||This article may require copy editing for grammar, style, cohesion, tone, or spelling. (August 2013)|
A Biosand Filter (BSF) is a point-of-use water treatment system adapted from traditional slow sand filters. Biosand filters remove pathogens and suspended solids from water through a combination of biological and physical processes that take place in a sand column covered with a biofilm. BSFs have been shown to effectively remove heavy metals, turbidity and other contaminants such as bacteria, viruses and protozoa. BSFs also help to reduce discoloration, odor and unpleasant taste. Studies have shown correlation between use of BSFs and decrease in occurrence of diarrhea with an increase in general health. Due to their effectiveness, ease of use, and lack of recurring costs, biosand filters are often considered appropriate technology in developing countries. It is estimated that over 200,000 BSFs are in use worldwide.
- 1 History
- 2 Biosand filter components
- 3 Filtration process
- 4 Maintenance
- 5 Removal of contaminants
- 6 Health benefits
- 7 Types of biosand filters
- 8 See also
- 9 References
- 10 External links
The household biosand filter was proposed by Dr. David Manz in the late 1980s at the University of Calgary, Canada. The system was developed from the slow sand filter, a technology already used for drinking water purification since the 1800s. Initial lab and field tests were conducted in 1991, and the system was patented in 1993  as well as implemented in the field for the first time, in Nicaragua. The Canadian non-profit Center For Affordable Water and Sanitation Technology (CAWST) was co-founded in 2001 by David Manz and Camille Dow Baker to promote worldwide education and training in water purification and sanitation including via this technology as well as to continue developing it. Alternatively, a privately owned company, Hydraid Biosand Water Filter  produces and distributes plans for filters.
Biosand filter components
Biosand filters are typically constructed from either concrete or plastic. The most widely used plans for the concrete biosand filter are produced and distributed by CAWST, and Hydraid Biosand Water Filter. Most biosand filters consist of similar components. At the top of the filter there is a tightly fitted lid, which prevents contamination and unwanted pests from entering the filter. Below is the diffuser plate, which prevents disturbance of the biofilm when water is poured into the filter. Water then travels through the sand column, removing pathogens and suspended solids. Below the sand column is a layer of gravel that prevents sand from entering the drainage layer and clogging the outlet tube. Below the separating layer is the drainage layer, which consists of larger gravel that promotes water flow by preventing clogging near the base of the outlet tube.
Pathogens and suspended solids are removed through a combination of biological and physical processes that take place in the biolayer and within the sand layer. These processes include:
- Mechanical trapping: Suspended solids and pathogens are physically trapped in the spaces between the sand grains.
- Predation: Pathogens are consumed by other microorganisms in the biolayer.
- Adsorption: Pathogens get absorbed to each other and to suspended solids in the water and sand grains.
- Natural death: Pathogens finish their life cycle or die because there is not enough food or oxygen for them to survive.
As referenced earlier, different processes occur during different points in the filter running process. These can be broken down into segments of the filter running process: the pause period (idle time) and actual run of the filter.
During the run
The high water level (hydraulic head) in the inlet reservoir zone pushes the water through the diffuser and filter. The water level in the reservoir decreases as it flows evenly through the sand. The flow rate will slow down over time because there is less pressure to force the water through the filter. The inlet water contains dissolved oxygen, nutrients and contaminants. It provides the oxygen required by the microorganisms in the biofilm. Larger suspended particles and pathogens are trapped in the top of the sand and they partially plug the pore spaces between the sand grains. This also causes the flow rate to slow down.
Pause period (idle time)
Idle time typically accounts for greater than 80% of the daily cycle whereupon various microbial attenuation processes are likely to be significant. In other words, most removal occurs during the point where water is in contact with the biofilm (also referred to as schmutzdecke). Unfortunately the exact processes that occur in the biofilm have not been identified and require further study.
When the standing water layer reaches the same height as the outlet tube, the flow stops. Ideally, this should be at a level that is high enough to keep the biofilm in the sand layer wet, but also allow oxygen from the air to diffuse through the standing water to the biolayer.
The pause period allows time for microorganisms in the biolayer to consume the pathogens and nutrients in the water. The flow rate through the filter is restored as they are consumed. If the pause period is too long, the biolayer will eventually consume all of the pathogens and nutrients and die off. This will reduce the removal efficiency of the filter when it is used again. The pause period should be a minimum of 1 hour after the water has stopped flowing up to a maximum of 48 hours.
Pathogens in the non-biological zone die off due to the lack of nutrients and oxygen.
Over time, particles will accumulate between the sand grains in the filter. Also, as more water is poured, a biofilm will form along the top of the diffuser plate. Both of these occurrences cause a decrease in flow rate. Although slower flow rates generally improve water filtration due to idle time [APS1], it may become too slow for the users’ convenience. If flow rates go below 0.1 litre/minute, it is recommended by CAWST to perform maintenance.
The cleaning method known as the “swirl and dump” or wet harrowing, is used to restore flow rate. To do this, about one gallon of water is added into the filter before cleaning (assuming the filter is empty). The upper layer of sand is then swirled in a circular motion. Dirty water from the swirling is dumped out and the sand is smoothed out at the top. This process is repeated until flow rate is restored.
It is also recommended to clean the diffuser plate, outlet tube, lid, and outside surfaces of the filters regularly.
Long term sustainability and efficacy of biosand filters is dependent on continued education and support from knowledgeable support personnel. Ideally this support should come from the local trained water workers embedded in the community.
Removal of contaminants
Results for turbidity reductions vary depending on the turbidity of the in fluent water. Water with high turbidity looks dirty due to sand, silt and clay floating in the water. Feed turbidity in one study ranged from 1.86 to 3.9 NTU. In a study water was obtained from sample taps of water treatment plants from three local reservoirs. It poured through a slow sand filter and results showed that turbidity decreased to a mean of 1.45 NTU. In another study using surface water a 93% reduction in turbidity was observed. As the biofilm above the sand ripens turbidity removal increases. Although biosand filters do exhibit a high reduction in turbidity, slow sand filters show higher removals due to a slower filtration rate.
There is limited research on removal of heavy metals by biosand filters. In a study conducted in South Africa, the filter was found to have about 64% removal of iron and 5% removal of magnesium.
In laboratory studies, the biosand filter has been found to have about a 98-99% removal of bacteria. In removal for Escherichia coli it was found that the biosand filter may increase due to biofilm formation, over a time period of about two months. The removal after this time period ranged from 97-99.99% depending on the daily charge volume and percent feed water amended with primary effluent to the filter daily. The addition of primary effluent or waste water facilitates growth of the biofilm which aids bacterial die-off. Research in the field shows that implemented biosand filters reduce fewer bacteria than ones in a controlled environment. In research conducted in 55 households of Bonao, Dominican Republic, the average E. coli reduction was found to be about 93 percent.
Lab tests have shown that while the reduction of E. coli from these filters is quite significant, the attenuation in viruses is significantly less due to their small size. In a study using bacteriophages, the removal ranged between 85% and 95% after 45 days of usage. A recent study has suggested that virus removal increases significantly over time, reaching 99.99% after a period of approximately 150 days.
In one lab test the biosand filter got greater than 99.9% removal of protozoa. In tests for one type of protozoa, Giardia lamblia had a 100% removal for 29 days of usage. Another protozoa, Cryptosporidium oocysts, showed to have a slightly lower reduction (99.98%) possibly due to their smaller size. This removal showed to be comparable to that of the slow sand filter.
Studies in the Dominican Republic and Cambodia conducted by the University of North Carolina and the University of Nevada show that BSF use reduced occurrence of diarrheal diseases by 47% in all age groups.
In a study conducted by CAWST in Haiti, 95% of 187 households reported that they believed their water had improved since using biosand filters to clean household water. 80% of users stated that their families’ health had improved since implementation. Such health perceptions on the use of biosand filter has shown to be more positive in long term users.
Types of biosand filters
Concrete filters are the most widespread type of biosand filter, consisting of a durable outer core structure of concrete. Concrete is generally preferable to other materials because of the low cost, wide availability and possibility to be completely constructed on-site. Concrete filter production further allows for entrepreneurship amongst the local community. The plans for the concrete filter are distributed openly by CAWST. Several versions have been developed. The CAWST Version 9 biosand filter is constructed with a higher maximum loading rate and although the filtered water passes EPA water quality standards, it is not optimal. Recent research establishes that contact time between the water and the granular material is the leading determinant in purifying water. The CAWST Version 10 biosand filter takes this into account as the volume of the water reservoir is equal to the pore space volume of the sand layer, with a maximum loading rate decreased by 33% to ensure stagnant water in constant contact with granular material.
- Elliott, M., Stauber, C., Koksal, F., DiGiano, F., and M. Sobsey (2008). Reduction of E. coli, echovirus type 12 and bacteriophages in an intermittently operated 2 household-scale slow sand filter.Water Research, Volume 42, Issues 10-11
- "CAWST Biosand Filter Manual 2008".
- "CAWST Biosand Filter".
- "CAWST History".
- "Hydraid Biosand Technology".
- Sisson, Andrew J.; Wampler, PJ; Rediske RR; Molla AR (January 2013). "An assessment of long-term biosand filter use and sustainability in the Artibonite Valley near Deschapelles, Haiti". Journal of Water, Sanitation and Hygiene for Development 3 (1): 51–60. doi:10.2166/washdev.2013.092.
- Mwabi, J.K., F.E. Adeyemo and T.O. Mamba. "Household Water Treatment Systems: A Solution to the Production of Safe Drinking." SAO/NASA ADS: ADS Home Page. Web. 22 Dec. 2011. http://adsabs.harvard.edu/abs/2011PCE....36.1120M
- Sobsey, Mark; Christine Stauber; Lisa Casanova; Joseph Brown; Mark Elliott (2008). "Point of Use Household Drinking Water Filtration: A Practical, Effective Solution for Providing Sustained Access to Safe Drinking Water in the Developing World". Environmental Science and Technology.
- Bradley, I., Straub, A., Maraccini, P., Markazi, Nguyen, T., (2011). Iron Oxide Amended Biosand Filters for Virus Removal. Water Research
- "Biosand Filter".
- Stauber, Christine; Gloria M. Ortiz; Dana P. Loomis; Mark D. Sobsey (2009). "A Randomized Controlled Trial of the Concrete Biosand Filter and Its Impact on Diarrheal Disease in Bonai, Dominican Republic". The American Society of Tropical Medicine and Hygiene 80 (2): 286–293.
- CAWST Biosand Filter Manual 2010.