|This article needs additional citations for verification. (April 2012) (Learn how and when to remove this template message)|
Track lighting is a method of lighting where light fixtures are attached anywhere on a continuous track device which contains electrical conductors. This is as opposed to the routing of electrical wiring to individual light positions. Tracks can be mounted to ceilings or walls, lengthwise down beams, or crosswise across rafters or joists. They can also be hung with rods from especially high places like vaulted ceilings.
Typical systems have line voltage running through a recessed track. The track may have more than one live conductor, so that multiple switched circuits can be used to control different fittings on the same track. This is selected by placing the tab of the connector on the fixture to one side or the other when attaching it to the track. There are three standard types of tracks used in North America, as well as elsewhere in the world. They are often termed "H", "J", and "L" track, after the names of the manufacturers that established the standards, Halo, Juno, and Lightolier. To identify a track fixture, you may use the following two rules: 1. if it has three contacts, it is probably "H" type. 2. If the contact-tips are 1 inch apart, it is probably "J" type, if they are 7/8 inch apart, it is probably "L" type.
Many systems now simply use a single live and then use digital control interfaces such as DALI to control the fittings. This means that each fitting can be independently controlled.
More modern systems are available with low voltage (10, 12, or 24 volts) running through the track, which is in itself decorative. In this case, the fixture may clamp onto a track made of two metal strips separated with an insulating strip. Two-circuit configurations are rare in such systems. The track is powered by a transformer which converts the high voltage into low voltage. There are magnetic and electronic transformers.
Variations on track lighting
Cable lighting is a variation where the fixtures are hung from uninsulated cables which carry low voltage. These fixtures range from the very simple, such as two hinged rods from which a halogen lamp hangs, to the very artful, such as a human silhouette whose feet touch the wires and hands hold the bulb or its socket. Two sets of cables (such as in the corner of a room where two walls meet) can be connected together with short wires that have clips (such as alligator clips or screw clamps) at either end.
Another variation is called flex track or monorail track lighting in which the fixtures are hung from a single line monorail track attached to the ceiling using stems. There are several different types of track. Some are very flexible and can be curved in any shape or form and some are more rigid and can be curved very slightly. Some patterns that can be made are "S curves" or "spirals".
It is also common to see line-voltage tracks with low-voltage fixtures. For these, each fixture requires a small transformer to operate it. For all low-voltage fixtures or systems a special dimmer (if used) is required, as standard dimmers are cheaply made and will cause flickering because of the interaction with the inductive electrical load.
Various adapters are available for combining features of track and other lighting. If the track is properly anchored, a hanging fixture may be suspended from it. The track itself can also be suspended. Rather than being hard-wired to a junction box (which requires a feeder device to be snapped into the track, either in the middle or at one end), it can also be end-fed from a standard wall outlet. Outlets can also be snapped into line-voltage track. There are "L" and "T" adapters for rigid track, as well as flexible ones for unusual angles, or to change the vertical angle where a ceiling changes slope. Adapter plates allow single fixtures to be attached directly to a junction box, by providing an extremely small section of track embedded into the plate. There are also arms which have the same feature, allowing fixtures to be mounted onto the same wall they shine onto, and having an attached power cord and wall plug.
- http://books.google.ca/books?id=bAEAAAAAMBAJ&pg=PA75&dq=%22track+lighting%22&hl=en&redir_esc=y#v=onepage&q=%22track%20lighting%22&f=false Richard Stepler "Track Lighting puts light where you want it", Popular Science, January 1975 Page 75