R-407C is a mixture of hydrofluorocarbons used as a refrigerant. It is a zeotropic blend of difluoromethane (R-32), pentafluoroethane (R-125), and 1,1,1,2-tetrafluoroethane (R-134a). Difluoromethane serves to provide the heat capacity, pentafluoroethane decreases flammability, tetrafluoroethane reduces pressure. R-407C cylinders are colored burnt orange.
It is not recommended to drop R-407C into R-22 systems on top of the existing charge in cases of low refrigerant levels. A licensed professional should be contracted to completely remove the R-22 and as much of the mineral oil as possible. In the case of compressor change-outs, replacement compressors are already manufactured with POE (polyolester) oil and are therefore more compatible with R-407C than returning the recovered R-22. The recovered R-22 can be sent to a facility for disposal.
It is cost effective to replace R-22 with R-407C before there is an emergency. Preventive maintenance programs should include strong suggestions to replace ozone-depleting refrigerants such as R-22 with environmentally friendly refrigerants and it seems that R-407C has become the front runner.
There are many millions of tons of R-22 in air conditioning and refrigeration equipment in use today and most of it is destined to end up in the atmosphere in spite of efforts to curtail this probability. These efforts have been in place since the late 1980s.
|Molecular Weight (kg/kmol)||86.2|
|Boiling point (°C)||−43.8|
|Saturated liquid density (25°C), kg/m3||1138|
|Saturated vapour density (25°C), kg/m3||43.8|
|Critical temperature (°C)||86.4|
|Critical pressure, bar||46.3|
|Liquid heat capacity @ 25°C, (kJ/(kg·K))||1.533|
|Vapour heat capacity @ 1.013 bar (kJ/(kg·K))||1.107|
|This chemistry-related article is a stub. You can help Wikipedia by expanding it.|