Solar air conditioning
This can be done through passive solar, solar thermal energy conversion and photovoltaic conversion (sunlight to electricity). The U.S. Energy Independence and Security Act of 2007 created 2008 through 2012 funding for a new solar air conditioning research and development program, which should develop and demonstrate multiple new technology innovations and mass production economies of scale. Solar air conditioning might play an increasing role in zero-energy and energy-plus buildings design.[who?]
In the late 19th century, the most common fluid for absorption cooling was a solution of ammonia and water. Today, the combination of lithium bromide and water is also in common use. One end of the system of expansion/condensation pipes is heated, and the other end gets cold enough to make ice. Originally, natural gas was used as a heat source in the late 19th century. Today, propane is used in recreational vehicle absorption chiller refrigerators. Hot water solar thermal energy collectors can also be used as the modern "free energy" heat source.
Photovoltaic (PV) solar cooling
Photovoltaics can provide the power for any type of electrically powered cooling be it conventional compressor-based or adsorption/absorption-based, though the most common implementation is with compressors. For small residential and small commercial cooling (less than 5 MWh/a) PV-powered cooling has been the most frequently implemented solar cooling technology. The reason for this is debated, but commonly suggested reasons include incentive structuring, lack of residential-sized equipment for other solar-cooling technologies, the advent of more efficient electrical coolers, or ease of installation compared to other solar-cooling technologies (like radiant cooling).
Since PV cooling's cost effectiveness depends largely on the cooling equipment and given the poor efficiencies in electrical cooling methods until recently it has not been cost effective without subsidies. Using more efficient electrical cooling methods and allowing longer payback schedules is changing that scenario.
For example, a 100,000 BTU U.S. Energy Star rated[note 1] air conditioner with a high seasonal energy efficiency ratio (SEER) of 14 requires around 7 kW of electric power for full cooling output on a hot day. This would require over a 20 kW solar photovoltaic electricity generation system with storage.
A solar-tracking 7 kW photovoltaic system would probably have an installed price well over $20,000 USD (with PV equipment prices currently falling at roughly 17% per year). Infrastructure, wiring, mounting, and NEC code costs may add up to an additional cost; for instance a 3120 watt solar panel grid tie system has a panel cost of $0.99/watt peak, but still costs ~$2.2/watt hour peak. Other systems of different capacity cost even more, let alone battery backup systems, which cost even more.
A more efficient air conditioning system would require a smaller, less-expensive photovoltaic system. A high-quality geothermal heat pump installation can have a SEER in the range of 20 (±). A 100,000 BTU SEER 20 air conditioner would require less than 5 kW while operating.
Newer and lower power technology including reverse inverter DC heat pumps can achieve SEER ratings up to 26.
There are new non-compressor-based electrical air conditioning systems with a SEER above 20 coming on the market. New versions of phase-change indirect evaporative coolers use nothing but a fan and a supply of water to cool buildings without adding extra interior humidity (such as at McCarran Airport Las Vegas Nevada). In dry arid climates with relative humidity below 45% (about 40% of the continental U.S.) indirect evaporative coolers can achieve a SEER above 20, and up to SEER 40. A 100,000 BTU indirect evaporative cooler would only need enough photovoltaic power for the circulation fan (plus a water supply).
A less-expensive partial-power photovoltaic system can reduce (but not eliminate) the monthly amount of electricity purchased from the power grid for air conditioning (and other uses). With American state government subsidies of $2.50 to $5.00 USD per photovoltaic watt, the amortized cost of PV-generated electricity can be below $0.15 per kWh. This is currently cost effective in some areas where power company electricity is now $0.15 or more. Excess PV power generated when air conditioning is not required can be sold to the power grid in many locations, which can reduce (or eliminate) annual net electricity purchase requirement. (See Zero-energy building)
Superior energy efficiency can be designed into new construction (or retrofitted to existing buildings). Since the U.S. Department of Energy was created in 1977, their Weatherization Assistance Program has reduced heating-and-cooling load on 5.5 million low-income affordable homes an average of 31%. A hundred million American buildings still need improved weatherization. Careless conventional construction practices are still producing inefficient new buildings that need weatherization when they are first occupied.
It is fairly simple to reduce the heating-and-cooling requirement for new construction by one half. This can often be done at no additional net cost, since there are cost savings for smaller air conditioning systems and other benefits.
Earth sheltering or Earth cooling tubes can take advantage of the ambient temperature of the Earth to reduce or eliminate conventional air conditioning requirements. In many climates where the majority of humans live, they can greatly reduce the buildup of undesirable summer heat, and also help remove heat from the interior of the building. They increase construction cost, but reduce or eliminate the cost of conventional air conditioning equipment.
Earth cooling tubes are not cost effective in hot humid tropical environments where the ambient Earth temperature approaches human temperature comfort zone. A solar chimney or photovoltaic-powered fan can be used to exhaust undesired heat and draw in cooler, dehumidified air that has passed by ambient Earth temperature surfaces. Control of humidity and condensation are important design issues.
A geothermal heat pump uses ambient Earth temperature to improve SEER for heat and cooling. A deep well recirculates water to extract ambient Earth temperature (typically at 2 gallons of water per ton per minute). These "open loop" systems were the most common in early systems, however water quality could cause damage to the coils in the heat pump and shorten the life of the equipment. Another method is a closed loop system, in which a loop of tubing is run down a well or wells, or in trenches in the lawn, to cool an intermediate fluid. When wells are used, they are back-filled with Bentonite or another grout material to ensure good thermal conductivity to the earth.
In the past the fluid of choice was a 50/50 mixture of propylene glycol because it is non-toxic unlike ethylene glycol (which is used in car radiators). Propylene glycol is viscous, and would eventually gum up some parts in the loop(s), so it has fallen out of favor. Today, the most common transfer agent is a mixture of water and ethyl alcohol (ethanol).
Ambient earth temperature is much lower than peak summer air temperature, and much higher than the lowest extreme winter air temperature. Water is 25 times more thermally conductive than air, so it is much more efficient than an outside air heat pump, (which becomes less effective when the outside temperature drops in Winter).
The same type of geothermal well can be used without a heat pump but with greatly diminished results. Ambient Earth temperature water is pumped through a shrouded radiator (like an automobile radiator). Air is blown across the radiator, which cools without a compressor-based air conditioner. Photovoltaic solar electric panels produce electricity for the water pump and fan, eliminating conventional air-conditioning utility bills. This concept is cost-effective, as long as the location has ambient Earth temperature below the human thermal comfort zone (not the tropics).
Solar Thermal Compression Technology
Introduction - Everyone who understands refrigeration knows that wherever we have gas; the ideal gas law applies. In the refrigeration process, refrigerant is in gaseous state from when it leaves the evaporator through to the condenser.
Therefore the ideal gas law applies - p * V = n * R * T
Pressure (p) of a gas multiplied with its volume (V) corresponds to its temperature (T) and the amount of the gas molecules (n) in that volume. The formula is originally based on the Avogadro constant being the same for all types of gases. However since we use a specific gas, we need to cover the different properties of that gas in a separate constant. In this case R describes the refrigerant and is, a constant. This loop is closed. The volume inside of the piping and vessels i.e. compressor, accumulators, separators etc is always constant, so the volume (V) is constant. In this case, the gas R and V are constant, so therefore the formula basically cuts down to only 3 change variables: p ~ n x T
p * V = n * R * T When the temperature of the gas changes, there are only two things that can happen, either: 1. the pressure (p) increases 2. or the number (n) of gas molecules decreases There are no other options.
The technology saves substantial amounts of energy on both fixed speed multi-stage and variable speed (inverter or digital scroll for example) compression. However, it has little if any impact on single fixed speed compression.
How this technology saves energy: The solar collection system absorbs the infrared and other radiance from the sun. The vacuum tubes become internally hot and therefore heat the refrigerant gas as it passes through. In turn the gas is provided with thermal energy, this process then raises the internal energy (the sum of all microscopic kinetic and potential energy of the molecules) the molecules move with a higher value of kinetic energy which simply implies each molecule moves with a higher velocity than before, as the molecules collide with one another they rebound with higher energies, moreover intermolecular forces weaken and the molecules space out further which then results in an increase in volume. At this point most, if not all of the pressure produced from the additional heat is released in mass volume flow and therefore substantially increased molecular velocity of the refrigerant gas, thus resulting in an increase in the ΔT between condensing and ambient temperatures, effectively increasing the surface area of the condenser.
Those who may be concerned how the condenser addresses any additional heat generated by this process: First and foremost, the systems condenser is designed to manage the compressors running at full load. The reality is when the sun is in the sky (the time when most systems run at full load), this process will ensure that all compressors virtually never run at full load. Of course it would be fantastic to achieve the additional efficiency without additional heat, but the additional heat is the price we pay in return for the higher efficiency. We actually want the heat from the solar collectors, utilising the heat (temperature not pressure) increasing the gas molecules kinetic energy, hence increasing the mass volume flow, and additionally creating an improved Delta T therefore actually enhancing the efficiency of the heat exchanger (condenser). All Refrigeration and A/C systems are manufactured to a very specific design point, e.g. for A/C systems ISO 5151. This point sets the capacities for the compressor, condenser and all other parts. The facts covered in the second paragraph above allows SolarCool [Note: this is promotion of a company] to easily cope with any additional heat.
Solar open-loop Air Conditioning using desiccants
Air can be passed over common, solid desiccants (like silica gel or zeolite) or liquid desiccants (like lithium bromide/chloride) to draw moisture from the air to allow an efficient mechanical or evaporative cooling cycle. The desiccant is then regenerated by using solar thermal energy to dehumidfy, in a cost-effective, low-energy-consumption, continuously repeating cycle. A photovoltaic system can power a low-energy air circulation fan, and a motor to slowly rotate a large disk filled with desiccant.
Energy recovery ventilation systems provide a controlled way of ventilating a home while minimizing energy loss. Air is passed through an "enthalpy wheel" (often using silica gel) to reduce the cost of heating ventilated air in the winter by transferring heat from the warm inside air being exhausted to the fresh (but cold) supply air. In the summer, the inside air cools the warmer incoming supply air to reduce ventilation cooling costs. This low-energy fan-and-motor ventilation system can be cost-effectively powered by photovoltaics, with enhanced natural convection exhaust up a solar chimney - the downward incoming air flow would be forced convection (advection).
A desiccant like calcium chloride can be mixed with water to create an attractive recirculating waterfall, that dehumidifies a room using solar thermal energy to regenerate the liquid, and a PV-powered low-rate water pump
Active solar cooling wherein solar thermal collectors provide input energy for a desiccant cooling system. There are several commercially available systems that blow air through a desiccant impregnated medium for both the dehumidification and the regeneration cycle. The solar heat is one way that the regeneration cycle is powered. In theory packed towers can be used to form a counter-current flow of the air and the liquid desiccant but are not normally employed in commercially available machines. Preheating of the air is shown to greatly enhance desiccant regeneration. The packed column yields good results as a dehumidifier/regenerator, provided pressure drop can be reduced with the use of suitable packing.
Passive solar cooling
In this type of cooling solar thermal energy is not used directly to create a cold environment or drive any direct cooling processes. Instead, solar building design aims at slowing the rate of heat transfer into a building in the summer, and improving the removal of unwanted heat. It involves a good understanding of the mechanisms of heat transfer: heat conduction, convective heat transfer, and thermal radiation, the latter primarily from the sun.
For example, a sign of poor thermal design is an attic that gets hotter in summer than the peak outside air temperature. This can be significantly reduced or eliminated with a cool roof or a green roof, which can reduce the roof surface temperature by 70 °F (40 °C) in summer. A radiant barrier and an air gap below the roof will block about 97% of downward radiation from roof cladding heated by the sun.
Passive solar cooling is much easier to achieve in new construction than by adapting existing buildings. There are many design specifics involved in passive solar cooling. It is a primary element of designing a zero energy building in a hot climate.
Solar closed-loop absorption cooling
The following are common technologies in use for solar thermal closed-loop air conditioning.
- Absorption: NH
2O or Ammonia/Water
- Absorption: Water/Lithium Bromide
- Absorption: Water/Lithium Chloride
- Adsorption: Water/Silica Gel or Water/Zeolite
- Adsorption: Methanol/Activated Carbon
Active solar cooling uses solar thermal collectors to provide solar energy to thermally driven chillers (usually adsorption or absorption chillers). Solar energy heats a fluid that provides heat to the generator of an absorption chiller and is recirculated back to the collectors. The heat provided to the generator drives a cooling cycle that produces chilled water. The chilled water produced is used for large commercial and industrial cooling.
Solar thermal energy can be used to efficiently cool in the summer, and also heat domestic hot water and buildings in the winter. Single, double or triple iterative absorption cooling cycles are used in different solar-thermal-cooling system designs. The more cycles, the more efficient they are. Absorption chillers operate with less noise and vibration than compressor-based chillers, but their capital costs are relatively high.
Efficient absorption chillers nominally require water of at least 190 °F (88 °C). Common, inexpensive flat-plate solar thermal collectors only produce about 160 °F (71 °C) water. High temperature flat plate, concentrating or evacuated tube collectors are needed to produce the higher temperature water required. In large scale installations there are several projects successful both technical and economical in operation world wide including, for example, at the headquarters of Caixa Geral de Depósitos in Lisbon with 1,579 square metres (17,000 sq ft) solar collectors and 545 kW cooling power or on the Olympic Sailing Village in Qingdao/China. In 2011 the most powerful plant at Singapore's new constructed United World College will be commissioned (1500 kW).
These projects have shown that flat plate solar collectors specially developed for temperatures over 200 °F (93 °C) (featuring double glazing, increased backside insulation, etc.) can be effective and cost efficient. Where water can be heated well above 190 °F (88 °C), it can be stored and used when the sun is not shining.
The Audubon Environmental Center at the Ernest E. Debs Regional Park in Los Angeles has an example solar air conditioning installation, which failed fairly soon after commissioning and is no longer being maintained. The Southern California Gas Co. (The Gas Company) is also testing the practicality of solar thermal cooling systems at their Energy Resource Center (ERC) in Downey, California. Solar Collectors from Sopogy and Cogenra were installed on the rooftop at the ERC and are producing cooling for the building’s air conditioning system. Masdar City in the United Arab Emirates is also testing a double-effect absorption cooling plant using Sopogy parabolic trough collectors, Mirroxx Fresnel array and TVP Solar high-vacuum solar thermal panels.
For 150 years, absorption chillers have been used to make ice (before the electric light bulbs were invented). This ice can be stored and used as an "ice battery" for cooling when the sun is not shining, as it was in the 1995 Hotel New Otani Tokyo in Japan. Mathematical models are available in the public domain for ice-based thermal energy storage performance calculations.
The ISAAC Solar Icemaker is an intermittent solar ammonia-water absorption cycle. The ISAAC uses a parabolic trough solar collector and a compact and efficient design to produce ice with no fuel or electric input, and with no moving parts.
Providers of solar cooling systems include ChillSolar, SOLID, Sopogy, Cogenra, Mirroxx  and TVP Solar  for commercial installations and ClimateWell, Fagor-Rotartica, SorTech and Daikin mostly for residential systems. Cogenra uses solar co-generation to produce both thermal and electric energy that can be used for cooling.
Goals of zero-energy buildings include sustainable, green building technologies that can significantly reduce, or eliminate, net annual energy bills. The supreme achievement is the totally off-the-grid autonomous building that does not have to be connected to utility companies. In hot climates with significant degree days of cooling requirement, leading-edge solar air conditioning will be an increasingly important critical success factor.
- "U.S. Energy Independence and Security Act of 2007". Retrieved 2007-12-23.
- Dsire: Dsire Home
- EERE: Department of Energy Weatherization Assistance Program Home Page
- San, J. Y., Lavan, Z., Worek, W. M., Jean-Baptiste Monnier, Franta, G. E., Haggard, K., Glenn, B. H., Kolar, W. A., Howell, J. R. (1982). "Exergy analysis of solar powered desiccant cooling system". Proc. of the American Section of the Intern. Solar Energy Society: 567-572
- EERE Consumer's Guide: Energy Recovery Ventilation Systems
- See Liquid Desiccant Waterfall for attractive building dehumidification
- A packed bed dehumidifier/regenerator for solar air conditioning with liquid desiccants (by Factor, H. M. and Grossman, G., Technion – Israel Institute of Technology)
- Solar Powered Air Conditioning
- George O. G. Löf (1993). Active solar systems. MIT Press. p. 682. ISBN 978-0-262-12167-5.
- Otanicar, T., Taylor, R.A., Phelan, P., Prospects for solar cooling – An economic and environmental assessment,Solar Energy Volume 86, Issue 5, May 2012, Pages 1287–1299
- "Solar Cooling". www.solid.at. Accessed on 1 July 2008
- Les Hamasaki. "10 Ton Solar Air Conditioning at the Debs Park Audubon Environmental Center in Los Angeles (6 minute video)". Retrieved 2007-12-23.
- Gregory Wright, "Solar-Thermal HVAC Technology Debuts in Los Angeles at new Audubon Urban Nature Center ", EnergyPulse, 2.3.04, Accessed 2 July 2014
- "SoCalGas Tests Unusual Solar Air Conditioner". Los Angeles Times. 2012-05-25.
- "HH General Sheikh Mohammed bin Zayed Al Nahyan Crown Prince of Abu Dhabi and Deputy Supreme Commander of UAE Armed Forces visit to Masdar". Zawya. 2011-10-20. Retrieved 2011-10-25.
- "Masdar City Testing TVP Solar High-Vacuum Flat Solar Thermal Panels for Air Conditioning" (PDF). Masdar. 2012-02-16. Retrieved 2012-01-16.
- Gearoid Foley; Robert DeVault; Richard Sweetser. "The Future of Absorption Technology in America" (PDF). U.S. DOE Energy Efficiency and Renewable Energy (EERE). Retrieved 2007-11-08.
- "Ice-cooling System Reduces Environmental Burden". The New Otani News. New Otani Co.,Ltd. 2000-06-28. Retrieved 2007-11-08.
- "Development of a thermal energy storage model for EnergyPlus" (PDF). 2004. Retrieved 2008-04-06.
- "ISAAC Solar Icemaker".
- "Solar installation+design".
- "Sopogy solar heat generation technology".
- "Cogenra- cogeneration".
- "TVP Solar SA".
- Andrew Burger (2012-05-24). "Solar Cogeneration adds Cooling Capability". TriplePundit.
- Solar Thermal Air Conditioning
- AbsorPilot (Spanish)
- EU: solar Heating and Cooling:.
- Cooling with Solar Heat: Growing Interest in Solar Air Conditioning.
- Liquid Desiccant Waterfall for attractive building dehumidification
- Passive solar cooling
- Passive solar cooling in a hot humid climate
- Solar Heating and Cooling Programme, International Energy Agency.
- Solar Thermal Absortion Cooling System.
- Fraunhofer-Institut für Solare Energiesysteme ISE, Solar Cooling
- Distributed Energy Resources Customer Adoption Model (DER-CAM)
- Center for Energy and innovative Technologies
- Solar furnace and air conditioning invention