||This article includes a list of references, related reading or external links, but its sources remain unclear because it lacks inline citations. (August 2009)|
|Operator||50Hertz Transmission GmbH
|Manufacturer of conductor/cable||NKT Cables|
|Type||submarine cables (52 km (32 mi))
underground cables (119 km (74 mi))
|Type of current||HVDC|
|Total length||171 km (106 mi)|
|Power rating||600 MW|
|AC Voltage||400 kV (both ends)|
|DC Voltage||400 kV|
|Number of poles||1|
The Kontek HVDC is a 170-kilometre (110 mi) long, monopolar 400 kV high-voltage direct current cable between Germany and the Danish island Zealand. Its name comes from "continent" and the name of the former Danish power transmission company "Elkraft", which operated the power grid on the Danish islands Lolland, Falster and Zealand and had the abbreviation "ek". As of today, the cable is operated by Energinet.dk in Denmark and 50Hertz Transmission GmbH in Germany.
Kontek is remarkable because, in contrast to similar facilities like Baltic-Cable and Konti-Skan, all land sections of the 119-kilometre (74 mi) onshore lines on Falster, Sealand and Germany are implemented as underground cable. This unusual measure, which raised the construction costs of Kontek significantly, was made for practical rather than technical reasons. Obtaining permission for building overhead cables can take a long time, and hence underground cables were used in order to ensure it was completed on schedule.
The Kontek cable begins in the static inverter plant of Bentwisch in Germany. It runs 13 kilometres (8.1 mi) to Markgrafenheide on the Baltic Sea, where a 43-kilometre (27 mi) submarine cable section to the island of Falster begins. In this section, the Kontek crosses the Baltic Cable at through the use of a 50-centimetre (20 in) ramp. The Kontek reaches Falster near Gedser, and crosses the island via 50 kilometres (31 mi) of underground cable. Subsequently, a 7-kilometre (4.3 mi) submarine cable section then crosses the sea between Falster and Sealand. A 53-kilometre (33 mi) land cable on Sealand follows, which ends at the static inverter station in Bjæverskov.
The Kontek capacity is 600 megawatts and was commissioned in 1995.
The high-voltage cable of the Kontek is implemented as paper-isolated oil-filled cable with two copper conductors with a cross section of 800 mm2 permanently joined in parallel. For better monitoring of the oil, the land sections of the Kontek cable are divided in sections of approx. 8 kilometres (5.0 mi), which are separated by oil-impermeable sockets from each other. In the proximity of these sockets - at some distance from the cable route - there are automatic stations for the monitoring of the oil pressure, the oil temperature and other operating parameters of the cable. For practical reasons, the 45-kilometre (28 mi) long submarine cable section through the Baltic Sea between Germany and Denmark was implemented as a single oil-filled section without sockets. As electrode cables of the Kontek, on the German and on the Danish side, commercial plastic-isolated 17 kV-cables are used.
The static inverter station in Bjæverskov was attached to an existing substation for 380 kV/110 kV. For the construction of the static inverter plant in Bentwisch a new construction site was chosen even though only one kilometer north there is still the old 220 kV/110 kV-substation which was built in the GDR. In 2002 the static inverter station in Bentwisch was extended to a 380 kV/110 kV-substation and connected by a 110 kV-line to the old 220 kV/110 kV-substation.
|Bentwisch Static Inverter Plant|
|Stuthof Kontek Cable Monitoring Cabinet|
|Markgrafenheide Kontek Cable Monitoring Cabinet|
|Kontek enters Baltic Sea|
|Kontek leaves Baltic Sea|
|Kontek enters Storstrømmen|
|Kontek leaves Storstrømmen|
|Bjæverskov Static Inverter Plant|
- Kontek HVDC Interconnection (ABB)
- Google Maps: Bentwisch Converter
- Google Maps: Bjæverskov Converter
|Wikimedia Commons has media related to Kontek.|