Hinkley Point A nuclear power station
|Hinkley Point A nuclear power station|
Hinkley Point A twin buildings housing the Magnox reactors
|Location||Hinkley Point, Somerset, South West England|
|Owner(s)||Central Electricity Generating Board|
Nuclear Decommissioning Authority
|Nuclear power station|
|Reactor type||Magnox GCR|
|Reactor supplier||English Electric & Babcock & Wilcox Ltd|
|Cooling source||Sea water Severn Estuary|
|Thermal capacity||2 x 960 MWt (Gross)|
|Make and model||English Electric|
|Units decommissioned||2 x 250 MWe (Net. 235 MWe) |
|Nameplate capacity||500 MWe|
|Annual net output||3,261 GW·h (1994)|
|Commons||Related media on Commons|
Hinkley Point A nuclear power station is a decommissioned Magnox Nuclear power station located on a 19.4-hectare (48-acre) site in Somerset on the Bristol Channel coast, 5 miles (8 km) west of the River Parrett estuary.
The construction of the power station, which was undertaken by a consortium backed by English Electric, Babcock & Wilcox Ltd and Taylor Woodrow Construction, began in 1957. The reactors and the turbines were supplied by English Electric.
The power station, which is currently[when?] being decommissioned, had two Magnox reactors, each supplying steam to three English Electric 93.5 MWe turbine generator sets which were all together across both reactors designed to produce 500 MWe net but, after de-rating of the reactor power output due to corrosion concerns, both reactors combined produced 470 MWe net.
The design followed the principles established by the Calder Hall nuclear power station, in that it used a reactor core of natural uranium fuel in Magnox alloy cans within a graphite moderator, all contained in a welded steel pressure vessel. The core was cooled by CO2 pumped by six nominal 7,000 hp (5.2 MW) gas circulators, which transported the hot gas from the core to the six Steam Raising Units (boilers) via steel ducts. The gas circulators could be driven by induction motors supplied with mains electricity or, when steam was available, dedicated variable speed turbo alternator sets. The design pressure of the gas circuit was 185 psig, and the temperature of the gas leaving the reactor was 378 °C, although this was later reduced when the hot CO2 was found to be corroding the mild steel components of the gas circuit more quickly than had been anticipated. Like all Magnox reactors, Hinkley Point A was designed for on-load refuelling so that exhausted fuel elements could be replaced with fresh without shutting down the reactor.
Like all other British Magnox power stations, Hinkley Point A had numerous backup systems to maintain an excellent safety record throughout its life. Emergency backup systems consisting of 5 x 1,050 hp English Electric 8CSV Diesel Generating Sets were installed at the station, which provided power to both reactors gas circulation systems if external power was lost in the event of a SCRAM. On 22 April 1966 the Minister of Power Richard Marsh officially opened the new nuclear power plant..
|Output of Main Turbines||6 x 93.5 MW 500 MW|
|Area of Main Station||16.2 ha (40 acres)|
|Fuel Per Reactor||355 t (349 tons)|
|Fuel Surface Temperature||about 430 Degrees Celsius|
|CO2 Pressure||12.7 bar g (185 lb/in2 g)|
|CO2 Channel Outlet Temperature||387 Degrees Celsius|
|Number of Channels per Reactor||4500|
|Total Weight of Graphite per Core||1891 t (1861 tons)|
|Steam Conditions Turbine Stop Valve HP||45.5 bar g (660 lb/in2 g) 363 Degrees Celsius|
|Steam Conditions Turbine Stop Valve IP||IP 12.7 bar g (183 lb/in2 g) 354 Degrees Celsius|
Capacity and output
The generating capacity, electricity output, load factor and thermal efficiency was as shown in the table.
|Year||Net capability, MW||Electricity supplied, GWh||Load as percent of capability, %||Thermal efficiency, %|
Gas circulator design problem
In August 1963 during a hot run test on the first reactor, which had not then been loaded with nuclear fuel, problems were encountered due to noise from the single stage axial flow gas circulators. This could be heard up to five miles away, and personnel working at the station had to wear ear defenders. After unexplained drops in the mass flow rate and motor driving current in number 3 and 5 gas circulators, the hot run tests were stopped and the gas circuit opened up. Severe mechanical damage to the blading and diffuser sections of the number 3 and 5 gas circulators was observed. Large sections of the diffusers had broken away, and extensive fatigue cracking was found in the outer tapering shell and central axial cone. Large pieces of the diffuser casing had entered the gas circulator blades and caused heavy impact damage, and large amounts of debris had been transported down the gas duct. The Inlet Guide Vanes (IGVs), which were provided to enable the performance of individual gas circulators to be "trimmed," were found to be extensively damaged, and the rotor blades and outlet guide vanes also had extensive impact and fatigue damage. Large numbers of the nuts and bolts involved had been shaken loose.
The subsequent investigation determined that the noise was caused by interaction between the IGVs and the rotor blades. The sound pressure levels generated by this noise were high enough to cause rapid fatigue failure in gas circuit components, and major re-design of the gas circulators and associated components was required. The IGVs were scrapped and flow straighteners introduced to smooth the flow of gas into the gas circulator intakes. Much pioneering experimental laboratory work on resonance and sound pressure levels was performed at English Electric's Gas Turbine and Atomic Power Division (APD) facilities at Whetstone, Leicestershire, to support the redesign work, and instrumentation to measure stress and sound pressure levels in the gas circuit during testing was developed. The delay caused severe financial difficulties for the consortium and set the construction schedule back; the station began generating electricity two years late in 1965.
The importance of materials design and the understanding of grain boundaries was highlighted during the operation of Hinkley Point. In 1969 there was a catastrophic failure of the Hinkley Point ‘A’ turbine-generator at near normal speeds (3200 rev/min). The interaction of fragments of the burst disc and the shaft caused the adjacent disc to burst almost immediately afterwards, and in the general disruption that followed another disc disintegrated completely and the entire unit was irreparably damaged. This is thought to be the first catastrophic failure of a turbine-generator in Britain. The characteristics of the material from which the burst discs were made were a contributory factor in the failure. The 3 Cr-Mo steel made by the a.0.h. process was temper embrittled during slow furnace cooling after heat treatment and therefore had poor fracture toughness, i.e. low tolerance of very sharp crack-like defects in highly stressed regions. Such material can of course be used quite safely in highly stressed regions in the absence of cracks. A material of higher fracture toughness would have tolerated larger cracks without succumbing to their unstable propagation, and the failure would have been postponed if not avoided. At the time of the manufacture of these discs, it was not possible to quantify the effect of embrittlement on the material’s ability to tolerate small cracks in the most highly stressed regions. The reason for the failure was down to transport of phosphor towards the grain boundaries which embrittled the chromium steel causing it to fail 
Closure and Decommissioning
Both reactors were shut down in April 1999 to carry out reinforcement work following a Nuclear Installations Inspectorate Periodic Safety Review. Reactor 2 was returned to service in September 1999, but shut down on 3 December 1999 because of newly identified uncertainties in the reactor pressure vessel material properties. Because of the cost of remedying these problems, it was announced on 23 May 2000 that Hinkley Point A would be shut down.
Hinkley Point A was one of eleven Magnox nuclear power stations commissioned in the United Kingdom between 1956 and 1971. During its 35 years of operation, Hinkley Point A generated more than 103 TWh of electricity, giving a lifetime load factor against design of 34%.
Defuelling and removal of most buildings is expected to take until 2031, followed by a care and maintenance phase from 2031 to 2085. Demolition of reactor buildings and final site clearance is planned for 2081 to 2091 
The Hinkley Point Site is currently organized as two nuclear power stations: Next to Hinkley Point A with its two Magnox reactor buildings there is Hinkley Point B, operated by EDF Energy, with two AGCR reactors in one building. In October 2013, the UK government announced that it had approved the construction of Hinkley Point C. This new plant, consisting of two EPR units, is scheduled to be completed in 2023 and remain operational for around 60 years.
- "IAEA PRIS". Retrieved 14 Oct 2014.
- Nuclear Development in the United Kingdom
- "Nuclear Power Plants in the UK". Archived from the original on 2009-07-19. Retrieved 2009-04-11.
- "PRIS - Reactor Details Hinkley A1". PRIS. Retrieved 2015-07-28.
- David Lowry (13 November 2014). "The world's first 'Nuclear Proliferation Treaty'". Ecologist. Retrieved 2 December 2014.
- Reginald Maudling (24 June 1958). "Atomic Power Stations (Plutonium Production)". Hansard. UK Parliament. HC Deb 24 June 1958 vol 590 cc246-8. Retrieved 2 December 2014.
the Central Electricity Generating Board has agreed to a small modification in the design of Hinkley Point and of the next two stations in its programme so as to enable plutonium suitable for military purposes to be extracted should the need arise.
- "The Electrical Review". Electrical Review. 178 (9–17): 638. 1966.
- "Nuclear Technology Society in the German Atomic Forum". Handelsblatt Gmbh. 11: 50, 225. 1966.
- Hinkley Point B Nuclear Power Station. Information Services, Sudbury House, 15 Newgate Street, London EC1 7AU: Central Electricity Generating Board. April 1971. p. 4.CS1 maint: location (link)
- CEGB Statistical Yearbooks 1972-84, CEGB, London
- "Investigations into the failure of gas circulators and circuit components at Hinkley Point nuclear power station" Rizk, W and Seymour, D F Proceedings of the Institution of Mechanical Engineers, v179 1964 p627-703
- "Hinkley A: 1965". BBC Somerset. BBC. Retrieved 2008-07-05.
- Kalderon, D. (1972). Steam Turbine Failure at Hinkley Point “A.” Proceedings of the Institution of Mechanical Engineers, 186(1), 341–377. https://doi.org/10.1243/PIME_PROC_1972_186_037_02
- Seah, M. P. (1977). Grain boundary segregation and the T-t dependence of temper brittleness. Acta Metallurgica, 25(3), 345–357. https://doi.org/10.1016/0001-6160(77)90153-5
- Lejček, P., & Hofmann, S. (1995). Thermodynamics and structural aspects of grain boundary segregation. Critical Reviews in Solid State and Materials Sciences, 20(1), 1–85. https://doi.org/10.1080/10408439508243544
- Lozovoi, A. Y., Paxton, A. T., & Finnis, M. W. (2006). Structural and chemical embrittlement of grain boundaries by impurities: A general theory and first-principles calculations for copper. Physical Review B - Condensed Matter and Materials Physics, 74(15), 155416. https://doi.org/10.1103/PhysRevB.74.155416
- Nuclear Installations Inspectorate (September 2000). Report by HM Nuclear Installations Inspectorate on the results of Magnox Long Term Safety Reviews (LTSRs) and Periodic Safety Reviews (PSRs) (PDF) (Report). Health and Safety Executive. p. 37 (Appendix E). Retrieved 2010-03-21.
- "Hinkley Point A - Facts and figures". Magnox Ltd. Archived from the original on 17 August 2011. Retrieved 7 February 2011.
- "The 2010 UK Radioactive Waste Inventory: Main Report" (PDF). Nuclear Decommissioning Agency/Department of Energy & Climate Change. February 2011. Archived from the original (PDF) on 25 March 2012. Retrieved 22 May 2012.
- "UK nuclear power plant gets go-ahead". BBC News. 21 October 2013. Retrieved 21 October 2013.
|Wikimedia Commons has media related to Hinkley Point A Nuclear Power Station.|