A transformer is an electrical device that transfers energy between two circuits through electromagnetic induction. A transformer may be used as a safe and efficient voltage converter to change the AC voltage at its input to a higher or lower voltage at its output. Other uses include current conversion, isolation with or without changing voltage and impedance conversion.
A transformer most commonly consists of two windings of wire that are wound around a common core to provide tight electromagnetic coupling between the windings. The core material is often a laminated iron core. The coil that receives the electrical input energy is referred to as the primary winding, the output coil is the secondary winding.
An alternating electric current flowing through the primary winding (coil) of a transformer generates a varying electromagnetic field in its surroundings which induces a varying magnetic flux in the core of the transformer. The varying electromagnetic field in the vicinity of the secondary winding induces an electromotive force in the secondary winding, which appears as a voltage across the output terminals. If a load is connected across the secondary winding, a current flows through the secondary winding drawing power from the primary winding and its power source.
A transformer cannot operate with direct current. When connected to a DC source, a transformer typically produces a short output pulse as the input current rises.
- 1 Invention
- 2 Applications
- 3 Basic principles
- 4 Basic transformer parameters and construction
- 5 Construction
- 6 Classification parameters
- 7 Types
- 8 Applications
- 9 History
- 10 See also
- 11 Notes
- 12 References
- 13 Bibliography
- 14 External links
The invention of transformers during the late 1800s enabled long distance, cheaper, and energy efficient transmission, distribution, and utilization of electrical energy. In the early days of commercial electric power, the main energy source was direct current (DC), which operates at relatively low-voltage and high-current. According to Joule's Law, energy losses are directly proportional to the square of the current. This law revealed that even a tiny decrease in current or rise in voltage can cause a substantial lowering in energy losses and costs. Thus, the historical pursuit for a high voltage low current electricity transmission system took shape. Although high voltage transmission systems offered many benefits, the future fate of high-voltage alternating current remained unclear for several reasons: high-voltage sources had a much higher risk of causing severe electrical injuries. Many essential appliances could only function at low voltage. Regarded as one of the most influential electrical innovations of all time, the introduction of transformers had successfully reduced the safety concerns associated with alternating current and had the ability to lower voltage to the value required by most essential appliances.
Transformers perform voltage conversion, isolation protection, and impedance matching. In terms of voltage conversion, transformers can step up voltage and step down current from generators to high voltage transmission lines, and step down voltage/step up current to local distribution circuits or industrial customers. The step-up transformer is used to increase the secondary voltage relative to the primary voltage. The step-down transformer is used to decrease the secondary voltage relative to the primary voltage. Transformers range in size from thumbnail-sized units used in microphones to those weighing hundreds of tons interconnecting the power grid. A broad range of transformer designs are used in electronic and electric power applications, including miniature, audio, isolation, high-frequency, power conversion, etc.
The operation of a transformer is based on two principles of the laws of electromagnetic induction: An electric current through a conductor, produces a magnetic field surrounding the conductor, and a changing magnetic field in the vicinity of a conductor induces a voltage across the ends of that conductor.
The magnetic field excited in the primary coil gives rise to self-induction as well as mutual induction between coils. This self-induction counters the excited field to such a degree that the resulting current through the primary winding is very small when the secondary winding is not connected to a load.
The physical principles of the inductive behavior of the transformer are most readily understood and formalized when making some assumptions to construct a simple model which is called the ideal transformer. This model differs from real transformers by assuming that the transformer is perfectly constructed and by neglecting that electrical or magnetic losses occur in the materials used to construct the device.
The assumptions to characterize the ideal transformer are:
- The windings of the transformer have no resistance. Thus, there is no copper loss in the winding, and hence no voltage drop.
- Flux is confined within the magnetic core. Therefore, it is the same flux that links the input and output windings.
- Permeability of the core is infinitely high which implies that net mmf (amp-turns) must be zero (otherwise there would be infinite flux) hence IP NP - IS NS = 0.
- The transformer core does not suffer magnetic hysteresis or eddy currents, which cause inductive loss.
If the secondary winding of an ideal transformer has no load, no current flows in the primary winding.
The circuit diagram (right) shows the conventions used for an ideal, i.e. lossless and perfectly coupled transformer having primary and secondary windings with NP and NS turns, respectively.
The ideal transformer induces secondary voltage VS as a proportion of the primary voltage VP and respective winding turns as given by the equation
- a is the winding turns ratio, the value of these ratios being respectively higher and lower than unity for step-down and step-up transformers,[a][b]
- VP designates source impressed voltage,
- VS designates output voltage, and,
According to this formalism, when the number of turns in the primary coil is greater than the number of turns in the secondary coil, the secondary voltage is smaller than the primary voltage. On the other hand, when the number of turns in the primary coil is less than the number of turns in the secondary, the secondary voltage is greater than the primary voltage.
Any load impedance ZL connected to the ideal transformer's secondary winding allows energy to flow without loss from primary to secondary circuits. The resulting input and output apparent power are equal as given by the equation
Combining the two equations yields the following ideal transformer identity
This formula is a reasonable approximation for the typical commercial transformer, with voltage ratio and winding turns ratio both being inversely proportional to the corresponding current ratio.
The load impedance ZL and secondary voltage VS determine the secondary current IS as follows
A varying electrical current passing through the primary coil creates a varying magnetic field around the coil which induces a voltage in the secondary winding. The primary and secondary windings are wrapped around a core of very high magnetic permeability, usually iron,[c] so that most of the magnetic flux passes through both the primary and secondary coils. The current through a load connected to the secondary winding and the voltage across it flow in the directions indicated in the figure.
The voltage induced across the secondary coil may be calculated from Faraday's law of induction, which states that:
where Vs is the instantaneous voltage, Ns is the number of turns in the secondary coil, and dΦ/dt is the derivative[d] of the magnetic flux Φ through one turn of the coil. If the turns of the coil are oriented perpendicularly to the magnetic field lines, the flux is the product of the magnetic flux density B and the area A through which it cuts. The area is constant, being equal to the cross-sectional area of the transformer core, whereas the magnetic field varies with time according to the excitation of the primary. Since the same magnetic flux passes through both the primary and secondary coils in an ideal transformer, the instantaneous voltage across the primary winding equals
Taking the ratio of the above two equations gives the same voltage ratio and turns ratio relationship shown above, that is,
The changing magnetic field induces an emf across each winding. The primary emf, acting as it does in opposition to the primary voltage, is sometimes termed the counter emf. This is in accordance with Lenz's law, which states that induction of emf always opposes development of any such change in magnetic field.
As still lossless and perfectly-coupled, the transformer still behaves as described above in the ideal transformer.
The relationships of the instantaneous polarity at each of the terminals of the windings of a transformer depend on the direction the windings are wound around the core. Identically wound windings produce the same polarity of voltage at the corresponding terminals. This relationship is usually denoted by the dot convention in transformer circuit diagrams, nameplates, and on terminal markings, which marks the terminals having an in-phase relationship.[e][f]
The ideal transformer model neglects the following basic linear aspects in real transformers.
Core losses, collectively called magnetizing current losses, consist of
- Hysteresis losses due to nonlinear application of the voltage applied in the transformer core, and
- Eddy current losses due to joule heating in the core that are proportional to the square of the transformer's applied voltage.
Whereas windings in the ideal model have no impedance, the windings in a real transformer have finite non-zero impedances in the form of:
- Joule losses due to resistance in the primary and secondary windings
- Leakage flux that escapes from the core and passes through one winding only resulting in primary and secondary reactive impedance.
If a voltage is applied across the primary terminals of a real transformer while the secondary winding is open without load, the real transformer must be viewed as a simple inductor with an impedance Z:
The ideal transformer model assumes that all flux generated by the primary winding links all the turns of every winding, including itself. In practice, some flux traverses paths that take it outside the windings. Such flux is termed leakage flux, and results in leakage inductance in series with the mutually coupled transformer windings. Leakage flux results in energy being alternately stored in and discharged from the magnetic fields with each cycle of the power supply. It is not directly a power loss, but results in inferior voltage regulation, causing the secondary voltage not to be directly proportional to the primary voltage, particularly under heavy load. Transformers are therefore normally designed to have very low leakage inductance. Nevertheless, it is impossible to eliminate all leakage flux because it plays an essential part in the operation of the transformer. The combined effect of the leakage flux and the electric field around the windings is what transfers energy from the primary to the secondary.
In some applications increased leakage is desired, and long magnetic paths, air gaps, or magnetic bypass shunts may deliberately be introduced in a transformer design to limit the short-circuit current it will supply. Leaky transformers may be used to supply loads that exhibit negative resistance, such as electric arcs, mercury vapor lamps, and neon signs or for safely handling loads that become periodically short-circuited such as electric arc welders.
Air gaps are also used to keep a transformer from saturating, especially audio-frequency transformers in circuits that have a DC component flowing in the windings.
Knowledge of leakage inductance is also useful when transformers are operated in parallel. It can be shown that if the percent impedance (Z) and associated winding leakage reactance-to-resistance (X/R) ratio of two transformers were hypothetically exactly the same, the transformers would share power in proportion to their respective volt-ampere ratings (e.g. 500 kVA unit in parallel with 1,000 kVA unit, the larger unit would carry twice the current). However, the impedance tolerances of commercial transformers are significant. Also, the Z impedance and X/R ratio of different capacity transformers tends to vary, corresponding 1,000 kVA and 500 kVA units' values being, to illustrate, respectively, Z ~ 5.75%, X/R ~ 3.75 and Z ~ 5%, X/R ~ 4.75.
Winding joule losses and leakage reactances are represented by the following series loop impedances of the model:
- Primary winding: RP, XP
- Secondary winding: RS, XS.
In normal course of circuit equivalence transformation, RS and XS are in practice usually referred to the primary side by multiplying these impedances by the turns ratio squared, (NP/NS) 2 = a2.
Core loss and reactance is represented by the following shunt leg impedances of the model:
- Core or iron losses: RC
- Magnetizing reactance: XM.
RC and XM are collectively termed the magnetizing branch of the model.
Core losses are caused mostly by hysteresis and eddy current effects in the core and are proportional to the square of the core flux for operation at a given frequency. The finite permeability core requires a magnetizing current IM to maintain mutual flux in the core. Magnetizing current is in phase with the flux, the relationship between the two being non-linear due to saturation effects. However, all impedances of the equivalent circuit shown are by definition linear and such non-linearity effects are not typically reflected in transformer equivalent circuits. With sinusoidal supply, core flux lags the induced emf by 90°. With open-circuited secondary winding, magnetizing branch current I0 equals transformer no-load current.
The resulting model, though sometimes termed 'exact' equivalent circuit based on linearity assumptions, retains a number of approximations. Analysis may be simplified by assuming that magnetizing branch impedance is relatively high and relocating the branch to the left of the primary impedances. This introduces error but allows combination of primary and referred secondary resistances and reactances by simple summation as two series impedances.
Transformer equivalent circuit impedance and transformer ratio parameters can be derived from the following tests: open-circuit test,[g] short-circuit test, winding resistance test, and transformer ratio test.
Basic transformer parameters and construction
Effect of frequency
The time-derivative term in Faraday's Law shows that the flux in the core is the integral with respect to time of the applied voltage. Hypothetically an ideal transformer would work with direct-current excitation, with the core flux increasing linearly with time. In practice, the flux rises to the point where magnetic saturation of the core occurs, causing a large increase in the magnetizing current and overheating the transformer. All practical transformers must therefore operate with alternating (or pulsed direct) current.
The emf of a transformer at a given flux density increases with frequency. By operating at higher frequencies, transformers can be physically more compact because a given core is able to transfer more power without reaching saturation and fewer turns are needed to achieve the same impedance. However, properties such as core loss and conductor skin effect also increase with frequency. Aircraft and military equipment employ 400 Hz power supplies which reduce core and winding weight. Conversely, frequencies used for some railway electrification systems were much lower (e.g. 16.7 Hz and 25 Hz) than normal utility frequencies (50 – 60 Hz) for historical reasons concerned mainly with the limitations of early electric traction motors. As such, the transformers used to step-down the high over-head line voltages (e.g. 15 kV) were much heavier for the same power rating than those designed only for the higher frequencies.
Operation of a transformer at its designed voltage but at a higher frequency than intended will lead to reduced magnetizing current. At a lower frequency, the magnetizing current will increase. Operation of a transformer at other than its design frequency may require assessment of voltages, losses, and cooling to establish if safe operation is practical. For example, transformers may need to be equipped with 'volts per hertz' over-excitation relays to protect the transformer from overvoltage at higher than rated frequency.
One example of state-of-the-art design is traction transformers used for electric multiple unit and high-speed train service operating across the country border and using different electrical standards, such transformers' being restricted to be positioned below the passenger compartment. The power supply to, and converter equipment being supply by, such traction transformers have to accommodate different input frequencies and voltage (ranging from as high as 50 Hz down to 16.7 Hz and rated up to 25 kV) while being suitable for multiple AC asynchronous motor and DC converters & motors with varying harmonics mitigation filtering requirements.
Large power transformers are vulnerable to insulation failure due to transient voltages with high-frequency components, such as caused in switching or by lightning.
A theoretical (ideal) transformer does not experience energy losses, i.e. it is 100% efficient. The power dissipated by its load would be equal to the power supplied by its primary source. In contrast, a real transformer is typically 95 to 99% efficient, due to several loss mechanisms, including winding resistance, winding capacitance, leakage flux, core losses, and hysteresis loss. Larger transformers are generally more efficient than small units, and those rated for electricity distribution usually perform better than 98%.
Experimental transformers using superconducting windings achieve efficiencies of 99.85%. The increase in efficiency can save considerable energy in a large heavily loaded transformer; the trade-off is in the additional initial and running cost of the superconducting design.
As transformer losses vary with load, it is often useful to express these losses in terms of no-load loss, full-load loss, half-load loss, and so on. Hysteresis and Eddy current losses are constant at all load levels and dominate overwhelmingly without load, while variable winding joule losses dominating increasingly as load increases. The no-load loss can be significant, so that even an idle transformer constitutes a drain on the electrical supply. Designing energy efficient transformers for lower loss requires a larger core, good-quality silicon steel, or even amorphous steel for the core and thicker wire, increasing initial cost. The choice of construction represents a trade-off between initial cost and operating cost.
Transformer losses arise from:
- Winding joule losses
- Current flowing through winding conductors causes joule heating. As frequency increases, skin effect and proximity effect causes winding resistance and, hence, losses to increase.
- Core losses
- Hysteresis losses
- Each time the magnetic field is reversed, a small amount of energy is lost due to hysteresis within the core. According to Steinmetz's formula, the heat energy due to hysteresis is given by
- , and,
- hysteresis loss is thus given by
- where, f is the frequency, η is the hysteresis coefficient and βmax is the maximum flux density, the empirical exponent of which varies from about 1.4 to 1 .8 but is often given as 1.6 for iron.
- Eddy current losses
- Ferromagnetic materials are also good conductors and a core made from such a material also constitutes a single short-circuited turn throughout its entire length. Eddy currents therefore circulate within the core in a plane normal to the flux, and are responsible for resistive heating of the core material. The eddy current loss is a complex function of the square of supply frequency and inverse square of the material thickness. Eddy current losses can be reduced by making the core of a stack of plates electrically insulated from each other, rather than a solid block; all transformers operating at low frequencies use laminated or similar cores.
- Magnetostriction related transformer hum
- Magnetic flux in a ferromagnetic material, such as the core, causes it to physically expand and contract slightly with each cycle of the magnetic field, an effect known as magnetostriction, the frictional energy of which produces an audible noise known as mains hum or transformer hum. This transformer hum is especially objectionable in transformers supplied at power frequencies[h] and in high-frequency flyback transformers associated with PAL system CRTs.
- Stray losses
- Leakage inductance is by itself largely lossless, since energy supplied to its magnetic fields is returned to the supply with the next half-cycle. However, any leakage flux that intercepts nearby conductive materials such as the transformer's support structure will give rise to eddy currents and be converted to heat. There are also radiative losses due to the oscillating magnetic field but these are usually small.
- Mechanical vibration and audible noise transmission
- In addition to magnetostriction, the alternating magnetic field causes fluctuating forces between the primary and secondary windings. This energy incites vibration transmission in interconnected metalwork, thus amplifying audible transformer hum.
Core form and shell form transformers
Closed-core transformers are constructed in 'core form' or 'shell form'. When windings surround the core, the transformer is core form; when windings are surrounded by the core, the transformer is shell form. Shell form design may be more prevalent than core form design for distribution transformer applications due to the relative ease in stacking the core around winding coils. Core form design tends to, as a general rule, be more economical, and therefore more prevalent, than shell form design for high voltage power transformer applications at the lower end of their voltage and power rating ranges (less than or equal to, nominally, 230 kV or 75 MVA). At higher voltage and power ratings, shell form transformers tend to be more prevalent. Shell form design tends to be preferred for extra high voltage and higher MVA applications because, though more labor-intensive to manufacture, shell form transformers are characterized as having inherently better kVA-to-weight ratio, better short-circuit strength characteristics and higher immunity to transit damage.
Laminated steel cores
Transformers for use at power or audio frequencies typically have cores made of high permeability silicon steel. The steel has a permeability many times that of free space and the core thus serves to greatly reduce the magnetizing current and confine the flux to a path which closely couples the windings. Early transformer developers soon realized that cores constructed from solid iron resulted in prohibitive eddy current losses, and their designs mitigated this effect with cores consisting of bundles of insulated iron wires. Later designs constructed the core by stacking layers of thin steel laminations, a principle that has remained in use. Each lamination is insulated from its neighbors by a thin non-conducting layer of insulation. The universal transformer equation indicates a minimum cross-sectional area for the core to avoid saturation.
The effect of laminations is to confine eddy currents to highly elliptical paths that enclose little flux, and so reduce their magnitude. Thinner laminations reduce losses, but are more laborious and expensive to construct. Thin laminations are generally used on high-frequency transformers, with some of very thin steel laminations able to operate up to 10 kHz.
One common design of laminated core is made from interleaved stacks of E-shaped steel sheets capped with I-shaped pieces, leading to its name of 'E-I transformer'. Such a design tends to exhibit more losses, but is very economical to manufacture. The cut-core or C-core type is made by winding a steel strip around a rectangular form and then bonding the layers together. It is then cut in two, forming two C shapes, and the core assembled by binding the two C halves together with a steel strap. They have the advantage that the flux is always oriented parallel to the metal grains, reducing reluctance.
A steel core's remanence means that it retains a static magnetic field when power is removed. When power is then reapplied, the residual field will cause a high inrush current until the effect of the remaining magnetism is reduced, usually after a few cycles of the applied AC waveform. Overcurrent protection devices such as fuses must be selected to allow this harmless inrush to pass. On transformers connected to long, overhead power transmission lines, induced currents due to geomagnetic disturbances during solar storms can cause saturation of the core and operation of transformer protection devices.
Distribution transformers can achieve low no-load losses by using cores made with low-loss high-permeability silicon steel or amorphous (non-crystalline) metal alloy. The higher initial cost of the core material is offset over the life of the transformer by its lower losses at light load.
Powdered iron cores are used in circuits such as switch-mode power supplies that operate above mains frequencies and up to a few tens of kilohertz. These materials combine high magnetic permeability with high bulk electrical resistivity. For frequencies extending beyond the VHF band, cores made from non-conductive magnetic ceramic materials called ferrites are common. Some radio-frequency transformers also have movable cores (sometimes called 'slugs') which allow adjustment of the coupling coefficient (and bandwidth) of tuned radio-frequency circuits.
Toroidal transformers are built around a ring-shaped core, which, depending on operating frequency, is made from a long strip of silicon steel or permalloy wound into a coil, powdered iron, or ferrite. A strip construction ensures that the grain boundaries are optimally aligned, improving the transformer's efficiency by reducing the core's reluctance. The closed ring shape eliminates air gaps inherent in the construction of an E-I core. The cross-section of the ring is usually square or rectangular, but more expensive cores with circular cross-sections are also available. The primary and secondary coils are often wound concentrically to cover the entire surface of the core. This minimizes the length of wire needed, and also provides screening to minimize the core's magnetic field from generating electromagnetic interference.
Toroidal transformers are more efficient than the cheaper laminated E-I types for a similar power level. Other advantages compared to E-I types, include smaller size (about half), lower weight (about half), less mechanical hum (making them superior in audio amplifiers), lower exterior magnetic field (about one tenth), low off-load losses (making them more efficient in standby circuits), single-bolt mounting, and greater choice of shapes. The main disadvantages are higher cost and limited power capacity (see Classification parameters below). Because of the lack of a residual gap in the magnetic path, toroidal transformers also tend to exhibit higher inrush current, compared to laminated E-I types.
Ferrite toroidal cores are used at higher frequencies, typically between a few tens of kilohertz to hundreds of megahertz, to reduce losses, physical size, and weight of inductive components. A drawback of toroidal transformer construction is the higher labor cost of winding. This is because it is necessary to pass the entire length of a coil winding through the core aperture each time a single turn is added to the coil. As a consequence, toroidal transformers rated more than a few kVA are uncommon. Small distribution transformers may achieve some of the benefits of a toroidal core by splitting it and forcing it open, then inserting a bobbin containing primary and secondary windings.
A physical core is not an absolute requisite and a functioning transformer can be produced simply by placing the windings near each other, an arrangement termed an 'air-core' transformer. The air which comprises the magnetic circuit is essentially lossless, and so an air-core transformer eliminates loss due to hysteresis in the core material. The leakage inductance is inevitably high, resulting in very poor regulation, and so such designs are unsuitable for use in power distribution. They have however very high bandwidth, and are frequently employed in radio-frequency applications, for which a satisfactory coupling coefficient is maintained by carefully overlapping the primary and secondary windings. They're also used for resonant transformers such as Tesla coils where they can achieve reasonably low loss in spite of the high leakage inductance.
||It has been suggested that Compensation winding be merged into this article. (Discuss) Proposed since March 2014.|
The conducting material used for the windings depends upon the application, but in all cases the individual turns must be electrically insulated from each other to ensure that the current travels throughout every turn. For small power and signal transformers, in which currents are low and the potential difference between adjacent turns is small, the coils are often wound from enamelled magnet wire, such as Formvar wire. Larger power transformers operating at high voltages may be wound with copper rectangular strip conductors insulated by oil-impregnated paper and blocks of pressboard.
High-frequency transformers operating in the tens to hundreds of kilohertz often have windings made of braided Litz wire to minimize the skin-effect and proximity effect losses. Large power transformers use multiple-stranded conductors as well, since even at low power frequencies non-uniform distribution of current would otherwise exist in high-current windings. Each strand is individually insulated, and the strands are arranged so that at certain points in the winding, or throughout the whole winding, each portion occupies different relative positions in the complete conductor. The transposition equalizes the current flowing in each strand of the conductor, and reduces eddy current losses in the winding itself. The stranded conductor is also more flexible than a solid conductor of similar size, aiding manufacture.
The windings of signal transformers minimize leakage inductance and stray capacitance to improve high-frequency response. Coils are split into sections, and those sections interleaved between the sections of the other winding.
Power-frequency transformers may have taps at intermediate points on the winding, usually on the higher voltage winding side, for voltage adjustment. Taps may be manually reconnected, or a manual or automatic switch may be provided for changing taps. Automatic on-load tap changers are used in electric power transmission or distribution, on equipment such as arc furnace transformers, or for automatic voltage regulators for sensitive loads. Audio-frequency transformers, used for the distribution of audio to public address loudspeakers, have taps to allow adjustment of impedance to each speaker. A center-tapped transformer is often used in the output stage of an audio power amplifier in a push-pull circuit. Modulation transformers in AM transmitters are very similar.
Dry-type transformer winding insulation systems can be either of standard open-wound 'dip-and-bake' construction or of higher quality designs that include vacuum pressure impregnation (VPI), vacuum pressure encapsulation (VPE), and cast coil encapsulation processes. In the VPI process, a combination of heat, vacuum and pressure is used to thoroughly seal, bind, and eliminate entrained air voids in the winding polyester resin insulation coat layer, thus increasing resistance to corona. VPE windings are similar to VPI windings but provide more protection against environmental effects, such as from water, dirt or corrosive ambients, by multiple dips including typically in terms of final epoxy coat.
To place the cooling problem in perspective, the accepted rule of thumb is that the life expectancy of insulation in all electric machines including all transformers is halved for about every 7 °C to 10 °C increase in operating temperature, this life expectancy halving rule holding more narrowly when the increase is between about 7 °C to 8 °C in the case of transformer winding cellulose insulation.
Small dry-type and liquid-immersed transformers are often self-cooled by natural convection and radiation heat dissipation. As power ratings increase, transformers are often cooled by forced-air cooling, forced-oil cooling, water-cooling, or combinations of these. Large transformers are filled with transformer oil that both cools and insulates the windings. Transformer oil is a highly refined mineral oil that cools the windings and insulation by circulating within the transformer tank. The mineral oil and paper insulation system has been extensively studied and used for more than 100 years. It is estimated that 50% of power transformers will survive 50 years of use, that the average age of failure of power transformers is about 10 to 15 years, and that about 30% of power transformer failures are due to insulation and overloading failures. Prolonged operation at elevated temperature degrades insulating properties of winding insulation and dielectric coolant, which not only shortens transformer life but can ultimately lead to catastrophic transformer failure. With a great body of empirical study as a guide, transformer oil testing including dissolved gas analysis provides valuable maintenance information. This underlines the need to monitor, model, forecast and manage oil and winding conductor insulation temperature conditions under varying, possibly difficult, power loading conditions.
Building regulations in many jurisdictions require indoor liquid-filled transformers to either use dielectric fluids that are less flammable than oil, or be installed in fire-resistant rooms. Air-cooled dry transformers can be more economical where they eliminate the cost of a fire-resistant transformer room.
The tank of liquid filled transformers often has radiators through which the liquid coolant circulates by natural convection or fins. Some large transformers employ electric fans for forced-air cooling, pumps for forced-liquid cooling, or have heat exchangers for water-cooling. An oil-immersed transformer may be equipped with a Buchholz relay, which, depending on severity of gas accumulation due to internal arcing, is used to either alarm or de-energize the transformer. Oil-immersed transformer installations usually include fire protection measures such as walls, oil containment, and fire-suppression sprinkler systems. Another protection means consists in fast depressurization systems which are activated by the first dynamic pressure peak of the shock wave, avoiding transformer explosion before static pressure increases. Many explosions are reported to have been avoided thanks to this technology.
Polychlorinated biphenyls have properties that once favored their use as a dielectric coolant, though concerns over their environmental persistence led to a widespread ban on their use. Today, non-toxic, stable silicone-based oils, or fluorinated hydrocarbons may be used where the expense of a fire-resistant liquid offsets additional building cost for a transformer vault. PCBs for new equipment was banned in 1981 and in 2000 for use in existing equipment in United Kingdom Legislation enacted in Canada between 1977 and 1985 essentially bans PCB use in transformers manufactured in or imported into the country after 1980, the maximum allowable level of PCB contamination in existing mineral oil transformers being 50 ppm.
Experimental power transformers in the 500-to-1,000 kVA range have been built with liquid nitrogen or helium cooled superconducting windings, which eliminates winding losses without affecting core losses.
Construction of oil-filled transformers requires that the insulation covering the windings be thoroughly dried of residual moisture before the oil is introduced. Drying is carried out at the factory, and may also be required as a field service. Drying may be done by circulating hot air around the core, or by vapor-phase drying (VPD) where an evaporated solvent transfers heat by condensation on the coil and core.
For small transformers, resistance heating by injection of current into the windings is used. The heating can be controlled very well, and it is energy efficient. The method is called low-frequency heating (LFH) since the current used is at a much lower frequency than that of the power grid, which is normally 50 or 60 Hz. A lower frequency reduces the effect of inductance, so the voltage required can be reduced. The LFH drying method is also used for service of older transformers.
Larger transformers are provided with high-voltage insulated bushings made of polymers or porcelain. A large bushing can be a complex structure since it must provide careful control of the electric field gradient without letting the transformer leak oil.
Transformers can be classified in many ways, such as the following:
- Power capacity: From a fraction of a volt-ampere (VA) to over a thousand MVA.
- Duty of a transformer: Continuous, short-time, intermittent, periodic, varying.
- Frequency range: Power-frequency, audio-frequency, or radio-frequency.
- Voltage class: From a few volts to hundreds of kilovolts.
- Cooling type: Dry and liquid-immersed - self-cooled, forced air-cooled; liquid-immersed - forced oil-cooled, water-cooled.
- Circuit application: Such as power supply, impedance matching, output voltage and current stabilizer or circuit isolation.
- Utilization: Pulse, power, distribution, rectifier, arc furnace, amplifier output, etc..
- Basic magnetic form: Core form, shell form.
- Constant-potential transformer descriptor: Step-up, step-down, isolation.
- General winding configuration: By EIC vector group - various possible two-winding combinations of the phase designations delta, wye or star, and zigzag or interconnected star;[i] other - autotransformer, Scott-T, zigzag grounding transformer winding.
- Rectifier phase-shift winding configuration: 2-winding, 6-pulse; 3-winding, 12-pulse; . . . n-winding, [n-1]*6-pulse; polygon; etc..
Various specific electrical application designs require a variety of transformer types. Although they all share the basic characteristic transformer principles, they are customize in construction or electrical properties for certain installation requirements or circuit conditions.
- Autotransformer: Transformer in which part of the winding is common to both primary and secondary circuits.
- Capacitor voltage transformer: Transformer in which capacitor divider is used to reduce high voltage before application to the primary winding.
- Distribution transformer, power transformer: International standards make a distinction in terms of distribution transformers being used to distribute energy from transmission lines and networks for local consumption and power transformers being used to transfer electric energy between the generator and distribution primary circuits.[j]
- Phase angle regulating transformer: A specialised transformer used to control the flow of real power on three-phase electricity transmission networks.
- Scott-T transformer: Transformer used for phase transformation from three-phase to two-phase and vice versa.
- Polyphase transformer: Any transformer with more than one phase.
- Grounding transformer: Transformer used for grounding three-phase circuits to create a neutral in a three wire system, using a wye-delta transformer, or more commonly, a zigzag grounding winding.
- Leakage transformer: Transformer that has loosely coupled windings.
- Resonant transformer: Transformer that uses resonance to generate a high secondary voltage.
- Audio transformer: Transformer used in audio equipment.
- Output transformer: Transformer used to match the output of a valve amplifier to its load.
- Instrument transformer: Potential or current transformer used to accurately and safely represent voltage, current or phase position of high voltage or high power circuits.
Transformers are used to increase voltage before transmitting electrical energy over long distances through wires. Wires have resistance which loses energy through joule heating at a rate corresponding to square of the current. By transforming power to a higher voltage transformers enable economical transmission of power and distribution. Consequently, transformers have shaped the electricity supply industry, permitting generation to be located remotely from points of demand. All but a tiny fraction of the world's electrical power has passed through a series of transformers by the time it reaches the consumer.
Transformers are also used extensively in electronic products to step-down the supply voltage to a level suitable for the low voltage circuits they contain. The transformer also electrically isolates the end user from contact with the supply voltage.
Signal and audio transformers are used to couple stages of amplifiers and to match devices such as microphones and record players to the input of amplifiers. Audio transformers allowed telephone circuits to carry on a two-way conversation over a single pair of wires. A balun transformer converts a signal that is referenced to ground to a signal that has balanced voltages to ground, such as between external cables and internal circuits.
Discovery of induction
Electromagnetic induction, the principle of the operation of the transformer, was discovered independently and almost simultaneously by Joseph Henry and Michael Faraday in 1831. Although Henry's work likely having preceded Faraday's work by a few months, Faraday was the first to publish the results of his experiments and thus receive credit for the discovery. The relationship between emf and magnetic flux is an equation now known as Faraday's law of induction:
Faraday performed the first experiments on induction between coils of wire, including winding a pair of coils around an iron ring, thus creating the first toroidal closed-core transformer. However he only applied individual pulses of current to his transformer, and never discovered the relation between the turns ratio and emf in the windings.
The first type of transformer to see wide use was the induction coil, invented by Rev. Nicholas Callan of Maynooth College, Ireland in 1836. He was one of the first researchers to realize the more turns the secondary winding has in relation to the primary winding, the larger the induced secondary emf will be. Induction coils evolved from scientists' and inventors' efforts to get higher voltages from batteries. Since batteries produce direct current (DC) rather than AC, induction coils relied upon vibrating electrical contacts that regularly interrupted the current in the primary to create the flux changes necessary for induction. Between the 1830s and the 1870s, efforts to build better induction coils, mostly by trial and error, slowly revealed the basic principles of transformers.
First alternating current transformers
In 1876, Russian engineer Pavel Yablochkov invented a lighting system based on a set of induction coils where the primary windings were connected to a source of AC. The secondary windings could be connected to several 'electric candles' (arc lamps) of his own design.  The coils Yablochkov employed functioned essentially as transformers.
In 1878, the Ganz factory, Budapest, Hungary, began manufacturing equipment for electric lighting and, by 1883, had installed over fifty systems in Austria-Hungary. Their AC systems used arc and incandescent lamps, generators, and other equipment.
Lucien Gaulard and John Dixon Gibbs first exhibited a device with an open iron core called a 'secondary generator' in London in 1882, then sold the idea to the Westinghouse company in the United States. They also exhibited the invention in Turin, Italy in 1884, where it was adopted for an electric lighting system. However, the efficiency of their open-core bipolar apparatus remained very low.
Early series circuit transformer distribution
Induction coils with open magnetic circuits are inefficient at transferring power to loads. Until about 1880, the paradigm for AC power transmission from a high voltage supply to a low voltage load was a series circuit. Open-core transformers with a ratio near 1:1 were connected with their primaries in series to allow use of a high voltage for transmission while presenting a low voltage to the lamps. The inherent flaw in this method was that turning off a single lamp (or other electric device) affected the voltage supplied to all others on the same circuit. Many adjustable transformer designs were introduced to compensate for this problematic characteristic of the series circuit, including those employing methods of adjusting the core or bypassing the magnetic flux around part of a coil. Efficient, practical transformer designs did not appear until the 1880s, but within a decade, the transformer would be instrumental in the War of Currents, and in seeing AC distribution systems triumph over their DC counterparts, a position in which they have remained dominant ever since.
Closed-core transformers and parallel power distribution
In the autumn of 1884, Károly Zipernowsky, Ottó Bláthy and Miksa Déri (ZBD), three engineers associated with the Ganz factory, had determined that open-core devices were impracticable, as they were incapable of reliably regulating voltage. In their joint 1885 patent applications for novel transformers (later called ZBD transformers), they described two designs with closed magnetic circuits where copper windings were either a) wound around iron wire ring core or b) surrounded by iron wire core. The two designs were the first application of the two basic transformer constructions in common use to this day, which can as a class all be termed as either core form or shell form (or alternatively, core type or shell type), as in a) or b), respectively (see images). The Ganz factory had also in the autumn of 1884 made delivery of the world's first five high-efficiency AC transformers, the first of these units having been shipped on September 16, 1884. This first unit had been manufactured to the following specifications: 1,400 W, 40 Hz, 120:72 V, 11.6:19.4 A, ratio 1.67:1, one-phase, shell form.
In both designs, the magnetic flux linking the primary and secondary windings traveled almost entirely within the confines of the iron core, with no intentional path through air (see Toroidal cores below). The new transformers were 3.4 times more efficient than the open-core bipolar devices of Gaulard and Gibbs. The ZBD patents included two other major interrelated innovations: one concerning the use of parallel connected, instead of series connected, utilization loads, the other concerning the ability to have high turns ratio transformers such that the supply network voltage could be much higher (initially 1,400 to 2,000 V) than the voltage of utilization loads (100 V initially preferred). When employed in parallel connected electric distribution systems, closed-core transformers finally made it technically and economically feasible to provide electric power for lighting in homes, businesses and public spaces. Bláthy had suggested the use of closed cores, Zipernowsky had suggested the use of parallel shunt connections, and Déri had performed the experiments;
Transformers today are designed on the principles discovered by the three engineers. They also popularized the word 'transformer' to describe a device for altering the emf of an electric current, although the term had already been in use by 1882. In 1886, the ZBD engineers designed, and the Ganz factory supplied electrical equipment for, the world's first power station that used AC generators to power a parallel connected common electrical network, the steam-powered Rome-Cerchi power plant.
Although George Westinghouse had bought Gaulard and Gibbs' patents in 1885, the Edison Electric Light Company held an option on the US rights for the ZBD transformers, requiring Westinghouse to pursue alternative designs on the same principles. He assigned to William Stanley the task of developing a device for commercial use in United States. Stanley's first patented design was for induction coils with single cores of soft iron and adjustable gaps to regulate the emf present in the secondary winding (see image). This design was first used commercially in the US in 1886 but Westinghouse was intent on improving the Stanley design to make it (unlike the ZBD type) easy and cheap to produce.
Westinghouse, Stanley and associates soon developed an easier to manufacture core, consisting of a stack of thin 'E‑shaped' iron plates, insulated by thin sheets of paper or other insulating material. Prewound copper coils could then be slid into place, and straight iron plates laid in to create a closed magnetic circuit. Westinghouse applied for a patent for the new low-cost design in December 1886; it was granted in July 1887.
Other early transformers
- Polyphase system
- Load profile
- Magnetic core
- Geomagnetic storm
- Switched-mode power supply
- Electronic symbol
- "The turn ratio of a transformer is the ratio of the number of turns in the high-voltage winding to that in the low-voltage winding", common usage having evolved over time from 'turn ratio' to 'turns ratio',
- A step-down transformer converts a high voltage to a lower voltage while a step-up transformer converts a low voltage to a higher voltage, an isolation transformer having 1:1 turns ratio with output voltage the same as input voltage.
- Transformer windings are usually wound around ferromagnetic cores but can also be air-core wound.
- The expression dΦ/dt, defined as the derivative of magnetic flux Φ with time t, provides a measure of rate of magnetic flux in the core and hence of emf induced in the respective winding.
- ANSI/IEEE C57.13, ANS Requirements for Instrument Transformers, defines polarity as the 'designation of the relative instantaneous directions of the currents entering the primary terminals and leaving the secondary terminals during most of each half cycle', the word 'instantaneous' differentiating from say phasor current.
- Transformer polarity can also be identified by terminal markings H0,H1,H2... on primary terminals and X1,X2, (and Y1,Y2, Z1,Z2,Z3... if windings are available) on secondary terminals. Each letter prefix designates a different winding and each numeral designates a termination or tap on each winding. The designated terminals H1,X1, (and Y1, Z1 if available) indicate same instantaneous polarities for each winding as in the dot convention.
- A standardized open-circuit or unloaded transformer test called the Epstein frame can also be used for the characterization of magnetic properties of soft magnetic materials including especially electrical steels.
- Transformer hum's fundamental noise frequency is two times that of the power frequency as there is an extension and a contraction of core laminations for every cycle of the AC wave and a transformer's audible hum noise level is dominated by the fundamental noise frequency and its first triplen harmonic, i.e., by the 100 & 300 Hz, or 120 & 360 Hz, frequencies.
- For example, the delta-wye transformer, by far the most common commercial three-phase transformer, is known as the Dyn11 vector group configuration, Dyn11 denoting D for delta primary winding, y for wye secondary winding, n for neutral of the wye winding, and 11 for relative phase position on the clock by which the secondary winding leads the primary winding, namely, 30° leading.
- While the above formal definition, derived from standards such as IEEE C57.12.80, applies to large transformers, it is not uncommon in colloquial, or even trade, parlance for small general-purpose transformers to be referred to as 'power' transformers, for distribution transformers to be referred to as 'power distribution' transformers, and so on.
- Knowlton, A.E. (Ed.) (1949). Standard Handbook for Electrical Engineers (8th ed.). McGraw-Hill. p. 597, Fig. 6–42.
- Mack, James E.; Shoemaker, Thomas (2006). "Chapter 15 - Distribution Transformers". The Lineman's and Cableman's Handbook (11th ed.). New York: McGraw-Hill. pp. 15–1 to 15–22. ISBN 0071467890.
- Thomas P. Hughes (1993). Networks of Power: Electrification in Western Society, 1880–1930. Baltimore: Johns Hopkins University Press. pp. 119–122. ISBN 0-8018-4614-5.
- Winders, John J., Jr. (2002). Power Transformer Principles and Applications. CRC. pp. 20–21.
- Hameyer, Kay (2001). "§3.2 'Definition of Transformer Ratio' in Section 3 - Transformers". Electrical Machines I: Basics, Design, Function, Operation. RWTH Aachen University Institute of Electrical Machines. p. 27.
- Knowlton, §6-13, p. 552
- Flanagan, William M. (1993). Handbook of Transformer Design & Applications (2nd ed.). McGraw-Hill. pp. 1–2. ISBN 0-07-021291-0.
- Tcheslavski, Gleb V. (2008). "Slide 13 Impedance Transformation in Lecture 4: Transformers". ELEN 3441 Fundamentals of Power Engineering. Lamar University (TSU system member).
- John Avison (1989). "The World of Physics". [Thomas Nelson and Sons Ltd]. pp. 300–320.
- Jim Breithaupt (2000). "New Understanding: Physics for Advanced Level (4th Edition)". [Stanley Thornes (Publishers) Ltd]. pp. 300–320.
- Heathcote, Martin (Nov 3, 1998). J & P Transformer Book (12th ed.). Newnes. pp. 2–3. ISBN 0-7506-1158-8.
- Calvert, James (2001). "Inside Transformers". University of Denver. Retrieved May 19, 2007.
- Parker, M. R; Ula, S.; Webb, W. E. (2005). "§2.5.5 'Transformers' & §10.1.3 'The Ideal Transformer'". In Whitaker, Jerry C. The Electronics Handbook (2nd ed.). Taylor & Francis. pp. 172, 1017. ISBN 0-8493-1889-0.
- Kothari, D.P.; Nagrath, I.J. (2010). §3.7 'Transformer Testing' in Chapter 3 - Transformers (4th ed.). Tata McGraw-Hill. p. 73. ISBN 978-0-07-069967-0.
- Brenner, Egon; Javid, Mansour (1959). "§18.1 'Symbols and Polarity of Mutual Inductance' in Chapter 18 - Circuits with Magnetic Circuits". Analysis of Electric Circuits. McGraw-Hill. pp. 589–590.
- "Polarity Markings on Instrument Transformers". Retrieved 13 April 2013.
- "Connections - Polarity". Retrieved 13 April 2013.
- Say, M. G. (1984). Alternating Current Machines (5th ed.). Halsted Press. ISBN 0-470-27451-4.
- McLaren, P. G. (1984). Elementary Electric Power and Machines. pp. 68–74. ISBN 0-13-257601-5.
- Edwards, J.; Saha, T. K. (2000). "Power Flow in Transformers Via the Poynting Vector". AUPEC 2000 Proceedings. Queensland University of Technology.
- Say, p. 485
- Terman, Frederick E. (1955). Electronic and Radio Engineering (4th ed.). New York: McGraw-Hill. p. 15.
- Knowlton, pp. 585-586
- Haymeyer, Kay (2001). "Electrical Machines I: Basics, Design, Function, Operation". RWTH Aachen University Institute of Electrical Machines. p. 39.
- Daniels, A. R. Introduction to Electrical Machines. pp. 47–49.
- Say, pp. 142-143
- IEC Std 60404-2 Magnetic Materials - Part 2: Methods of Measurement of the Magnetic Properties . . .
- Dixon, Lloyd (2001). "Power Transformer Design". Magnetics Design Handbook. Texas Instruments.
- Billings, Keith (1999). Switchmode Power Supply Handbook. McGraw-Hill. ISBN 0-07-006719-8.
- "400 Hz Electrical Systems". Aerospaceweb.org. Retrieved May 21, 2007.
- Gururaj, B.I. (June 1963). "Natural Frequencies of 3-Phase Transformer Windings". IEEE Transactions on Power Apparatus and Systems 82 (66): 318–329. doi:10.1109/TPAS.1963.291359.
- Kubo, T.; Sachs, H.; Nadel, S. (2001). Opportunities for New Appliance and Equipment Efficiency Standards. American Council for an Energy-Efficient Economy. p. 39. Retrieved June 21, 2009.
- Riemersma, H.; Eckels, P.; Barton, M.; Murphy, J.; Litz, D.; Roach, J. (1981). "Application of Superconducting Technology to Power Transformers". IEEE Transactions on Power Apparatus and Systems. PAS-100 (7): 3398. doi:10.1109/TPAS.1981.316682.
- Heathcote, pp. 41-42
- Knowlton, pp. 49 (§2.67) & 323 (§4.279)
- EE-Reviewonline.com. "Steinmetz's Formula for Magnetic Hysteresis". Retrieved 7 February 2013.
- "Understanding Transformer Noise". FP. Retrieved 30 January 2013.
- Nailen, Richard (May 2005). "Why We Must Be Concerned With Transformers". Electrical Apparatus.
- Pansini, Anthony J. (1999). Electrical Transformers and Power Equipment. Fairmont Press. p. 23. ISBN 0-88173-311-3.
- Del Vecchio, Robert M. et al. (2002). Transformer Design Principles: With Applications to Core-Form Power Transformers. Boca Raton: CRC Press. pp. 10–11, Fig. 1.8. ISBN 90-5699-703-3.
- Knowlton, p. 562
- Hydroelectric Research and Technical Services Group. "Transformers: Basics, Maintenance, and Diagnostics". U.S. Dept. of the Interior, Bureau of Reclamation. p. 12. Retrieved Mar 27, 2012.
- EM 1110-2-3006 (1994). "Chapter 4 - Power Transformers". Engineering and Design - Hydroelectric Power Plants Electrical Design. U.S. Army Corps of Engineers. p. 4-1.
- Hindmarsh, J. (1984). Electrical Machines and Their Applications. Oxford: Pergamon Press. pp. 29–31. ISBN 0-08-030573-3.
- Gottlieb, Irving (1998). Practical Transformer Handbook. Newnes. p. 4. ISBN 0-7506-3992-X.
- Allan, D.J. (Jan. 1991). "Power Transformers – The Second Century". Power Engineering Journal 5 (1): 5–14. doi:10.1049/pe:19910004.
- Kulkarni, S. V.; Khaparde, S. A. (May 24, 2004). Transformer Engineering: Design and Practice. CRC. pp. 36–37. ISBN 0-8247-5653-3.
- Hindmarsh, pp. 29-31
- McLyman, Colonel Wm. T. (2004). Transformer and Inductor Design Handbook. CRC. Chap. 3, pp. 9–14. ISBN 0-8247-5393-3.
- Sim, H. Jim; Digby; Scott H. (2004). "§2.1 Power Transformers in Chap. 2 - Equipment Types". In James H. Harlow (ed.); L. L. Grigsby (Series ed.). The Electric Power Engineering Handbook (Online ed.). CRC Press. p. §2.1.7 & §220.127.116.11.1. ISBN 0-8493-8578-4.
- Boteler, D. H.; Pirjola, R. J.; Nevanlinna, H. (1998). "The Effects of Geomagnetic Disturbances On Electrical Systems at the Earth's Surface". Advances in Space Research 22: 17–27. doi:10.1016/S0273-1177(97)01096-X.
- Hasegawa, Ryusuke (June 2, 2000). "Present Status of Amorphous Soft Magnetic Alloys". Journal of Magnetism and Magnetic Materials. 215-216: 240–245. doi:10.1016/S0304-8853(00)00126-8.
- McLyman, Chap. 3 p. 1
- Lee, Reuben. "Air-Core Transformers". Electronic Transformers and Circuits. Retrieved May 22, 2007.
- Dixon, L.H., Jr. (1997). Eddy Current Losses in Transformer Windings. Texas Instrument. pp. R2–1–to–R2–10.
- Central Electricity Generating Board (1982). Modern Power Station Practice. Pergamon Press.
- Lane, Keith (2007). "The Basics of Large Dry-Type Transformers". EC&M. Retrieved 29 January 2013.
- Heathcote, pp. 720–723
- Tillman, Robert F. (2004). "§3.4 Load and Thermal Performance in Chap. 3 - Ancillary Topics". In James H. Harlow (ed.); L. L. Grigsby (Series ed.). The Electric Power Engineering Handbook (Online ed.). CRC Press. p. §3.4.8. ISBN 0-8493-8578-4.
- Walling, Reigh; Shattuck; G. Bruce (May 2007). "Distribution Transformer Thermal Behaviour and Aging in Local-Delivery Distribution Systems". 19th International Conference on Electricity Distribution. Paper 0720. Retrieved 11 February 2013.
- Kimberly, E.E. "Permissible Temperatures for Insulation". Retrieved 12 February 2013.
- Pansini, p. 32
- Willis, H. Lee (2004). Power Distribution Planning Reference Book. CRC Press. p. 403. ISBN 0-8247-4875-1.
- Hartley, William H. (2003). "Analysis of Transformer Failures". 36th Annual Conference of the International Association of Engineering Insurers. p. 7 (fig. 6). Retrieved 30 January 2013.
- Hartley, William H. (~2011). "An Analysis of Transformer Failures, Part 1 – 1988 through 1997". The Locomotive. Retrieved 30 January 2013.
- Prevost, Thomas A. et al. (Nov 2006). "Estimation of Insulation Life Based on a Dual Temperature Aging Model". Weidmann. p. 1. Retrieved Mar 30, 2012.
- Sen, P.K. et al. (2011). "PSERC Pub. 11-02 Transformer Overloading and Assessment of Loss-of-Life for Liquid-Filled Transformers". Power Systems Engineering Research Center, Arizona State University. Retrieved 11 January 2013.
- De Keulenaer, H. et al (2001). The Scope for Energy Saving in the EU Through the Use of Energy-Efficient Electricity Distribution Transformers. Institution of Engineering and Technology.
- "ASTDR ToxFAQs for Polychlorinated Biphenyls". 2001. Retrieved June 10, 2007.
- Kulkarni, pp. 2-3
- AFBI (2011). "9. Contaminants". State of the Seas Report. Agri-Food and Biosciences Institute & Northern Ireland Environment Agency. p. 71. ISBN 9977 and 178-1-907053-20-7 Check
- McDonald, C. J.; Tourangeau, R. E. (1986). PCBs, Question and Answer Guide Concerning Polychlorinated Biphenyls. Government of Canada: Environment Canada Department. ISBN 0-662-14595-X. Retrieved Nov 7, 2007.
- Mehta, S.P.; Aversa, N.; Walker, M.S. (Jul 1997). "Transforming Transformers [Superconducting windings]". IEEE Spectrum 34 (7): 43–49. doi:10.1109/6.609815. Retrieved 14 November 2012.
- Pansini, pp. 66–67
- Fink, Donald G.; Beatty, H. Wayne (Eds.) (1978). Standard Handbook for Electrical Engineers (11th ed.). McGraw Hill. pp. 10–38 through 10–40. ISBN 0-07-02974-x Check
- Figueroa, Elisa et al (Jan/Feb 2009). "Low Frequency Heating Field Dry-Out of a 750 MVA 500 kV Auto Transformer". Electricity Today. Retrieved Feb 28, 2012.
- Ryan, Hugh M. (2001). High Voltage Engineering and Testing. Institution Electrical Engineers. pp. 416–417. ISBN 0-85296-775-6.
- Lawhead, Larry; Hamilton, Randy; Horak, John (2006). "Three Phase Transformer Winding Configurations and Differential Relay Compensation". Georgia Tech 60th Protective Relay Conference. pp. 8–10. Retrieved Feb 23, 2012.
- Beeman, Donald (Ed.) (1955). Industrial Power Systems Handbook. McGraw-Hill. pp. 349–364.
- Brown, BIll. "Section 6 Grounding Systems". Schneider. pp. 9–12. Retrieved 18 January 2013.
- Beltz, Robert; Peacock, Ian; Vilcheck, William (2000). "Application Considerations for High Resistance Ground Retrofits in Pulp and Paper Mills". Pulp and Paper Industry Technical Conference. pp. 33–40. doi:10.1109/PAPCON.2000.854186.
- Knowlton, §6-7, pp. 549-550
- IEEE PES TC (Fall 2011). "Discussion of Class I & II Terminology". IEEE PES Transformer Committee. p. slide 6. Retrieved 27 January 2013.
- Knowlton, §12-341, fig. 12-95, p. 1085
- AEMO et al. (2012). "Joint Consultation Paper - Western Metropolitan Melbourne Transmission Connection and Subtransmission Capacity". p. 11. Retrieved and archived 4 January 2013.
- Heathcote, p. 1
- Poyser, Arthur William (1892). Magnetism and Electricity: A Manual for Students in Advanced Classes. London and New York: Longmans, Green, & Co. p. 285, fig. 248. Retrieved Aug 6, 2009.
- "Joseph Henry". Distinguished Members Gallery, National Academy of Sciences. Retrieved Nov 30, 2006.
- Chow, Tai L. (2006). Introduction to Electromagnetic Theory: A Modern Perspective. Sudbury, Mass.: Jones and Bartlett Publishers. p. 171. ISBN 0-7637-3827-1.
- Faraday, Michael (1834). "Experimental Researches on Electricity, 7th Series". Philosophical Transactions of the Royal Society 124: 77–122. doi:10.1098/rstl.1834.0008.
- "Stanley Transformer". Los Alamos National Laboratory; University of Florida. Retrieved Jan 9, 2009.
- De Fonveille, W. (Jan 22, 1880). "Gas and Electricity in Paris". Nature 21 (534): 283. Bibcode:1880Natur..21..282D. doi:10.1038/021282b0. Retrieved Jan 9, 2009.
- Hughes, Thomas P. (1993). Networks of Power: Electrification in Western Society, 1880-1930. Baltimore: The Johns Hopkins University Press. p. 96. ISBN 0-8018-2873-2. Retrieved Sep 9, 2009.
- Uppenborn, F. J. (1889). History of the Transformer. London: E. & F. N. Spon. pp. 35–41.
- Coltman, J. W. (Jan. 1988). "The Transformer". Scientific American. pp. 86–95. OSTI 6851152.
- Stanley, William, Jr.. "Induction Coil". U.S. Patent 349 311, issued Sept. 21, 1886. Retrieved July 13, 2009.
- Hughes, p. 95
- Károly, Simonyi. "The Faraday Law With a Magnetic Ohm's Law". Természet Világa. Retrieved Mar 1, 2012.
- Lucas, J.R. "Historical Development of the Transformer". IEE Sri Lanka Centre. Retrieved Mar 1, 2012.
- Halacsy, A. A.; Von Fuchs, G. H. (April 1961). "Transformer Invented 75 Years Ago". IEEE Transactions of the American Institute of Electrical Engineers 80 (3): 121–125. doi:10.1109/AIEEPAS.1961.4500994. Retrieved Feb 29, 2012.
- Jeszenszky, Sándor. "Electrostatics and Electrodynamics at Pest University in the Mid-19th Century". University of Pavia. Retrieved Mar 3, 2012.
- "Hungarian Inventors and Their Inventions". Institute for Developing Alternative Energy in Latin America. Retrieved Mar 3, 2012.
- "Bláthy, Ottó Titusz". Budapest University of Technology and Economics, National Technical Information Centre and Library. Retrieved Feb 29, 2012.
- "Bláthy, Ottó Titusz (1860–1939)". Hungarian Patent Office. Retrieved Jan 29, 2004.
- Zipernowsky, K.; Déri, M.; Bláthy, O.T. "Induction Coil". U.S. Patent 352 105, issued Nov. 2, 1886. Retrieved July 8, 2009.
- Smil, Vaclav (2005). Creating the Twentieth Century: Technical Innovations of 1867—1914 and Their Lasting Impact. Oxford: Oxford University Press. p. 71. ISBN 9780198037743.
- Nagy, Árpád Zoltán (Oct. 11, 1996). "Lecture to Mark the 100th Anniversary of the Discovery of the Electron in 1897 (preliminary text)". Budapest. Retrieved July 9, 2009.
- Oxford English Dictionary (2nd ed.). Oxford University Press. 1989.
- Hospitalier, Édouard; as translated by Julius Maier (1882). The Modern Applications of Electricity. New York: D. Appleton & Co. p. 103.
- "Ottó Bláthy, Miksa Déri, Károly Zipernowsky". IEC Techline. Retrieved Apr 16, 2010.
- Skrabec, Quentin R. (2007). George Westinghouse: Gentle Genius. Algora Publishing. p. 102. ISBN 978-0-87586-508-9.
- Coltman, J.W.; (Jan–Feb 2002). "The Transformer [Historical Overview]". Industry Applications Magazine, IEEE 8 (1): 8–15. doi:10.1109/2943.974352. Retrieved Feb 29, 2012.
- Westinghouse, George, Jr.. "Electrical Converter". U.S. Patent 366 362, issued July 12, 1887.
- Neidhöfer, Gerhard; in collaboration with VDE "History of Electrical Engineering" Committee (2008). Michael von Dolivo-Dobrowolsky and Three-Phase: The Beginnings of Modern Drive Technology and Power Supply (in German) (2 ed.). Berlin: VDE-Verl. ISBN 978-3-8007-3115-2.
- Uth, Robert (Dec 12, 2000). "Tesla Coil". Tesla: Master of Lightning. PBS.org. Retrieved May 20, 2008.
- Tesla, Nikola. "System of Electrical Lighting". U.S. Patent 454 622, issued June 23, 1891.
- Central Electricity Generating Board (1982). Modern Power Station Practice. Pergamon. ISBN 0-08-016436-6.
- Daniels, A.R. (1985). Introduction to Electrical Machines. Macmillan. ISBN 0-333-19627-9.
- Flanagan, William M. (1993). Handbook of Transformer Design & Applications (2nd ed.). McGraw-Hill. ISBN 0-07-021291-0.
- Gottlieb, Irving (1998). Practical Transformer Handbook: for Electronics, Radio and Communications Engineers. Elsevier. ISBN 0-7506-3992-X.
- Hammond, John Winthrop (1941). Men and Volts: The Story of General Electric. J.B. Lippincott Company. pp. see esp. 106–107, 178, 238.
- Harlow, James (2004). Electric Power Transformer Engineering. CRC Press. ISBN 0-8493-1704-5.
- Heathcote, Martin (1998). J & P Transformer Book (12th ed.). Newnes. ISBN 0-7506-1158-8.
- Hindmarsh, John (1977). Electrical Machines and Their Applications (4th ed.). Exeter: Pergammon. ISBN 0-08-030573-3.
- Kulkarni, S.V.; Khaparde, S.A. (2004). Transformer Engineering: Design and Practice. CRC Press. ISBN 0-8247-5653-3.
- McLaren, Peter (1984). Elementary Electric Power and Machines. Ellis Horwood. ISBN 0-470-20057-X.
- McLyman, Colonel William (2004). Transformer and Inductor Design Handbook. CRC. ISBN 0-8247-5393-3.
- Pansini, Anthony (1999). Electrical Transformers and Power Equipment. CRC Press. ISBN 0-88173-311-3.
- Ryan, H.M. (2004). High Voltage Engineering and Testing. CRC Press. ISBN 0-85296-775-6.
- Say, M.G. (1983). Alternating Current Machines (5th ed.). London: Pitman. ISBN 0-273-01969-4.
- Winders, Jr., John J. (2002). Power Transformer Principles and Applications. CRC. ISBN 0-8247-0766-4.
|Wikimedia Commons has media related to Transformers.|
|The Wikibook School Science has a page on the topic of: How to make a transformer|
- Inside Transformers, composed by J. B. Calvert, from Denver University
- Substation and Transmission at DMOZ
- Introduction to Current Transformers
- Transformer (Interactive Java applet), 'Physics is fun' by Chui-king Ng
- HD video tutorial on transformers
- Three-phase transformer circuits from All About Circuits
- Bibliography of Transformer Books by P.M. Balma, from IEEE Transformer Committee
- Einschalten des Transformators. German Wikipedia article about transformer inrush current at switch on (in German).