IEC 61334 is a standard for low-speed reliable power line communications by electricity meters, water meters and SCADA. It is also known as spread frequency shift keying (S-FSK) and was formerly known as IEC 1334 before IEC's most recent renumbering. It is actually a series of standards describing the researched physical environment of power lines, a well-adapted physical layer, a workable low-power media access layer, and a management interface. Related standards use the physical layer (e.g. Internet Protocol over S-FSK), but not the higher layers.
The physical layer synchronizes a small packet of tones to the zero-crossing of the power line's voltage. The tones are chosen by utilities, not specified in the standard. Tones are usually between 20 kHz and 100 kHz, and should be separated by at least 10 kHz to prevent cross talk. One tone is chosen for mark (i.e. a binary 1), and the other for space (i.e. 0). The standard permits each zero-crossing to convey 1, 2, 4 or 8 bits, with increased sensitivity to timing as the number of bits increases. In multiphase power lines, a separate signal might be sent on each phase to speed up the transmission.
The standard's low speed is caused by the limited number of bits per power line cycle. The high reliability comes from its reliable timing system (i.e. zero crossing), high signal to noise ratio (frequencies are chosen to avoid common power line noise), lack of intermodulation distortion, and adaptive signal detection.
The most significant bits are sent first, unlike a conventional serial port. The data from zero crossings should be collected into 8-bit bytes. Each byte is collected into 42-byte packets. The first four bytes of each packet are a preamble to measure the channel's current condition. This is followed by 38 bytes of data, and 3 byte-times of silence.
The physical layer is adaptive. The silence and the preamble allow the receiver's signal processing to measure the channel's noise ratios. Depending on the signal to noise ratios, the bits can be recovered from the difference between the power of the mark and space tones, the power of the mark tones only, or the space tones only. The system should be able to adjust the receiving method on each 42-byte packet.
The bytes from the low-layer packets are reformed into bytes for the higher layers. The higher link-layer strongly resembles HDLC, except with a novel feature that allows selected stations to retransmit messages. The management interface layer provides remote control of a station's protocol layers, including diagnostics and configuration. For example, it lets a central controller read a unit's signal to noise ratios, and set the bit that enables a station to retransmit weak stations.
The protocol layers are designed to integrate with any application layer, but the presence of a management interface suggests a design targeted to DLMS/COSEM, a widely used EU standard for the application layer of meters and SCADA. DLMS/COSEM requires a management interface.
spread spectrum frequency shift keying
S-FSK (spread spectrum frequency shift keying) is a modulation scheme that combines some of the advantages of classical spread-spectrum modulation (immunity against narrow-band interference) with some of the advantages of classical frequency-shift keying (FSK is low complexity). The difference between S-FSK and classical FSK is that in S-FSK, the mark frequency is placed far from the space frequency . The frequencies are placed far enough apart that frequency-selective fading and narrow-band interference only blocks one of the frequencies, so the receiver can still recover all the data from the other frequency.
- Power line communication for a survey of the topic.
- Universal powerline bus is the more common shorter-ranged competitor.
- IEC 61334-5-1, preface.
- ADD GRUP, Russia
- IEC 61334-4-1
- IEC 61334-4-1154
- IEC 61334-1155
- "Power Line Carrier Modem". 2014. p. 16