Heat transfer coefficient
||It has been suggested that thermal transmittance be merged into this article. (Discuss) Proposed since June 2014.|
The heat transfer coefficient or film coefficient, in thermodynamics and in mechanics is the proportionality coefficient between the heat flux and the thermodynamic driving force for the flow of heat (i.e., the temperature difference, ΔT):
- q: amount of heat transferred (Heat Flux), W/m2 i.e., thermal power per unit area, q = d/dA
- h: heat transfer coefficient, W/(m2•K)
- ΔT: difference in temperature between the solid surface and surrounding fluid area, K.
The heat transfer coefficient has SI units in watts per squared meter kelvin: W/(m2K).
There are numerous methods for calculating the heat transfer coefficient in different heat transfer modes, different fluids, flow regimes, and under different thermohydraulic conditions. Often it can be estimated by dividing the thermal conductivity of the convection fluid by a length scale. The heat transfer coefficient is often calculated from the Nusselt number (a dimensionless number). There are also online calculators available specifically for heat transfer fluid applications. Experimental assessment of the heat transfer coefficient poses some challenges especially when small fluxes are to be measured (e.g. ).  
- 1 Composition
- 2 Convective heat transfer correlations
- 2.1 External flow, vertical plane
- 2.2 External flow, vertical cylinders
- 2.3 External flow, horizontal plates
- 2.4 External flow, horizontal cylinder
- 2.5 External flow, spheres
- 2.6 Forced convection
- 3 Thom correlation
- 4 Heat transfer coefficient of pipe wall
- 5 Combining heat transfer coefficients
- 6 Overall heat transfer coefficient
- 7 Thermal resistance due to fouling deposits
- 8 See also
- 9 References
- 10 External links
A simple method for determining an overall heat transfer coefficient that is useful to find the heat transfer between simple elements such as walls in buildings or across heat exchangers is shown below. Note that this method only accounts for conduction within materials, it does not take into account heat transfer through methods such as radiation. The method is as follows:
- = the overall heat transfer coefficient (W/(m2•K))
- = the contact area for each fluid side (m2) (with and expressing either surface)
- = the thermal conductivity of the material (W/(m·K))
- = the individual convection heat transfer coefficient for each fluid (W/(m2•K))
- = the wall thickness (m).
As the areas for each surface approach being equal the equation can be written as the transfer coefficient per unit area as shown below:
It is to be noted that often the value for is referred to as the difference of two radii where the inner and outer radii are used to define the thickness of a pipe carrying a fluid, however, this figure may also be considered as a wall thickness in a flat plate transfer mechanism or other common flat surfaces such as a wall in a building when the area difference between each edge of the transmission surface approaches zero.
In the walls of buildings the above formula can be used to derive the formula commonly used to calculate the heat through building components. Architects and engineers call the resulting values either the U-Value or the R-Value of a construction assembly like a wall. Each type of value (R or U) are related as the inverse of each other such that R-Value = 1/U-Value and both are more fully understood through the concept of an overall heat transfer coefficient described in lower section of this document.
Convective heat transfer correlations
Although convective heat transfer can be derived analytically through dimensional analysis, exact analysis of the boundary layer, approximate integral analysis of the boundary layer and analogies between energy and momentum transfer, these analytic approaches may not offer practical solutions to all problems when there are no mathematical models applicable. As such, many correlations were developed by various authors to estimate the convective heat transfer coefficient in various cases including natural convection, forced convection for internal flow and forced convection for external flow. These empirical correlations are presented for their particular geometry and flow conditions. As the fluid properties are temperature dependent, they are evaluated at the film temperature , which is the average of the surface and the surrounding bulk temperature, .
External flow, vertical plane
Churchill and Chu correlation for natural convection adjacent to vertical planes. NuL applies to all fluids for both laminar and turbulent flows. L is the characteristic length with respect to the direction of gravity, and RaL is the Rayleigh Number with respect to this length.
For laminar flows in the range of , the following equation can be further improved.
External flow, vertical cylinders
For cylinders with their axes vertical, the expressions for plane surfaces can be used provided the curvature effect is not too significant. This represents the limit where boundary layer thickness is small relative to cylinder diameter . The correlations for vertical plane walls can be used when
where is the Grashof number.
External flow, horizontal plates
W. H. McAdams  suggested the following correlations. The induced buoyancy will be different depending upon whether the hot surface is facing up or down. For a hot surface facing up or a cold surface facing down,
For a hot surface facing down or a cold surface facing up,
The length is the ratio of the plate surface area to perimeter. If the plane surface is inclined at an angle θ, the equations for vertical plane by Churchill and Chu may be used for θ up to . When boundary layer flow is laminar, the gravitational constant is replaced with g cosθ for calculating the Ra in the equation for laminar flow.
External flow, horizontal cylinder
For cylinders of sufficient length and negligible end effects, Churchill and Chu has the following correlation for
External flow, spheres
For spheres, T. Yuge  has the following correlation for Pr≃1 and
Internal flow, laminar flow
Sieder and Tate  has the following correlation for laminar flow in tubes where is the internal diameter, is the fluid viscosity at the bulk mean temperature, is the viscosity at the tube wall surface temperature.
Internal flow, turbulent flow
The Dittus-Bölter correlation (1930) is a common and particularly simple correlation useful for many applications. This correlation is applicable when forced convection is the only mode of heat transfer; i.e., there is no boiling, condensation, significant radiation, etc. The accuracy of this correlation is anticipated to be ±15%.
For a fluid flowing in a straight circular pipe with a Reynolds number between 10 000 and 120 000 (in the turbulent pipe flow range), when the fluid's Prandtl number is between 0.7 and 120, for a location far from the pipe entrance (more than 10 pipe diameters; more than 50 diameters according to many authors) or other flow disturbances, and when the pipe surface is hydraulically smooth, the heat transfer coefficient between the bulk of the fluid and the pipe surface can be expressed explicitly as:
- is the hydraulic diameter
- is the thermal conductivity of the bulk fluid
- mass flux
- isobaric heat capacity
- n = 0.4 for heating (wall hotter than the bulk fluid) and 0.33 for cooling (wall cooler than the bulk fluid).
The fluid properties necessary for the application of this equation are evaluated at the bulk temperature thus avoiding iteration
Forced convection, external flow
In analyzing the heat transfer associated with the flow past the exterior surface of a solid, the situation is complicated by phenomena such as boundary layer separation. Various authors have correlated charts and graphs for different geometries and flow conditions. For flow parallel to a plane surface, where is the distance from the edge and is the height of the boundary layer, a mean Nusselt number can be calculated using the Colburn analogy.
There exist simple fluid-specific correlations for heat transfer coefficient in boiling. The Thom correlation is for the flow of boiling water (subcooled or saturated at pressures up to about 20 MPa) under conditions where the nucleate boiling contribution predominates over forced convection. This correlation is useful for rough estimation of expected temperature difference given the heat flux:
- is the wall temperature elevation above the saturation temperature, K
- q is the heat flux, MW/m2
- P is the pressure of water, MPa
Note that this empirical correlation is specific to the units given.
Heat transfer coefficient of pipe wall
The resistance to the flow of heat by the material of pipe wall can be expressed as a "heat transfer coefficient of the pipe wall". However, one needs to select if the heat flux is based on the pipe inner or the outer diameter. Selecting to base the heat flux on the pipe inner diameter, and assuming that the pipe wall thickness is small in comparison with the pipe inner diameter, then the heat transfer coefficient for the pipe wall can be calculated as if the wall were not curved:
where k is the effective thermal conductivity of the wall material and x is the wall thickness.
If the above assumption does not hold, then the wall heat transfer coefficient can be calculated using the following expression:
where di and do are the inner and outer diameters of the pipe, respectively.
The thermal conductivity of the tube material usually depends on temperature; the mean thermal conductivity is often used.
Combining heat transfer coefficients
For two or more heat transfer processes acting in parallel, heat transfer coefficients simply add:
For two or more heat transfer processes connected in series, heat transfer coefficients add inversely:
For example, consider a pipe with a fluid flowing inside. The approximate rate of heat transfer between the bulk of the fluid inside the pipe and the pipe external surface is:
- q = heat transfer rate (W)
- h = heat transfer coefficient (W/(m2·K))
- t = wall thickness (m)
- k = wall thermal conductivity (W/m·K)
- A = area (m2)
- = difference in temperature.
Overall heat transfer coefficient
The overall heat transfer coefficient is a measure of the overall ability of a series of conductive and convective barriers to transfer heat. It is commonly applied to the calculation of heat transfer in heat exchangers, but can be applied equally well to other problems.
For the case of a heat exchanger, can be used to determine the total heat transfer between the two streams in the heat exchanger by the following relationship:
- = heat transfer rate (W)
- = overall heat transfer coefficient (W/(m²·K))
- = heat transfer surface area (m2)
- = log mean temperature difference (K).
The overall heat transfer coefficient takes into account the individual heat transfer coefficients of each stream and the resistance of the pipe material. It can be calculated as the reciprocal of the sum of a series of thermal resistances (but more complex relationships exist, for example when heat transfer takes place by different routes in parallel):
- R = Resistance(s) to heat flow in pipe wall (K/W)
- Other parameters are as above.
The heat transfer coefficient is the heat transferred per unit area per kelvin. Thus area is included in the equation as it represents the area over which the transfer of heat takes place. The areas for each flow will be different as they represent the contact area for each fluid side.
The thermal resistance due to the pipe wall is calculated by the following relationship:
- x = the wall thickness (m)
- k = the thermal conductivity of the material (W/(m·K))
- A = the total area of the heat exchanger (m2)
This represents the heat transfer by conduction in the pipe.
As mentioned earlier in the article the convection heat transfer coefficient for each stream depends on the type of fluid, flow properties and temperature properties.
Some typical heat transfer coefficients include:
- Air - h = 10 to 100 W/(m2K)
- Water - h = 500 to 10,000 W/(m2K).
Thermal resistance due to fouling deposits
Often during their use, heat exchangers collect a layer of fouling on the surface which, in addition to potentially contaminating a stream, reduces the effectiveness of heat exchangers. In a fouled heat exchanger the buildup on the walls creates an additional layer of materials that heat must flow through. Due to this new layer, there is additional resistance within the heat exchanger and thus the overall heat transfer coefficient of the exchanger is reduced. The following relationship is used to solve for the heat transfer resistance with the additional fouling resistance:
- = overall heat transfer coefficient for a fouled heat exchanger,
- = perimeter of the heat exchanger, may be either the hot or cold side perimeter however, it must be the same perimeter on both sides of the equation,
- = overall heat transfer coefficient for an unfouled heat exchanger,
- = fouling resistance on the cold side of the heat exchanger,
- = fouling resistance on the hot side of the heat exchanger,
- = perimeter of the cold side of the heat exchanger,
- = perimeter of the hot side of the heat exchanger,
This equation uses the overall heat transfer coefficient of an unfouled heat exchanger and the fouling resistance to calculate the overall heat transfer coefficient of a fouled heat exchanger. The equation takes into account that the perimeter of the heat exchanger is different on the hot and cold sides. The perimeter used for the does not matter as long as it is the same. The overall heat transfer coefficients will adjust to take into account that a different perimeter was used as the product will remain the same.
The fouling resistances can be calculated for a specific heat exchanger if the average thickness and thermal conductivity of the fouling are known. The product of the average thickness and thermal conductivity will result in the fouling resistance on a specific side of the heat exchanger.
- = average thickness of the fouling in a heat exchanger,
- = thermal conductivity of the fouling, .
- Convective heat transfer
- Heat sink
- Churchill–Bernstein equation
- Heat pump
- Heisler Chart
- Thermal conductivity
- Biot number
- Fourier number
- Nusselt number
- Chiavazzo, Eliodoro; Ventola, Luigi; Calignano, Flaviana; Manfredi, Diego; Asinari, Pietro (2014). "A sensor for direct measurement of small convective heat fluxes: Validation and application to micro-structured surfaces". Experimental Thermal and Fluid Science 55. doi:10.1016/j.expthermflusci.2014.02.010.
- Maddox, D.E.; Mudawar, I. (1989). "Single- and Two-Phase Convective Heat Transfer From Smooth and Enhanced Microelectronic Heat Sources in a Rectangular Channel". J. Heat Transfer 111.
- James R. Welty; Charles E. Wicks; Robert E. Wilson; Gregory L. Rorrer (2007). Fundamentals of Momentum, Heat and Mass transfer (5th edition). John Wiley and Sons. ISBN 978-0470128688.
- S. S. Kutateladze; V. M. Borishanskii (1966). A Concise Encyclopedia of Heat Transfer. Pergamon Press.
- F. Kreith, ed. (2000). The CRC Handbook of Thermal Engineering. CRC Press.
- W. Rohsenow; J. Hartnet; Y. Cho (1998). Handbook of Heat Transfer (3rd edition). McGraw-Hill.
- This relationship is similar to the harmonic mean; however, note that it is not multiplied with the number n of terms.
- "Heat transfer between the bulk of the fluid inside the pipe and the pipe external surface". http://physics.stackexchange.com. Retrieved 15 December 2014.
- Coulson and Richardson, "Chemical Engineering", Volume 1,Elsevier, 2000
- A.F. Mills (1999). Heat Transfer (second edition). Prentice Hall, Inc.