Micro combined heat and power
This article may be too technical for most readers to understand. Please help improve it to make it understandable to non-experts, without removing the technical details. (August 2015) (Learn how and when to remove this template message)
Micro combined heat and power, micro-CHP, µCHP or mCHP is an extension of the idea of cogeneration to the single/multi family home or small office building in the range of up to 50 kW. Usual technologies for the production of heat and power in one common process are e.g. internal combustion engines, micro gas turbines, stirling engines or fuel cells.
Local generation has the potential for a higher efficiency than traditional grid-level generators since it lacks the 8-10% energy losses from transporting electricity over long distances. It also lacks the 10–15% energy losses from heat transport in heating networks due to the difference between the thermal energy carrier (hot water) and the colder external environment.
The most common systems use natural gas as their primary energy source and emit carbon dioxide; nevertheless the effective efficiency of CHP heat production is much higher than of a condensing boiler, and thus reducing emissions and fuel costs.
A micro-CHP system usually contains a small heat engine as a prime mover used to rotate a generator which provides electric power, while simultaneously utilizing the waste heat from the prime mover for an individual building's space heating and the provision of hot domestic water. With fuel cells there is no rotating machinery, but the fuel cell's stack and where applicable also the reformer will provide useful heat. The stack does generate DC power which is converted by DC/AC inverter into mains voltage. Micro-CHP is defined by the EU as being of less than 50 kW electrical power output, however, others have more restrictive definitions, all the way down to <5 kWe.
A micro-CHP generator may primarily follow heat demand, delivering electricity as the by-product, or may follow electrical demand to generate electricity and use heat as the by-product. When used primarily for heating, micro-CHP systems may generate more electricity than is instantaneously being demanded, the surplus is then fed into the grid.
The purpose of cogeneration is to utilize more of the energy in the fuel. The reason for using CHP systems is that large thermal power plants which generate electric power by burning fuel produce between 40% to 60% low-temperature waste heat, due to Carnot's theorem. The temperature level (ca. 80°C - ca. 150°C) of this waste heat does allow to use it for space heating purposes, therefore in some urban areas district heating networks have been installed. Heat network have a limited extend, as it is not economical to transport heat long distances due to heat loss from the pipes, and it will not reach into areas of low population density, else revenues per CAPEX will go down. Where no district heating is possible due to low heat demand densities or the local utility did not invest in costly heat networks, this thermal energy is usually wasted via cooling tower or discharged in rivers, lakes or the sea.
Micro CHP systems allow to use the principle of highly efficient cogeneration while using the waste heat even if the served heat load is rather low. This allows to spread the idea of cogeneration beyond population centers or to use this efficient energy conversion principle even if a district heating network has not arrived yet. It is efficient to generate the electricity near where also the waste heat can be used. Small power plants (µCHP) are located in individual buildings, where the waste heat can be used to support the heating system and recharge the hot domestic water tank, thus saving heating oil or heating gas. CHP systems are able to increase the total energy utilization of primary energy sources. Thus CHP has been steadily gaining popularity in all sectors of the energy economy, due to the increased costs of electricity and fuel, particularly fossil fuels, and due to environmental concerns, particularly climate change.
In a traditional power plant delivering electricity to consumers, about 34.4% of the primary energy of the input fuel, such as coal, natural gas, uranium, petroleum solar thermal, or biomass, reaches the consumer via electricity, although the efficiency can be 20% for very old plants and 45% for newer gas plants. In contrast, a CHP system converts 15%–42% of the primary heat to electricity, and most of the remaining heat is captured for hot water or space heating. In total, over 90% of the heat from the primary energy source (LHV based) can be used when heat production does not exceed the thermal demand.
After the year 2000, micro-CHP has become cost effective in many markets around the world, due to rising energy costs. The development of micro-CHP systems has also been facilitated by recent technological developments of small heat engines. This includes improved performance and cost-effectiveness of fuel cells, Stirling engines, steam engines, gas turbines, diesel engines and Otto engines.
Combined heat and power (CHP) systems for homes or small commercial buildings are usually fueled by natural gas to produce electricity and heat. If no access to the natural gas network is available, which in general is the cheapest alternative, LPG, LNG or heating fuel (diesel) might be an alternative. PEMFC fuel cell mCHP operates at low temperature (50 to 100 °C) and needs high purity hydrogen, its prone to contamination, changes are made to operate at higher temperatures and improvements on the fuel reformer. SOFC fuel cell mCHP operates at a high temperature (500 to 1,000 °C) and can handle different fuel sources well but the high temperature requires expensive materials to handle the temperature, changes are made to operate at a lower temperature. Because of the higher temperature SOFC in general has a longer start-up time and need continuous heat output even in times when there is no thermal demand.
The fuel cell industry review stated in 2013 that with 64% of global sales the fuel cell micro-combined heat and power passed the conventional engine-based micro-CHP systems in sales in 2012.
Micro-CHP engine systems are currently based on several different technologies:
- Internal combustion engines
- Stirling engines
- Fuel cell
- Steam engine/Steam motor  (using either the traditional water or organic chemicals such as refrigerants)
There are many types of fuels and sources of heat that may be considered for micro-CHP. The properties of these sources vary in terms of system cost, heat cost, environmental effects, convenience, ease of transportation and storage, system maintenance, and system life. Some of the heat sources and fuels that are being considered for use with micro-CHP include: natural gas, LPG, biomass, vegetable oil (such as rapeseed oil), woodgas, solar thermal, and lately also hydrogen, as well as multi-fuel systems. The energy sources with the lowest emissions of particulates and net-carbon dioxide include solar power, hydrogen, biomass (with two-stage gasification into biogas), and natural gas. Due to the high efficiency of the CHP process, cogeneration has still lower carbon emissions compared to energy transformation in fossil driven boilers or thermal power plants.
The majority of cogeneration systems use natural gas for fuel, because natural gas burns easily and cleanly, it can be inexpensive, it is available in most areas and is easily transported through pipelines which already exist for over 60 million homes.
Reciprocating internal combustion engines are the most popular type of engine used in micro-CHP systems. Reciprocating internal combustion engine based systems can be sized such that the engine operates at a single fixed speed, usually resulting in a higher electrical or total efficiency. However, since reciprocating internal combustion engines have the ability to modulate their power output by changing their operating speed and fuel input, micro-CHP systems based on these engines can have varying electrical and thermal output designed to meet changing demand.
Natural gas is suitable for internal combustion engines, such as Otto engine and gas turbine systems. Gas turbines are used in many small systems due to their high efficiency, small size, clean combustion, durability and low maintenance requirements. Gas turbines designed with foil bearings and air-cooling operate without lubricating oil or coolants. The waste heat of gas turbines is mostly in the exhaust, whereas the waste heat of reciprocating internal combustion engines is split between the exhaust and cooling system.
External combustion engines can run on any high-temperature heat source. These engines include the Stirling engine, hot "gas" turbocharger, and the steam engine. Both range from 10%-20% efficiency, and as of 2014, small quantities are in production for micro-CHP products.
Other possibilities include the Organic Rankine cycle, which operates at lower temperatures and pressures using low-grade heat sources. The primary advantage to this is that the equipment is essentially an air-conditioning or refrigeration unit operating as an engine, whereby the piping and other components need not be designed for extreme temperatures and pressures, reducing cost and complexity. Electrical efficiency suffers, but it is presumed that such a system would be utilizing waste heat or a heat source such as a wood stove or gas boiler that would exist anyway for purposes of space heating.
The future of combined heat and power, particularly for homes and small businesses, will continue to be affected by the price of fuel, including natural gas. As fuel prices continue to climb, this will make the economics more favorable for energy conservation measures, and more efficient energy use, including CHP and micro-CHP.
Fuel cells generate electricity and heat as a by product. The advantages for a stationary fuel cell application over stirling CHP are no moving parts, less maintenance, and quieter operation. The surplus electricity can be delivered back to the grid.
PEMFC fuel cells fueled by natural gas or propane use a steam reformer to convert methane in the gas supply into carbon dioxide and hydrogen; the hydrogen then reacts with oxygen in the fuel cell to produce electricity. A PEMFC fuel cell based micro-CHP has an electrical efficiency of 37% LHV and 33% HHV and a heat recovery efficiency of 52% LHV and 47% HHV with a service life of 40,000 hours or 4000 start/stop cycles which is equal to 10 year use. An estimated 138,000 Fuel cell CHP systems below 1 kW had been installed in Japan by the end of 2014. Most of these CHP systems are PEMFC based (85%) and the remaining are SOFC systems.
|Electrical efficiency at rated power2||34%||40%||42.5%||45%|
|CHP energy efficiency3||80%||85%||87.5%||90%|
|Transient response (10%–90% rated power)||5 min||4 min||3 min||2 min|
|Start-up time from 20 °C ambient temperature||60 min||45 min||30 min||20 min|
|Degradation with cycling5||< 2%/1000 h||0.7%/1000 h||0.5%/1000 h||0.3%/1000 h|
|Operating lifetime6||6,000 h||30,000 h||40,000 h||60,000 h|
1Standard utility natural gas delivered at typical residential distribution line pressures. 2Regulated AC net/lower heating value of fuel. 3Only heat available at 80 °C or higher is included in CHP energy efficiency calculation. 4Cost includes materials and labor costs to produce stack, plus any balance of plant necessary for stack operation. Cost defined at 50,000 unit/year production (250 MW in 5 kW modules). 5Based on operating cycle to be released in 2010. 6Time until >20% net power degradation.
Thermoelectric generators operating on the Seebeck Effect show promise due to their total absence of moving parts. Efficiency, however, is the major concern as most thermoelectric devices fail to achieve 5% efficiency even with high temperature differences.
This can be achieved by Photovoltaic thermal hybrid solar collector, another option is Concentrated photovoltaics and thermal (CPVT), also sometimes called combined heat and power solar (CHAPS), is a cogeneration technology used in concentrated photovoltaics that produce both electricity and heat in the same module. The heat may be employed in district heating, water heating and air conditioning, desalination or process heat.
Sopogy produces a micro concentrated solar power (microCSP) system based on parabolic trough which can be installed above building or homes, the heat can be used for water heating or solar air conditioning, a steam turbine can also be installed to produce electricity.
The recent development of small scale CHP systems has provided the opportunity for in-house power backup of residential-scale photovoltaic (PV) arrays. The results of a recent study show that a PV+CHP hybrid system not only has the potential to radically reduce energy waste in the status quo electrical and heating systems, but it also enables the share of solar PV to be expanded by about a factor of five. In some regions, in order to reduce waste from excess heat, an absorption chiller has been proposed to utilize the CHP-produced thermal energy for cooling of PV-CHP system. These trigen+PV systems have the potential to save even more energy.
To date, micro-CHP systems achieve much of their savings, and thus attractiveness to consumers, by the value of electrical energy which is replaced by the autoproduced electricity. A "generate-and-resell" or net metering model supports this as home-generated power exceeding the instantaneous in-home needs is sold back to the electrical utility. This system is efficient because the energy used is distributed and used instantaneously over the electrical grid. The main losses are in the transmission from the source to the consumer which will typically be less than losses incurred by storing energy locally or generating power at less than the peak efficiency of the micro-CHP system. So, from a purely technical standpoint dynamic demand management and net-metering are very efficient.
Another positive to net-metering is the fact that it is fairly easy to configure. The user's electrical meter is simply able to record electrical power exiting as well as entering the home or business. As such, it records the net amount of power entering the home. For a grid with relatively few micro-CHP users, no design changes to the electrical grid need be made. Additionally, in the United States, federal and now many state regulations require utility operators to compensate anyone adding power to the grid. From the standpoint of grid operator, these points present operational and technical as well as administrative burdens. As a consequence, most grid operators compensate non-utility power-contributors at less than or equal to the rate they charge their customers. While this compensation scheme may seem almost fair at first glance, it only represents the consumer's cost-savings of not purchasing utility power versus the true cost of generation and operation to the micro-CHP operator. Thus from the standpoint of micro-CHP operators, net-metering is not ideal.
While net-metering is a very efficient mechanism for using excess energy generated by a micro-CHP system, it does have detractors. Of the detractors' main points, the first to consider is that while the main generating source on the electrical grid is a large commercial generator, net-metering generators "spill" power to the smart grid in a haphazard and unpredictable fashion. However, the effect is negligible if there are only a small percentage of customers generating electricity and each of them generates a relatively small amount of electricity. When turning on an oven or space heater, about the same amount of electricity is drawn from the grid as a home generator puts out. If the percentage of homes with generating systems becomes large, then the effect on the grid may become significant. Coordination among the generating systems in homes and the rest of the grid may be necessary for reliable operation and to prevent damage to the grid.
The largest deployment of micro-CHP is in Japan in 2009 where over 90,000 units in place, with the vast majority being of Honda's "ECO-WILL" type. Six Japanese energy companies launched the 300 W–1 kW PEMFC/SOFC ENE FARM product in 2009, with 3,000 installed units in 2008, a production target of 150,000 units for 2009–2010 and a target of 2,500,000 units in 2030. 20,000 units where sold in 2012 overall within the Ene Farm project making an estimated total of 50,000 PEMFC and up to 5,000 SOFC installations. For 2013 a state subsidy for 50,000 units is in place. The ENE FARM project will pass 100.000 systems in 2014, 34.213 PEMFC and 2.224 SOFC were installed in the period 2012-2014, 30,000 units on LNG and 6,000 on LPG.
Sold by various gas companies and as of 2013, installed in a total of 131,000 homes. Manufactured by Honda using their single cylinder EXlink engine capable of burning natural gas or propane. Each unit produces 1 kW of electricity and 2.8 kW of hot water.
- Per December 2012, Panasonic and Tokyo Gas Co., Ltd. sold about 21,000 PEM Ene-Farm units in Japan for a price of $22,600 before installation.
- Toshiba and Osaka Gas Co., Ltd./Nichigas installed 6,500 PEM ENE FARM units (manufactured by CHOFU SEISAKUSHO Co.,Ltd. ) per November 2011.
- In the middle of 2012, JX Nippon Oil Co. & Sanyo and Seibu Gas Energy Co. sold around 4,000 SOFC Ene Farm units.
- Aisin Seiki in combination with Osaka Gas, Kyocera, Toyota and Chofu Seisakusho started in April 2012 with the sales of the SOFC ENE-FARM Type S for around $33,500 before installation.
- NGK is a manufacturer of 700W-1 Kw mCHP units.
- Miura Kogyo and Sumitomo Precision Products with a 4.2 Kw unit.
- Toto Ltd.
In South Korea, subsidies will start at 80 percent of the cost of a domestic fuel cell. The Renewable Portfolio Standard program with renewable energy certificates runs from 2012 to 2022. Quota systems favor large, vertically integrated generators and multinational electric utilities, if only because certificates are generally denominated in units of one megawatt-hour. They are also more difficult to design and implement than a Feed-in tariff. Around 350 residential mCHP units were installed in 2012.
- PEMFC by GS FuelCell, FuelCell Power, Hyundai Hysco JV with Plug Power and Hyosung,
- SOFC by KEPRI, LS Industrial Systems (from ClearEdge Power), Samsung Everland (ClearEdge Power).
- MCFC by POSCO Energy (FuelCell Energy)  and Doosan.
- PAFC Doosan Fuel Cell America
- AFC AFC Energy
The European public–private partnership Fuel Cells and Hydrogen Joint Undertaking Seventh Framework Programme project ene.field aims to deploy by 2017 up 1,000 residential fuel cell Combined Heat and Power (micro-CHP) installations in 12 EU member states.
- The programme brings together 9 mature European micro FC-CHP manufacturers into a common analysis framework to deliver trials across all of the available fuel cell CHP technologies. Fuel cell micro-CHP trials will be installed and actively monitored in dwellings across the range of European domestic heating markets, dwelling types and climatic zones, which will lead to an invaluable dataset on domestic energy consumption and micro-CHP applicability across Europe.
- The ene.field project also brings together over 30 utilities, housing providers and municipalities to bring the products to market and explore different business models for micro-CHP deployment.
Powercell Sweden is a fuel cell company that develop environmentally friendly electric generators with the unique fuel cell and reformer technology that is suitable for both existing and future fuel.
In Germany, ca 50 MW of mCHP up to 50 kW units have been installed in 2015. The German government is offering large CHP incentives, including a market premium on electricity generated by CHP and an investment bonus for micro-CHP units. The German testing project Callux has 500 mCHP installations per nov 2014. North Rhine-Westphalia launched a 250 million subsidy program for up to 50 kW lasting until 2017.
- BDR Thermea/BAXI (Toshiba)
- Viessmann (Panasonic)
- Elcore, a 300W addon.
- Tropical 
- Dantherm Power
- Riesaer Brennstoffzellentechnik GmbH (Inhouse Engineering)
- Center for Fuel Cell Technology (ZBT) (JX Nippon)
- Ceramic Fuel Cells installs until 2014 up to 100 SOFC units under the SOFT-PACT project with E.ON in Germany and the UK. A factory in Heinsberg, Germany for the production of SOFC based micro-CHP units started in June 2009 to produce 10,000 two-kilowatt units per year.
- Vaillant (Sunfire/Staxera)
- Buderus/Junkers – Bosch Thermotechnik (Aisin Seiki)
- Itho-Daalderop (Ceres Power)
- Viessmann (HEXIS),
It is estimated that about 1,000 micro-CHP systems were in operation in the UK as of 2002. These are primarily Whispergen using Stirling engines, and Senertec Dachs reciprocating engines. The market is supported by the government through regulatory work, and some government research money expended through the Energy Saving Trust and Carbon Trust, which are public bodies supporting energy efficiency in the UK. Effective as of 7 April 2005, the UK government has cut the VAT from 20% to 5% for micro-CHP systems, in order to support demand for this emerging technology at the expense of existing, less environmentally friendly technology. The reduction in VAT is effectively a 10.63% subsidy for micro-CHP units over conventional systems, which will help micro-CHP units become more cost competitive, and ultimately drive micro-CHP sales in the UK. Of the 24 million households in the UK, as many as 14 to 18 million are thought to be suitable for micro-CHP units. Two fuel cell varieties of mCHP co-generation units are almost ready for mainstream production and are planned for release to commercial markets in early in 2014. With the UK Government's Feed-In-Tariff available for a 10-year period, a wide uptake of the technology is anticipated.
- In early 2012 less than 1000 1 kWe Baxi-Innotech  PEM micro-CHP units from BDR Thermea were installed 
- A Ceres Power factory in Horsham UK for the production of SOFC based micro-CHP units is expected to start low-volume production in the second half of 2009
- Ceramic Fuel Cells
The micro-CHP subsidy was ended in 2012. To test the effects of mCHP on a smart grid, 45 natural gas SOFC units (each 1,5 kWh) from Republiq Power (Ceramic Fuel Cells) will be placed on Ameland in 2013 to function as a virtual power plant.
This section needs to be updated.July 2019)(
In 2007, the United States company "Climate Energy" of Massachusetts introduced the "Freewatt, a micro-CHP system based on a Honda MCHP engine bundled with a gas furnace (for warm air systems) or boiler (for hydronic or forced hot water heating systems).
Marathon Engine Systems, a Wisconsin company, produces a variable electrical and thermal output micro-CHP system called the ecopower with an electrical output of 2.2-4.7 kWe. The ecopower was independently measured to operate at 24.4% and 70.1% electrical and waste heat recovery efficiency, respectively.
This section needs to be updated.July 2019)(
- Hyteon PEM 
Through a pilot program scheduled for mid-2009 in the Canadian province of Ontario, the Freewatt system is being offered by home builder Eden Oak with support from ECR International, Enbridge Gas Distribution and National Grid.
Testing is underway in Ameland, the Netherlands for a three-year field testing until 2010 of HCNG where 20% hydrogen is added to the local CNG distribution net, the appliances involved are kitchen stoves, condensing boilers, and micro-CHP boilers.
Micro-CHP Accelerator, a field trial performed between 2005 and 2008, studied the performance of 87 Stirling engine and internal combustion engine devices in residential houses in the UK. This study found that the devices resulted in average carbon savings of 9% for houses with heat demand over 54 GJ/year.
An ASME (American Society of Mechanical Engineers) paper fully describes the performance and operating experience with two residential sized Combined Heat and Power units which were in operation from 1979 through 1995.
Oregon State University, funded by the U.S. Department of Energy's Advanced Research Project Agency - Energy (ARPA-e), tested the state of the art micro-CHP systems in the United States. The results showed that the nominally 1 kWe state-of-the-art micro-CHP system operated at an electrical and total efficiency (LHV based) of 23.4 and 74.4%, respectively. The nominally 5 kWe state-of-the-art system operated at an electrical and total efficiency (LHV based) of 24.4 and 94.5%, respectively. The most popular 7 kWe home backup generator (not CHP) operated at an electrical efficiency (LHV based) of 21.5%. The price of the emergency backup generator was an order of magnitude lower than the 5 kWe generator, but the projected life span of the system was over 2 orders of magnitude lower. These results show the trade-off between efficiency, cost, and durability.
The U.S. Department of Energy's Advanced Research Project Agency - Energy (ARPA-e) has funded $25 million towards mCHP research in the GENerators for Small Electrical and Thermal Systems (GENSETS) program. 12 project teams have been selected to develop a 1 kWe mCHP technology that can achieve 40% electrical efficiency, have a 10-year system life, and cost under $3000.
- Distributed generation
- District heating
- Feed-in tariff
- Geothermal power in Iceland
- Grid-tied electrical system
- Home fuel cell
- Pinch analysis
- Relative cost of electricity generated by different sources
- Stationary fuel cell applications
- Timeline of hydrogen technologies
- Virtual power plant
- "DIRECTIVE 2012/27/EU on energy efficiency, Article 2(39)". eur-lex.europa.eu. 2012-10-25. Retrieved 2017-08-11.
- Micro Cogeneration - Towards Decentralized Energy Systems | Martin Pehnt | Springer. Springer. 2006. ISBN 9783540255826.
- De Paepe, Michel; D’Herdt, Peter; Mertens, David (2006-11-01). "Micro-CHP systems for residential applications". Energy Conversion and Management. 47 (18): 3435–3446. doi:10.1016/j.enconman.2005.12.024.
- A., Çengel, Yunus (2014-01-07). Thermodynamics : an engineering approach. Boles, Michael A. (Eighth ed.). New York. ISBN 978-0073398174. OCLC 869741544.
- Notter, Dominic A.; Kouravelou, Katerina; Karachalios, Theodoros; Daletou, Maria K.; Haberland, Nara Tudela (2015). "Life cycle assessment of PEM FC applications: electric mobility and μ-CHP". Energy Environ. Sci. 8 (7): 1969–1985. doi:10.1039/C5EE01082A.
- "State Electricity Profiles - Energy Information Administration". www.eia.gov. Retrieved 2017-08-11.
- Rosato, A.; Sibilio, S. (2012-12-01). "Calibration and validation of a model for simulating thermal and electric performance of an internal combustion engine-based micro-cogeneration device". Applied Thermal Engineering. 45: 79–98. doi:10.1016/j.applthermaleng.2012.04.020.
- Experimental investigation of residential cogeneration devices and calibration of Annex 42 models : a report of Subtask B of FC+COGEN-SIM, the Simulation of Building-1ntegrated Fuel Cell and Other Cogeneration Systems, Annex 42 of the International Energy Agency Energy Conservation in Buildings and Community Systems Programme. Beausoleil-Morrison, Ian., Arndt, Ulli., Canada. Natural Resources Canada., IEA Energy Conservation in Buildings & Community Systems Programme. Annex 42--Simulation of Building-Integrated Fuel Cell and Other Cogeneration Systems. [Ottawa]: [Natural Resources Canada]. 2007. ISBN 9780662475231. OCLC 226302449.CS1 maint: others (link)
- de Santoli, Livio; Basso, Gianluigi Lo; Albo, Angelo; Bruschi, Daniele; Nastasi, Benedetto (2015-12-01). "Single Cylinder Internal Combustion Engine Fuelled with H2NG Operating as Micro-CHP for Residential Use: Preliminary Experimental Analysis on Energy Performances and Numerical Simulations for LCOE Assessment" (PDF). Energy Procedia. 69th Conference of the Italian Thermal Engineering Association, ATI 2014. 81: 1077–1089. doi:10.1016/j.egypro.2015.12.130.
- Roselli, Carlo; Sasso, Maurizio; Sibilio, Sergio; Tzscheutschler, Peter (2011-04-01). "Experimental analysis of microcogenerators based on different prime movers". Energy and Buildings. 43 (4): 796–804. doi:10.1016/j.enbuild.2010.11.021.
- Thomas, Bernd (March 2008). "Benchmark Testing of Micro-CHP units". Applied Thermal Engineering. 28 (16): 2049–2054. doi:10.1016/j.applthermaleng.2008.03.010.
- Angrisani, G.; Roselli, C.; Sasso, M. (2012-08-01). "Distributed microtrigeneration systems". Progress in Energy and Combustion Science. 38 (4): 502–521. doi:10.1016/j.pecs.2012.02.001.
- Tri-Generation success story Archived March 4, 2016, at the Wayback Machine
- The role of micro CHP in a smart energy world Archived March 4, 2016, at the Wayback Machine
- Micro CHP report powers heated discussion about UK energy future Archived March 20, 2016, at the Wayback Machine
- The fuel cell industry review 2013 Archived April 14, 2016, at the Wayback Machine
- Ellamla H.R.; Staffell, I; Bujlo, P; Pollet, BG; Pasupathi, S (28 May 2015). "Current status of fuel cell based combined heat and power systems for residential sector". Journal of Power Sources. 293 (C): 312–328. Bibcode:2015JPS...293..312E. doi:10.1016/j.jpowsour.2015.05.050.
- Du, R.; Robertson, P. (2017). "Cost Effective Grid-Connected Inverter for a Micro Combined Heat and Power System" (PDF). IEEE Transactions on Industrial Electronics. 64 (7): 5360–5367. doi:10.1109/TIE.2017.2677340. ISSN 0278-0046.
- Dorer, Viktor; Weber, Andreas (2009-03-01). "Energy and carbon emission footprint of micro-CHP systems in residential buildings of different energy demand levels". Journal of Building Performance Simulation. 2 (1): 31–46. doi:10.1080/19401490802596435. ISSN 1940-1493.
- Dorer, Viktor; Weber, Andreas (2009-03-01). "Energy and CO2 emissions performance assessment of residential micro-cogeneration systems with dynamic whole-building simulation programs". Energy Conversion and Management. 50 (3): 648–657. doi:10.1016/j.enconman.2008.10.012.
- "U.S. Number of Natural Gas Consumers". www.eia.gov. Retrieved 2017-08-11.
- "ecopower® Cogeneration by Marathon Engine Systems". www.marathonengine.com. Retrieved 2017-08-11.
- Integration of fuel cell micro-CHPs on low voltage grid: A Danish case study Archived March 4, 2016, at the Wayback Machine
- "Osaka Gas' fuel processing system for ENE・FARM | residential polymer electrolyte fuel cell (PEFC) cogeneration system | OSAKA GAS". Archived from the original on 2016-01-16. Retrieved 2015-08-14.
- Latest developments in the Ene-Farm scheme Archived April 14, 2016, at the Wayback Machine
- DOE Distributed/Stationary fuel cell systems Archived November 6, 2014, at the Wayback Machine
- Renewable Energy World-Researchers explore hybrid concentrated solar energy system Archived December 20, 2014, at the Wayback Machine
- "Zenith Solar Projects – Yavne". zenithsolar.com. 2011. Archived from the original on April 15, 2011. Retrieved May 14, 2011.
- J. M. Pearce (2009). "Expanding Photovoltaic Penetration with Residential Distributed Generation from Hybrid Solar Photovoltaic + Combined Heat and Power Systems". Energy. 34 (11): 1947–1954. CiteSeerX 10.1.1.593.8182. doi:10.1016/j.energy.2009.08.012. hdl:1974/5307.
- A. Nosrat; J. M. Pearce (2011). "Dispatch Strategy and Model for Hybrid Photovoltaic and Combined Heating, Cooling, and Power Systems". Applied Energy. 88 (9): 3270–3276. CiteSeerX 10.1.1.593.5625. doi:10.1016/j.apenergy.2011.02.044. hdl:1974/6439.
- "Honda Worldwide | July 17, 2007 "Honda's Compact Household Cogeneration Unit Achieves Cumulative Sales of 50,000 units in Japan"". World.honda.com. Archived from the original on June 15, 2012. Retrieved 2012-06-12.
- Micro CHP in Japan
- (in English) Japan 2005-2008 mchp[dead link]
- FCgen-1030V3 Archived July 7, 2011, at the Wayback Machine
- ENE FARM residential fuel cells launched Archived June 16, 2012, at the Wayback Machine
- The IEA CHP and DHC Collaborative Archived March 3, 2016, at the Wayback Machine
- Enfarm enefield eneware Archived February 15, 2016, at the Wayback Machine
- "Honda Global | Honda Motor Co.,LTD". Archived from the original on 2016-11-21. Retrieved 2015-03-29.
- Launch of new 'Ene-Farm' home fuel cell product more affordable and easier to install Archived July 10, 2014, at the Wayback Machine
- Features of the Panasonic household fuel cell Archived March 29, 2016, at the Wayback Machine
- Nichigas Ene Farm Archived November 9, 2013, at the Wayback Machine
- Toshiba revamps 'Ene Farm' residential fuel cell Archived March 3, 2016, at the Wayback Machine
- Toshiba revamps 'Ene Farm' residential fuel cell Archived March 3, 2016, at the Wayback Machine
- The latest news number 196, 2012 FCDIC Archived March 5, 2016, at the Wayback Machine
- ENE-FARM Type S Archived March 17, 2016, at the Wayback Machine
- Development of SOFC for residential use[permanent dead link]
- Miura Archived May 4, 2016, at the Wayback Machine
- Toto Ltd[permanent dead link]
- South Korea unveils 80 per cent subsidy for domestic fuel cells Archived March 17, 2010, at the Wayback Machine
- R&D status and prospects on fuel cells in Korea Archived December 5, 2013, at the Wayback Machine
- Renewable Energy Policy Mechanisms by Paul Gipe Archived May 10, 2012, at the Wayback Machine(1.3MB)
Lauber, V. (2004). "REFIT and RPS: Options for a harmonized Community framework," Energy Policy, Vol. 32, Issue 12, pp.1405–1414.
Lauber, V. (2008). "Certificate Trading – Part of the Solution or Part of the Problem?" Ljubljana Conference on the Future of GHG Emissions Trading in the EU, March 2008. Salzburg, Austria: University of Salzburg. Retrieved 16 March 2009 at: www.uni-salzburg.at/politikwissenschaft/lauber
- The fuel cell industry review 2012 Archived July 1, 2016, at the Wayback Machine
- GS Fuelcell Co., Ltd Archived March 3, 2016, at the Wayback Machine
- FuelCell Power Archived July 7, 2014, at the Wayback Machine
- Hyundai Hysco Archived January 31, 2015, at the Wayback Machine
- Hyosung’s 1kW low temperature PEMFC System Archived March 4, 2016, at the Wayback Machine
- Kepri Archived July 9, 2015, at the Wayback Machine
- 2009-Initial stage of commercialization of residential fuel cells in Korea Archived March 4, 2016, at the Wayback Machine
- 5th stakeholders general assembly of the FCH JU Archived November 10, 2013, at the Wayback Machine
- ene.field Archived October 2, 2016, at the Wayback Machine
- European-wide field trials for residential fuel cell micro-CHP Archived November 9, 2016, at the Wayback Machine
- ene.field Grant No 303462 Archived November 10, 2013, at the Wayback Machine
- BAFA: Official statistics on CHP units commissioned per year, downloaded 2016-03-12[permanent dead link]
- North Rhine-Westphalia government launches capital subsidy for micro-CHP Archived November 9, 2013, at the Wayback Machine
- Number 211-2013 FDIC -Viesmann-Panasonic Archived October 6, 2014, at the Wayback Machine
- Elcore – Elcomax
- Handling the cost of residential fuel cells Archived April 6, 2016, at the Wayback Machine
- Tropical Archived April 4, 2016, at the Wayback Machine
- ZBT Archived March 27, 2016, at the Wayback Machine
- Solid oxide fuel cell micro-CHP field trials Archived October 6, 2014, at the Wayback Machine
- Ceramic fuel cells Archived June 29, 2016, at the Wayback Machine
- Sunfire Archived November 28, 2016, at the Wayback Machine
- Buderus Logapower FC10 energy centre supplies both heat and electricity Archived February 9, 2015, at the Wayback Machine
- Hexis Archived May 20, 2016, at the Wayback Machine
- Viessmann has announced two separate deals with Hexis Archived March 18, 2016, at the Wayback Machine
- CHP–The microgeneration boom? Archived January 6, 2009, at the Wayback Machine
- Not 12.5% as could be primarily thought: a subsidized system cost 105/117.5% of a normal, the différence being 12.5/117.5 = 10.63%
- The role of micro CHP in a smart energy world = March 2013 Archived March 4, 2016, at the Wayback Machine
- BAXI-Innotech Archived February 5, 2015, at the Wayback Machine
- Micro-CHP Japan continues to lead as fuel cell units emerge Archived January 11, 2016, at the Wayback Machine
- .Ceres Power signs fuel cell CHP assembly deal with Daalderop Archived March 20, 2016, at the Wayback Machine
- Demonstration of micro CHP based on Danish fuel cells Archived November 6, 2014, at the Wayback Machine
- "Methaanbrandstoffen op Ameland" (PDF) (in Dutch). Archived from the original (PDF) on 2013-11-01.
- ANnalysis of data collected for the Freewatt microCHP system in Syracuse, NY Archived April 2, 2015, at the Wayback Machine
- Taie, Z., Hagen, C. (2016). ARPA-e Final Scientific/Technical Report - Home Generator Benchmarking Program. Oregon State University. Bend, Oregon.
- Taie, Zachary; West, Brian; Szybist, James; Edwards, Dean; Thomas, John; Huff, Shean; Vishwanathan, Gokul; Hagen, Christopher (2018-06-15). "Detailed thermodynamic investigation of an ICE-driven, natural gas-fueled, 1 kWe micro-CHP generator". Energy Conversion and Management. 166: 663–673. doi:10.1016/j.enconman.2018.04.077. ISSN 0196-8904. OSTI 1436052.
- Taie, Zachary; Hagen, Christopher (2019-01-15). "Experimental thermodynamic first and second law analysis of a variable output 1–4.5 kWe, ICE-driven, natural-gas fueled micro-CHP generator". Energy Conversion and Management. 180: 292–301. doi:10.1016/j.enconman.2018.10.075. ISSN 0196-8904.
- Hyteon Archived March 3, 2016, at the Wayback Machine
- "New Homes & Spectacular Communities in Southern Ontario".
- "ECR International | A Family of Heating & Cooling Brands".
- "Huge savings claimed by new system". 20 September 2008. Archived from the original on 2015-04-02. Retrieved 2015-03-29.
- Micro-CHP Archived February 27, 2012, at the Wayback Machine
- Ameland Field testing
- Carbon Trust (2011). Micro-CHP Accelerator (PDF) (Report).
- Frederick R. Rosse: EXPERIENCE WITH EARLY DISTRIBUTED GENERATION SYSTEMS Archived March 14, 2016, at the Wayback Machine, Proceedings of IJPC-2003 2003 International Joint Power Conference, paper IJPGC2003-40192
- "GENSETS". ARPA-e. Retrieved 11 August 2017.
- "DEPARTMENT OF ENERGY ANNOUNCES 18 NEW PROJECTS TO ACCELERATE TECHNOLOGIES FOR EFFICIENT RESIDENTIAL COMBINED HEAT AND POWER GENERATION AND BIOENERGY CROP DEVELOPMENT". ARPA-e. Retrieved 11 August 2017.
Codes and standards
- Fuel cell gas appliances up to 70 kW
- Installation permitting guidance for hydrogen and fuel cells stationary applications
- Standard for the installation of stationary fuel cell power systems