Water metering is the process of measuring water use.
In many developed countries water meters are used to measure the volume of water used by residential and commercial building that are supplied with water by a public water supply system. Water meters can also be used at the water source, well, or throughout a water system to determine flow through a particular portion of the system. In most of the world water meters measure flow in cubic metres (m3) or litres  but in the USA and some other countries water meters are calibrated in cubic feet (ft.3) or US gallons on a mechanical or electronic register. Some electronic meter registers can display rate-of-flow in addition to total usage.
There are several types of water meters in common use. The choice depends on the flow measurement method, the type of end user, the required flow rates, and accuracy requirements.
In North America, standards for manufacturing water meters are set by the American Water Works Association.
- 1 Types of Metering Devices
- 2 Registers
- 3 Prevalence
- 4 Benefits
- 5 Costs
- 6 Problems
- 7 Effect on consumption
- 8 See also
- 9 References
- 10 Further reading
- 11 External links
Types of Metering Devices
There are two common approaches to flow measurement, displacement and velocity, each making use of a variety of technologies. Common displacement designs include oscillating piston and nutating disc meters. Velocity-based designs include single- and multi-jet meters and turbine meters.
There are also non-mechanical designs, for example electromagnetic and ultrasonic meters, and meters designed for special uses. Most meters in a typical water distribution system are designed to measure cold potable water only. Specialty hot water meters are designed with materials that can withstand higher temperatures. Meters for reclaimed water have special lavender register covers to signify that the water should not be used for drinking.
Additionally, there are also electromechanical meters, like the prepaid water meters and automatic meter reading meters. it will integrate the electronic measurement part and LCD display on the mechanical water meter. Normally the mechanical water meter will use read switch, hall or photoelectric coding register as the signal output, after processing by the MCU in electronic module, the data will be transmitted to LCD display or output to the information management system.
Water meters are generally owned, read and maintained by a public water provider such as a city, rural water association or private water company. In some cases an owner of a mobile home park, apartment complex or commercial building may be billed by a utility based on the reading of one meter, with the costs shared among the tenants based on some sort of key (size of flat, number of inhabitants or by separately tracking the water consumption of each unit in what is called submetering).
Displacement water meters
This type of water meter is most often used in residential and small commercial applications. Displacement meters are commonly referred to as Positive Displacement, or "PD" meters. Two common types are oscillating piston meters and Nutating disk meters. Either method relies on the water to physically displace the moving measuring element in direct proportion to the amount of water that passes through the meter. The piston or disk moves a magnet that drives the register.
PD meters are generally very accurate at the low-to-moderate flow rates typical of residential and small commercial users, and commonly range in size from 5/8" to 2". Because displacement meters require that all water flows through the meter to "push" the measuring element, they generally are not practical in large commercial applications requiring high flow rates or low pressure loss. PD meters normally have a built-in strainer to protect the measuring element from rocks or other debris that could stop or break the measuring element. PD meters normally have bronze, brass or plastic bodies with internal measuring chambers made of molded plastics and stainless steel.
Velocity water meters
A velocity-type meter measures the velocity of flow through a meter of a known internal capacity. The speed of the flow can then be converted into volume of flow to determine the usage. There are several types of meters that measure water flow velocity, including jet meters (single-jet and multi-jet), turbine meters, propeller meters and mag meters. Most velocity-based meters have an adjustment vane for calibrating the meter to the required accuracy.
Multi-jet meters are very accurate in small sizes and are commonly used in ⅝" to 2" sizes for residential and smaller commercial uses. Multi-jet meters use multiple ports surrounding an internal chamber to create multiple jets of water against an impeller. The impeller rotation speed depends on the velocity of water flow. Multi-jets are very accurate at low flow rates, but there are no larger sized meters since they do not have the straight-through flow path needed for the high flow rates used in large pipe diameters. Multi-jet meters generally have an internal strainer element that can protect the jet ports from getting clogged. Multi-jet meters normally have bronze alloy bodies or outer casings, with internal measuring parts made from modern thermoplastics and stainless steel.
Turbine meters are less accurate than displacement and jet meters at low flow rates, but the measuring element does not occupy or severely restrict the entire path of flow. The flow direction is generally straight through the meter, allowing for higher flow rates and less pressure loss than displacement-type meters. They are the meter of choice for large commercial users, fire protection and as master meters for the water distribution system. Strainers are generally required to be installed in front of the meter to protect the measuring element from gravel or other debris that could enter the water distribution system. Turbine meters are generally available for 1-½" to 12" or higher pipe sizes. Turbine meter bodies are commonly made of bronze, cast iron or ductile iron. Internal turbine elements can be plastic or non-corrosive metal alloys. They are accurate to 0.2l/s under normal working conditions, however are greatly affeced by dog mix interference.
- Fire meters are a specialized type of turbine meter meeting the high flow rates requirements for fire protection. They are often approved by Underwriters Laboratories (UL) or Factory Mutual (FM) for use in fire protection.
- Fire hydrant meters are a specialized type of portable turbine meter attached to a fire hydrant to measure water flowing out of the hydrant. The meters are normally made of aluminium to be lightweight and are usually 3" capacity. Utilities often require them for measuring water used in construction, pool filling or where a permanent meter has not yet been installed.
A compound meter is used where high flow rates are necessary, but where at times there are also smaller rates of flow that need to be accurately measured. Compound meters have two measuring elements and a check valve to regulate flow between them. At high flow rates, water is normally diverted primarily or completely to the turbine part of the meter. When flow rates drop to where the turbine meter cannot measure accurately, a check valve closes to divert water to a smaller meter that can measure the lower flow rates accurately. The low flow meter is typically a multi-jet or PD meter. By adding the values registered by the high and low meters, the utility has a record of the total consumption of water flowing through the meter.
Magnetic flow meters, commonly referred to as "mag meters", are technically a velocity-type water meter, except that they use electromagnetic properties to determine the water flow velocity, rather than the mechanical means used by jet and turbine meters. Mag meters use the physics principle of Faraday's law of induction for measurement, and require AC or DC electricity from line or battery to operate the electromagnets. Since mag meters have no mechanical measuring element, they normally have the advantage of being able to measure flow in either direction, and use electronics for measuring and totalizing the flow. Mag meters can also be useful for measuring untreated water, raw (untreated/unfiltered) water and waste-water, since there is no mechanical measuring element to get clogged or damaged by debris flowing through the meter. Strainers are not required with mag meters, since there is no measuring element in the stream of flow that could be damaged. Since stray electrical energy flowing through the flow tube can cause inaccurate readings, most mag meters are installed with either grounding rings or grounding electrodes to divert stray electricity away from the electrodes inside the flow tube which are used to measure the flow.
Prepaid water meters
According to the payment method, the meters can be divides into prepaid and postpaid. Most of mechanical type water meters is postpaid, and also the [electromagnetic meters] and [Ultrasonic Meters]. Prepaid water meters means the user must buy the water credit or amount from the vending station, and then transfer the credit through the media, the media can be the IC type card or RF Type Card. The main difference is whether the card need to contact with the processing part of the prepaid water meter. Also in some area the prepaid water meter is using keypad as the interface to input the water credit.
There are several types of registers on water meters. A standard register normally has a dial similar to a clock, with gradations around the perimeter to indicate water usage measured by the meter, as well as a set of odometer wheels similar to that in a car. Modern registers are normally driven by a magnetic coupling between a magnet in the measuring chamber attached to the measuring element and another attached to the bottom of the register. Gears in the register convert the motion of the measuring element to the proper usage increment for display on the sweep hand and the odometer. Many registers also have a leak detector. This is a small visible disk or hand that is geared closer to the rotation speed of the drive magnet, so that very small flows that would be visually undetectable on the regular sweep hand can be seen.
With Automatic Meter Reading, manufacturers have developed pulse or encoder registers to produce electronic output for radio transmitters, reading storage devices, and data logging devices. Pulse meters send a digital or analog electronic pulse to a recording device. Encoder registers have an electronic means for an external device to interrogate the register for either the position of the odometer wheels or a stored electronic reading. Frequent transmissions of consumption can be used to give smart meter functionality.
There are also some specialized types of registers such as meters with an LCD display instead of mechanical odometers, and registers to output data or pulses to a variety of recording and controller devices. For industrial applications, output is often 4-20 mA analog, for the recording or control of different flow rates in addition to totalization.
Water meter reading
Different size meters may indicate a reading in different resolutions. One rotation of the sweep hand may be 10 gallons or 1,000 gallons (1 to 100 ft.3, 0.1 to 10 m3). If one rotation of the hand represents 10 gallons, the meter has a 10 gallon sweep. Sometimes the last number(s) of the odometer are non-rotating or printed on the dial face. The fixed zero number(s) are represented by the position of the rotating sweep hand. If one rotation of the hand is 10 gallons, the sweep hand is on 7, and the odometer shows 123456 plus a fixed zero, the actual total usage would be 1,234,567 gallons.
In the United States most utilities bill only to the nearest 100 or 1,000 gallons (10 to 100 ft.3, 1 to 10 m3), and often only read the leftmost 4 or 5 numbers on the odometer. They would only read and bill using 1,234 and rounding to 1,234,000 gallons based on a 1,000 gallon billing resolution and the example above. The most common rounding for a particular size meter will often have different coloured number wheels, the ones ignored being black, and the ones used for billing being white.
Water metering is common for residential and commercial drinking water supply in many countries, as well as for industrial self-supply with water. However, it is less common in irrigated agriculture, which is the major water user worldwide. Water metering is also uncommon for piped drinking water supply in rural areas and small towns, although there are examples of successful metering in rural areas in developing countries, such as in El Salvador.
Metering of water supplied by utilities to residential, commercial and industrial users is common in most developed countries, except for the United Kingdom where only about 38% of users are metered. In some developing countries metering is very high, such as in Chile where it stands at 96%, while in others it still remains low, such as in Argentina.
The share of residential water metering in selected cities in developing countries is as follows:
- 99% in Santiago de Chile (1998)
- 96% in Abidjan, Ivory Coast (1987)
- 62% in cities in Guatemala (2000)
- 30% in Lima, Peru (1991)
- 28% in Kathmandu, Nepal (2001)
- 2% in Buenos Aires, Argentina (1992)
The benefits of metering are that:
- in conjunction with volumetric pricing it provides an incentive for water conservation,
- it helps to detect water leaks in the distribution network, thus providing a basis for the reduction of Non-revenue water;
- it is a precondition for quantity-targeting of water subsidies to the poor.
The costs of metering include:
- the investment costs to purchase and to install meters, as well as
- the recurrent costs to read meters and to issue bills based on consumption instead of bills based on monthly flat fees.
While the cost of purchasing residential meters is low (in the range of US$20 per meter), the total life cycle costs of metering are higher. For example, retrofitting flats in large buildings with meters for every flat can involve major plumbing work and can be very costly.
Problems associated with metering arise particularly in the case of intermittent supply, which is common in many developing countries. Sudden changes in pressure can damage meters, so that many meters in cities in developing countries are not functional. Also, some types of meters become less accurate as they age and under-register consumption thus leading to lower revenues, unless they are being replaced regularly. Many types of meters also register air flows, which can lead to over-registration of consumption, especially in systems with intermittent supply, when water supply is re-established and the incoming water pushes air through the meters.
Effect on consumption
There is disagreement as to the effect of metering and water pricing on water consumption. The price elasticity of metered water demand varies greatly depending on local conditions. The effect of volumetric water pricing on consumption tends to be higher if the water bill represents a significant share in household expenditures. There is evidence from the UK that there is an instant drop in consumption of some 10% when meters are being installed. In Hamburg, Germany, domestic water consumption for metered flats (112 liter/capita/day) was 18% lower than for unmetered flats (137 liter/capita/day) in 1992. The municipal utility Hamburger Wasserwerke GmbH had installed more than 40,000 water meters in individual flats of older houses since 1985. All new apartments had to be metered by law. Previously there had been only a single meter for the entire house in multi-apartment houses.
- Advanced Metering Infrastructure
- American Water Works Association
- Automated meter reading
- Drinking water
- Electricity Meter
- Flow measurement
- Gas meter
- Meter Data Management
- Public utility
- Utility submeter
- Water conservation
- Ofwat UK - Water meters - your questions answered
- Water and Sanitation Program Field Note: Micro-metering in rural areas: A success story from El Salvador, 2003 (in Spanish) PAS
- http://www.ofwat.gov.uk/future/customers/metering/pap_tec201110metering.pdf - Ofwat, Exploring the costs and benefits of faster, more systematic water metering in England and Wales, October 2011
- World Bank: Water, Electricity and the Poor, p. 78 WB
- OECD:The Price of Water: Trends in OECD countries, 1999, accessed on 21 January 2010
- Lis Stedman: Motivations for metering, Water 21, The Magazine of the International Water Association, April 2006, p. 26-28
- Trinkwasserversorgung in Deutschland, DIW-Wochenbericht 39/1993
- American Water Works Association Manual of Water Supply Practices Manual M6, Water Meters — Selection, Installation, Testing, and Maintenance, ISBN 1-58321-017-2
- American Water Works Association standards C700-02: Cold-Water Meters—Displacement Type, Bronze Main Case
- American Water Works Association standards C701-02: Cold-Water Meters—Turbine Type
- American Water Works Association standards C702-01: Cold-Water Meters—Compound Type
- American Water Works Association standards C703-96: Cold-Water Meters—Fire Service Type
- American Water Works Association standards C707-05: Encoder-Type Remote-Registration Systems for Cold-Water Meters
- American Water Works Association standards C708-05: Cold-Water Meters Multijet Type
|Wikimedia Commons has media related to Water meter.|
- Water Measurement Manual of the United States Bureau of Reclamation
- Utilimetrics - Non-profit industry trade association (Formerly known as the Automatic Meter Reading Association AMRA)
- How to read different size water meters (PDF file)
- How Meter Keeps Tab On The Water You Use, Popular Science, July 1950 very detailed article with good illustrations
- Typical Prepaid water meter introduction(PDF file)