Gaseous fire suppression
|This article needs additional citations for verification. (July 2007)|
Gaseous fire suppression is a term to describe the use of inert gases and chemical agents to extinguish a fire. Also called Clean Agent Fire Suppression. These Agents are governed by the NFPA Standard for Clean Agent Fire Extinguishing Systems – NFPA 2001 in the USA, with different standards and regulations in other parts of the world. The system typically consists of the agent, agent storage containers, agent release valves, fire detectors, fire detection system (wiring control panel, actuation signaling), agent delivery piping, and agent dispersion nozzles. Less typically, the agent may be delivered by means of solid propellant gas generators that produce either inert or chemically active gas.
There are four means used by the agents to extinguish a fire. They act on the "fire tetrahedron":
- Reduction or isolation of fuel. No agents currently use this as the primary means of fire suppression.
- Reduction of heat. Representative agents: Clean agent FS 49 C2 (NAF S 227, MH227, FM-200), Novec 1230, pentafluoroethane (NAF S125, ECARO-25).
- Reduction or isolation of oxygen: Representative agents: Argonite / IG-55 (ProInert), CO2 carbon dioxide, IG-541 Inergen, and IG-100 (NN100).
- Inhibiting the chain reaction of the above components. Representative agents: FE-13, 1,1,1,2,3,3,3-Heptafluoropropane, FE-25, haloalkanes, bromotrifluoromethane, trifluoroiodomethane, NAF P-IV, NAF S-III, NAF S 125, NAF S 227, and Triodide (Trifluoroiodomethane).
Broadly speaking, there are two methods for applying an extinguishing agent: total flooding and local application.
Systems working on a total flooding principle apply an extinguishing agent to a three dimensional enclosed space in order to achieve a concentration of the agent (volume percent of the agent in air) adequate to extinguish the fire. These types of systems may be operated automatically by detection and related controls or manually by the operation of a system actuator.
Systems working on a local application principle apply an extinguishing agent directly onto a fire (usually a two dimensional area), or into the three dimensional region immediately surrounding the substance or object on fire. The main difference in local application from total flooding design is the absence of physical barriers enclosing the fire space.
In the context of automatic extinguishing systems, local application generally refers to the use of systems that have been emplaced some time prior to their usage rather than the use of manually operated wheeled or portable fire extinguishers, although the nature of the agent delivery is similar and many automatic systems may also be activated manually. The lines are blurred somewhat with portable automatic extinguishing systems, although these are not common.
An extinguishing system which primarily is based on inert gases in enclosed spaces presents a risk of suffocation. Numerous incidents have occurred where individuals in these spaces have been killed by carbon dioxide agent release. To prevent such occurrences, additional life safety systems are typically installed with a warning alarm that precedes the agent release. The warning, usually an audible and visible alert, advises the immediate evacuation of the enclosed space. After a preset time, the agent starts to discharge. Accidents have also occurred during maintenance of these systems, so proper safety precautions must be taken beforehand.
The positive pressure caused by these gases may be sufficient to break windows and walls. Humans and structures must be adequately protected and ventilation/blow-off must be considered when designing the system.
- Automatic fire suppression
- Condensed aerosol fire suppression
- Fire protection
- Hypoxic air technology for fire prevention
- "Gas extinguishing system may blow out walls and windows". blog.anta.net. 2009-04-14. ISSN 1797-1993. Retrieved 2009-04-14.
- Fire Suppression Systems Association
- National Fire Protection Association
- EPA Study on CO2 System Safety