All-dielectric self-supporting cable
|This article needs additional citations for verification. (February 2014)|
All-dielectric self-supporting (ADSS) cable is a type of optical fiber cable that is strong enough to support itself between structures without using conductive metal elements. It is used by electrical utility companies as a communications medium, installed along existing overhead transmission lines and often sharing the same support structures as the electrical conductors.
ADSS is an alternative to OPGW and OPAC with lower installation cost. The cables are designed to be strong enough to allow lengths of up to 700 metres to be installed between support towers. ADSS cable is designed to be lightweight and small in diameter to reduce the load on tower structures due to cable weight, wind, and ice.
In the design of the cable, the internal glass optical fibers are supported with no strain, to maintain low optical loss throughout the life of the cable. The cable is jacketed to prevent moisture from degrading the fibers. The jacket also protects the polymer strength elements from the effect of solar ultraviolet light.
Using single-mode fibers and light wavelengths of either 1310 or 1530 nanometres, circuits up to 100 km long are possible without repeaters. A single cable can carry as many as 144 fibers.
No metal wires are used in an ADSS cable. Optical fibers are either supported in loose buffer tubes, or arranged in a ribbon configuration. To prevent strain on the fibers, most types provide the fibres with excess slack length compared to the length of the supporting member.
Several designs of cable are used. In one type, small plastic tubes each containing up to eight fibers are filled with a gel compound, and stranded around plastic rods. The hydrocarbon gel compound prevents water from wicking along the length of the cable. The inner structure is wrapped with polyester tapes and encased in a pultruded glass reinforced plastic tube, which provides the structural strength for the cable. An outer sheath is applied to protect the strength member from ultraviolet light and from damage due to leakage current.
Another type uses a glass reinforced plastic rod with a notch in one side, which carries one or two ribbons of glass fibers. The notch is filled with water-resistant gel and covered with an extruded plastic filler strip. The whole assembly is enclosed in a sunlight and tracking resistant sheath. This design is not as flexible as the symmetrical cylindrical design above, but provides good access to the fibers at joints and is resistant to crushing. At full working load the optical fibers may experience up to 0.25% strain, which is undesirable for long fiber life.
A third type gets its strength from aramid fiber yarns, which are coated to prevent water wicking. The aramid yarn strength member surrounds a core made up of multiple buffer tubes, each with a fiber, all surrounding a plastic core. The outer sheath provides protection from water and sunlight. This design does not have as great resistance to crushing.
Another type of design uses four glass-reinforced plastic strength member strands, and loose buffer tubes cabled into an assembly and protected by a jacket. This is more flexible than the outer cylinder type first described, but does not provide as much protection to the fibers.
ADSS cables made by BICC with 24 or 48 fibers in the above designs range from 220 to 284 kg/kilometre in weight and are between 13 and 16 mm outside jacket diameter. These cables can support between 20 and 25 kilonewtons of tension.
Accessories and installation
Fittings used with ADSS cable may be tension type, used at dead-ends where the cable terminates or changes direction, or may be suspension type, only holding the weight of a span with tension transmitted through the next span of cable. Reinforcing rods are used on either side of a support and at dead-ends. Wind-induced aeolian vibration is a factor since ADSS cables have light weight, relatively high tension, and little self-damping. Anti-vibration dampers are installed on each span near the support points. Accessories must not be clamped directly to the cable but instead over reinforcing rods, to protect the cable from electrical and mechanical damage. Termination boxes are used to enclose and protect splices between the ADSS cable and "inside plant" cable runs.
ADSS cable can be installed using live-line methods on an energized transmission line. Fiber cables are generally supported on the lower cross-arms of the tower, which provides good clearance to the ground. When the fibers are installed in the middle of a tower, the fiber cable is unlikely to hit energized conductors. Lower weights and forces are used for installation, compared with metallic cables, so lighter equipment can be used.
Installation technique is similar to installing overhead conductors, with care taken to prevent excessively tight bending of the cable, and adjustment of the sag of individual spans as for metallic cables.
Cables must be designed for the worst-case combinations of temperature, ice load, and wind. An installed cable must not sag so low that it can be damaged by traffic under the line. Cables must be installed so that "galloping" caused by sustained high wind does not cause the cable to hit conductors, and so that "sleet jump" caused by ice melting off the cable does not cause impacts. The water-blocking gel must not become so stiff at low temperature that the fibers are put under strain.
Transmission lines are exposed to damage by gunfire, especially in rural areas. Shotgun pellets can sever fibers or damage the sheath, allowing water into the cable. Adding a ballistic shield element to the cable makes it larger and heavier and may not be economically feasible. The utility may factor gunshot damage into reliability calculations for the system.
Glass under tension and exposed to acid environments loses strength; this applies to both the optical fibers and the glass reinforcement of polymers. The cable jacket and gel coating of fibres provides protection from chemical attack.
The ADSS cable is suspended in the electrical field due to the phase conductors; this varies from a maximum at mid-span to zero at the grounded metal supports of the cable. In dry conditions, no current flows on the jacket of the cable, but moisture reduces the jacket insulation. Uneven distribution of moisture can result in formation of high-resistance "dry bands" which have a relatively high voltage across them. Dry bands tend to form at the supports. Voltage across the dry band can cause carbon tracks to form and erosion of the jacket material. If the voltage across the dry band is high enough, an arc may form which can damage the jacket. Dry-band arcing is more likely for cables installed under higher transmission voltage lines (220 kV and above). Even a few incidents of arcing along a dry band can cause severe permanent damage to the jacket, leading to subsequent failure of the cable. Relatively low sustained arc currents of a few milliamperes can cause eventual aging degradation of the cable. The magnitude of current available in an arc (and probability of damage) depends on the geometry of the installation and is not simply correlated with the voltage of the transmission line. Wetting conditions near industrial plants or saltwater will have more severe effect on the jacket resistance than in freshwater rain or fog. While one measure to protect cables from dry-banding damage incorporates a semiconducting layer to equalize potential, a more feasible method uses externally applied protection within 50 metres of each support, since this is the area most susceptible to damage.
- Richard C. Dorf (ed), Electronics, Power Electronics, Optoelectronics, Microwaves, Electromagnetics, and Radar CRC Press, 2006 ISBN 0849373395 page 21-27
- G. F. Moore (ed.), Electric Cables Handbook Third Edition, Blackwell Science, 1997 ISBN 0-632-04075-0 Chapter 51 All-dielectric Self-supporting Cables pp. 730-744