|This article needs additional citations for verification. (May 2009) (Learn how and when to remove this template message)|
LonWorks (local operating network) is a networking platform specifically created to address the needs of control applications. The platform is built on a protocol created by Echelon Corporation for networking devices over media such as twisted pair, powerlines, fiber optics, and RF. It is used for the automation of various functions within buildings such as lighting and HVAC; see building automation.
Origins and uptake
The technology has its origins with chip designs, power line and twisted pair, signaling technology, routers, network management software, and other products from Echelon Corporation. In 1999 the communications protocol (then known as LonTalk) was submitted to ANSI and accepted as a standard for control networking (ANSI/CEA-709.1-B). Echelon's power line and twisted pair signaling technology was also submitted to ANSI for standardization and accepted. Since then, ANSI/CEA-709.1 has been accepted as the basis for IEEE 1473-L (in-train controls), AAR electro-pneumatic braking systems for freight trains, IFSF (European petrol station control), SEMI (semiconductor equipment manufacturing), and in 2005 as EN 14908 (European building automation standard). The protocol is also one of several data link/physical layers of the BACnet ASHRAE/ANSI standard for building automation.
China ratified the technology as a national controls standard, GB/Z 20177.1-2006 and as a building and intelligent community standard, GB/T 20299.4-2006; and in 2007 CECED, the European Committee of Domestic Equipment Manufacturers, adopted the protocol as part of its Household Appliances Control and Monitoring – Application Interworking Specification (AIS) standards.
During 2008 ISO and IEC have granted the communications protocol, twisted pair signaling technology, power line signaling technology, and Internet Protocol (IP) compatibility standard numbers ISO/IEC 14908-1, -2, -3, and -4.
By 2010 approximately 90 million devices were installed with LonWorks technology. Manufacturers in a variety of industries including building, home, street lighting, transportation, utility, and industrial automation have adopted the platform as the basis for their product and service offerings. Statistics as to the number of locations using the LonWorks technology are scarce, but it is known that products and applications built on top of the platform include such diverse functions as embedded machine control, municipal and highway/tunnel/street lighting, heating and air conditioning systems, intelligent electricity metering, subway train control, building lighting, stadium lighting and speaker control, security systems, fire detection and suppression, and newborn location monitoring and alarming, as well as remote power generation load control.
Two physical-layer signaling technologies, twisted pair "free topology" and power line carrier, are typically included in each of the standards created around the LonWorks technology. The two-wire layer operates at 78 kbit/s using differential Manchester encoding, while the power line achieves either 5.4 or 3.6 kbit/s, depending on frequency.
Additionally, the LonWorks platform uses an affiliated Internet protocol (IP) tunneling standard—ISO/IEC 14908-4 (ANSI/CEA-852) -- in use by a number of manufacturers to connect the devices on previously deployed and new LonWorks platform-based networks to IP-aware applications or remote network-management tools. Many LonWorks platform-based control applications are being implemented with some sort of IP integration, either at the UI/application level or in the controls infrastructure. This is accomplished with Web services or IP-routing products available in the market.
An Echelon Corporation-designed IC consisting of several 8-bit processors, the "Neuron chip" was initially the only way to implement a LonTalk protocol node and is used in the large majority of LonWorks platform-based hardware. Since 1999, the protocol has been available for general-purpose processors: A port of the ANSI/CEA-709.1 standard to IP-based or 32-bit chips.
Applications using LonWorks
- Semiconductor manufacturing
- Lighting control systems
- Energy management systems
- Heating/ventilation/air-conditioning systems
- Security systems
- Home automation
- Consumer appliance controls
- Public street lighting, monitoring, and control
- Petrol station control
- Rail Electronically Controlled Pneumatic Braking
SNVTs (Standard Network Variable Types)
One of the keys to the interoperability of the system is the standardisation of the variables used to describe physical things to LonWorks. This standards list is maintained by LonMark International and each standard is known as Standard Network Variable Types (SNVTs, pronounced "sniv-its"), so, for example, a thermostat using the temperature SNVT is expected to produce a number between zero and 65535 that corresponds to a temperature between -274 and 6279.5 degrees Celsius.
- BACnet a popular rival protocol. In 2014 Echelon Corporation, along with ConnectEx, Inc., announced the availability of BACnet over LonWorks as part of their IzoT Platform, allowing, for the first time, interoperability between previously rival protocols.
- KNX another popular rival protocol.
- Echelon Corporation
- LonMark International
- LonWorks en Español
- DTI - Examples of mixed ethernet and lonworks architectures
- LonWorks case study
- "LonWorks Technology Achieves ISO/IEC Standardization" (Press release). 2008-12-03. Retrieved 2014-02-11.
- http://www.echelon.com/support/documentation/manuals/transceivers/005-0154-01D.pdf PL3120/3150 transceiver data book, p5
- http://www.iso.org/iso/iso_catalogue/catalogue_tc/catalogue_detail.htm?csnumber=50360 IP Tunneling Protocol (International)
- "CEA-852.1 : IP Tunneling Protocol (USA)".
- http://www.lonmark.org/membership/directory/ Directory of LonMark International Member Companies
- "CEA-709.1 : Control Network Protocol Specification (USA)".