Eraring Power Station
|This article needs additional citations for verification. (October 2011) (Learn how and when to remove this template message)|
|Eraring Power Station|
Eraring Power Station
|Location||near Dora Creek, Lake Macquarie, New South Wales|
|Thermal power station|
|Primary fuel||Bituminous coal|
|Nameplate capacity||2,880 MW|
Eraring Power Station is a coal fired electricity power station with four 720 MW Toshiba steam driven turbo-alternators for a combined capacity of 2,880 MW. The station is located near the township of Dora Creek, on the western shore of Lake Macquarie, New South Wales, Australia and is owned and operated by Origin Energy. It is Australia's largest power station.
History and facilities
Construction of the power station began in 1977. The first turbo-alternator was brought online in 1982, with the second and third in 1983, and the fourth in 1984. The generating capacity of each of the four turbines was upgraded from 660 MW to 720 MW between 2011 and 2012. The process of upgrading the control room to a fully digital system was completed in 2005.
Salt water from Lake Macquarie is used for cooling and is supplied through a concrete tunnel which passes under Dora Creek and up to the station via open canal. Reclaimed sewage water from the Dora Creek Waste Water Treatment Works is heavily purified and used to generate steam for the turbines as opposed to using municipal potable water supplies. The salt water helps in the cooling of the superheated steam as well as moderation of the temperature of outlet water to minimise thermal pollution.
The coal comes from five mines in the local area, delivered by conveyor, rail and private road. There is significant coal storage capacity on site. Eraring power station employs the Fabric Filter system of dust collection, in which particulate emissions resulting from coal combustion are captured as opposed to being released into the atmosphere. Some of this material is stored in an area nearby while some is taken and used as a component of road base.
Electricity generated at the station is transmitted through high voltage transmission lines. Turbines 1 and 2 are connected to a 330kV transmission line while turbines 3 and 4 are connected to a 500kV transmission line.
At 2.16 am Friday 28 October 2011 unit 2B generator transformer exploded with the transformer oil catching fire. The oil fire burnt for approximately two days and the estimated repair cost is A$20 million. . NSW Fire & Rescue, assisted by the NSW Rural Fire Service controlled the initial incident with subsequent investigations by NSW Police, the Office of Environment & Heritage, and Workcover NSW.
- "Preliminary Project Application" (PDF). Environmental Assessment Scoping Report - Eraring Energy: Eraring Power Station 750 MW Upgrade. Planning NSW. 22 August 2006. Retrieved 25 January 2012.
- Keene, Neil; Clennell, Andrew (28 October 2011). "Fears oil could seep into lake after explosion at Eraring power station in southern Lake Macquarie". The Daily Telegraph. Australia. Retrieved 28 October 2011.
- Cronshaw, Damon (1 November 2011). "Eraring dismisses explosion speculation". Newcastle Herald. Retrieved 25 January 2012.