source. Series inductance exists in all AC transmission lines. On long lines, when a large current flows, this causes a large voltage drop. To compensate, series capacitors are connected, decreasing the effect of the inductance.Also by connecting series capacitors in series with line,the inductive reactance between the receiving end and the sending end will be reduced due to which power factor of the system can be improved. But the effect on power factor is very little when compared to shunt capacitor.
- Shunt capacitive compensation
- This method is used to improve the power factor. Whenever an inductive load is connected to the transmission line, power factor lags because of lagging load current. To compensate, a shunt capacitor is connected which draws current leading the source voltage. The net result is improvement in power factor.
- Shunt inductive compensation
- This method is used either when charging the transmission line, or, when there is very low load at the receiving end. Due to very low, or no load – very low current flows through the transmission line. Shunt capacitance in the transmission line causes voltage amplification (Ferranti effect). The receiving end voltage may become double the sending end voltage (generally in case of very long transmission lines). To compensate, shunt inductors are connected across the transmission line. The power transfer capability is thereby increased depending upon the power equation
In the case of a no-loss line, voltage magnitude at the receiving end is the same as voltage magnitude at the sending end: Vs = Vr=V. Transmission results in a phase lag that depends on line reactance X.
As it is a no-loss line, active power P is the same at any point of the line:
Reactive power at sending end is the opposite of reactive power at receiving end:
As is very small, active power mainly depends on whereas reactive power mainly depends on voltage magnitude.
FACTS for series compensation modify line impedance: X is decreased so as to increase the transmittable active power. However, more reactive power must be provided.
Reactive current is injected into the line to maintain voltage magnitude. Transmittable active power is increased but more reactive power is to be provided.
Examples of series compensation
- Static synchronous series compensator (SSSC)
- Thyristor-controlled series capacitor (TCSC): a series capacitor bank is shunted by a thyristor-controlled reactor
- Thyristor-controlled series reactor (TCSR): a series reactor bank is shunted by a thyristor-controlled reactor
- Thyristor-switched series capacitor (TSSC): a series capacitor bank is shunted by a thyristor-switched reactor
- Thyristor-switched series reactor (TSSR): a series reactor bank is shunted by a thyristor-switched reactor
Examples of shunt compensation
- Static synchronous compensator (STATCOM); previously known as a static condenser (STATCON)
- Static VAR compensator (SVC). Most common SVCs are:
- Thyristor-controlled reactor (TCR): reactor is connected in series with a bidirectional thyristor valve. The thyristor valve is phase-controlled. Equivalent reactance is varied continuously.
- Thyristor-switched reactor (TSR): Same as TCR but thyristor is either in zero- or full- conduction. Equivalent reactance is varied in stepwise manner.
- Thyristor-switched capacitor (TSC): capacitor is connected in series with a bidirectional thyristor valve. Thyristor is either in zero- or full- conduction. Equivalent reactance is varied in stepwise manner.
- Mechanically-switched capacitor (MSC): capacitor is switched by circuit-breaker. It aims at compensating steady state reactive power. It is switched only a few times a day.
- In-line references
- Proposed terms and definitions for flexible AC transmission system(FACTS), IEEE Transactions on Power Delivery, Volume 12, Issue 4, October 1997, pp. 1848–1853. doi: 10.1109/61.634216[dead link]
- Flexible AC Transmission Systems (FACTS) - Siemens
- General references
- Narain G. Hingorani, Laszlo Gyugyi Understanding FACTS: Concepts and Technology of Flexible AC Transmission Systems, Wiley-IEEE Press, December 1999. ISBN 978-0-7803-3455-7
- Xiao-Ping Zhang, Christian Rehtanz, Bikash Pal, Flexible AC Transmission Systems: Modelling and Control, Springer, March 2006. ISBN 978-3-540-30606-1. http://link.springer.com/book/10.1007%2F3-540-30607-2
- Xiao-Ping Zhang, Christian Rehtanz, Bikash Pal, Flexible AC Transmission Systems: Modelling and Control, 2nd Edition, Springer, Feb 2012, ISBN 978-3-642-28240-9 (Print) 978-3-642-28241-6 (Online), http://link.springer.com/book/10.1007%2F978-3-642-28241-6
- A. Edris, R. Adapa, M.H. Baker, L. Bohmann, K. Clark, K. Habashi, L. Gyugyi, J. Lemay, A. Mehraban, A.K. Myers, J. Reeve, F. Sener, D.R. Torgerson, R.R. Wood, Proposed Terms and Definitions for Flexible AC Transmission System (FACTS), IEEE Transactions on Power Delivery, Vol. 12, No. 4, October 1997. doi: 10.1109/61.634216[dead link] http://ieeexplore.ieee.org/stamp/stamp.jsp?arnumber=00634216