This article is within the scope of WikiProject Energy, a collaborative effort to improve the coverage of Energy on Wikipedia. If you would like to participate, please visit the project page, where you can join the discussion and see a list of open tasks.
This article has been rated as High-importance on the project's importance scale.
This article has been marked as needing immediate attention.
our ckt breaker always trips off and the breaker load sign is 30mA, I computed the used equipment and it turns out that it is higher than 15 amperes. By how many amperes should I use on the ckt breaker to stop tripping.<br