This article includes a list of references, but its sources remain unclear because it has insufficient inline citations. (November 2019) (Learn how and when to remove this template message)
A phase converter is a device that converts electric power provided as single phase to multiple phase or vice versa. The majority of phase converters are used to produce three-phase electric power from a single-phase source, thus allowing the operation of three-phase equipment at a site that only has single-phase electrical service. Phase converters are used where three-phase service is not available from the utility, or is too costly to install due to a remote location. A utility will generally charge a higher fee for a three-phase service because of the extra equipment, including transformers, metering, and distribution wire.
Three-phase induction motors may operate adequately on an unbalanced supply if not heavily loaded. This allows various imperfect techniques to be used. A single-phase motor can drive a three-phase generator, which will produce a high-quality three-phase source but with high cost for apparatus. Several methods exist to run three-phase motors from a single-phase supply, these can in general be classified as:
- Rotary phase converters constructed from a three-phase electric motor or generator "idler". These normally require some kind of starting aid and capacitors to improve phase balance and power factor. This is a two-motor solution. One motor is not connected to a load and produces the three-phase power, the second motor driving the load runs on the power produced.
- Electronic means of creating three phases where the incoming power is rectified, and the three-phase power is synthesized with electronics. Power electronic devices directly produce a three-phase waveform from single-phase power, using a rectifier and inverter combination. This also offers the advantage of variable frequency.
- A digital phase converter uses a rectifier and inverter to create a single voltage with power electronics, which is added to the two legs of the single-phase source to create three-phase power. Unlike a phase converting VFD, it cannot vary the frequency and motor speed, since it generates only one leg, which must match the voltage and frequency of the single-phase supply. It does have the advantage of a sine-wave output voltage and excellent voltage balance between the phases. More details about these methods are explained in the phase conversion patents Medagam et. al. “Active Single Phase to Three Phase Power Converter” US Patent 10,333,420 and Meiners et. al. “Phase Converter” US 6,297,971.[promotion?]
- Static conversion techniques in which the motor is run at less than full efficiency mainly on two of the legs of the three-phase motor. Current is sometimes injected into the third leg with a capacitor or transformer arrangements that provide imperfect phase shift. In these systems the motor must be derated.
- Methods in which the connection of the windings of the motor, normally a wye or delta configurations, are replaced with novel connections. These techniques are covered in patents of Dr. Otto J. M. Smith, such as US Patent 5,545,965.[promotion?]
Rotary phase converter
This section does not cite any sources. (January 2020) (Learn how and when to remove this template message)
A rotary phase converter is an economical way to create three-phase power in an area where three-phase utility power is not available or is cost-prohibitive to bring in. A rotary phase converter uses a control panel with a start circuit and run circuit to create balanced, clean power without excessive voltage. A three-phase motor produces the third leg of power. Some rotary phase converters are digitally controlled, enabling them to produce balanced power that is clean enough to run on voltage-sensitive loads such as a CNC machine, welder, or any other computer-controlled load.
A rotary phase converter does not change the voltage, but it can be paired with a transformer to step the voltage up or down depending on what is needed.
A digital phase converter creates a three-phase power supply from a single-phase supply. A digital signal processor (DSP) is used to control power electronic devices to generate a third voltage, which along with the single voltage from the supply creates a balanced three-phase power supply.
In one type of digital phase converter, the input rectifier consists of IGBTs in series with inductors. The IGBTs are controlled by software in the DSP to draw current from the single-phase line in a sinusoidal fashion, charging capacitors on a constant-voltage DC bus. Because the incoming current is sinusoidal, there are no significant harmonics generated back onto the line as there are with the rectifiers found in most VFDs. The controlled rectifier input allows power factor correction.
The output inverter consists of IGBTs that draw on the power of the DC bus to create an AC voltage. A voltage created by power-switching devices like IGBTs is not sinusoidal. It is a pulse-width modulated (PWM) waveform very high in harmonic distortion. This PWM voltage is then passed through an inductor/capacitor filter system that produces a sine-wave voltage with less than 3% total harmonic distortion (standards for computer grade power allow up to 5% THD). By contrast, VFDs generate a PWM voltage that limits their versatility and makes them unsuitable for many applications. Software in the DSP continually monitors and adjusts this generated voltage to produce a balanced three-phase output at all times. It also provides protective functions by shutting down in case of utility over-voltage and under-voltage or a fault. With the ability to adjust to changing conditions and maintain voltage balance, a digital phase converter can safely and efficiently operate virtually any type of three-phase equipment or any number of multiple loads.
The solid-state design results in a relatively small package with no moving parts except for small cooling fans. Digital phase converters operate at 98.7% efficiency., unlike rotary phase converters at an average of only 70-80%. When the converter is energized with no load, it consumes very little power.
In Europe, electricity is normally generated as three-phase AC at 50 hertz. Five European countries: Germany, Austria, Switzerland, Norway and Sweden have standardized on single-phase AC at 15 kV 16⅔ Hz for railway electrification. Phase converters are, therefore, used to change both the phase and the frequency.
- "3-Phase Converter Transformer", Agile Magnetics, Retrieved June 8, 2016
- U.S. Patent 5,545,965 13 August 1996. Three phase motor operated from a single phase power supply and phase converter. Otto J. M. Smith
- "Digital Phase Converters", Phase Technologies, Retrieved June 8, 2016
- "Phase Perfect". www.phasetechnologies.com. Retrieved 2020-05-02.
- "Downloads". www.phasetechnologies.com. Retrieved 2020-05-02.
- RadioWorld Magazine featured article: Harris Impressed by Phase Technologies PT355 by Terry Cockerill, 12.31.2009 
- Wine Business Monthly featured article: What's Cool: Digital Phase Converters November 15, 2008 Whats Cool: Digital Phase Converters
- January/February 2008 Vineyard & Winery Management Magazine Featured article "The Digital Converter; A New Way to Generate Three-Phase Electricity for a Winery"] by Ben Guthrie.
- United States Patent #6297971
- Digital-to-phase-converter - US Patent 7050467 Abstract
- Circuit and method for reducing inrush current of phase converter motor "Circuit and Method for Reducing Inrush Current of Phase Converter Motor" Inventor Glen Floreancig, Phoenix Phase Converters.
- US Patent for Active single phase to three phase power converter Patent (Patent # 10,333,420 issued June 25, 2019) - Justia Patents Search
- Phase converter